InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Air conditioner or heat pump compressor motor replacement outline:
This air conditioning repair article describes the basic steps involved in replacing
a burned out air conditioner compressor. Replacing an air conditioner compressor is a job for a trained service technician. Not only is the compressor motor often the most costly
part in the system, but it is not a simple "bolt-in" replacement.
Identify the compressor model and capacity so that a proper replacement can be obtained
Shut down the air conditioning system, including turning off electrical power
Remove all refrigerant from the system. Modern procedures require that the refrigerant be captured rather than released to the
environment in order to reduce environmental pollutants
If the air conditioner system used a now-obsolete refrigerant such as R11 or R22, a the new compressor will be one designed
to use a new, approved refrigerant and other changes may be needed to the system to accommodate this change, such as changes in
thermal-expansion valves, coils, or other components. Not all components need replacement, however; ducts and blower assemblies,
for example, are retained.
The new compressor is installed in place in the compressor/condenser unit (usually all of this equipment is located
outside), and its refrigerant lines are connected (usually silver soldering) to the existing refrigerant lines.
or other controls may need to be cut out and replaced if the refrigerant is being changed too.
A compressor motor burn-out filter is installed, possibly two of them on both the low and high side refrigerant lines at the compressor/condenser unit. This special HVAC compressor burnout dryer / filter may be installed on the refrigerant line(s) to provide extra debris and moisture and oil filtering capacity to protect the new equipment from debris clogging.
Capillary tubes and TEVs as well as coils and compressors are vulnerable to damage or clogging from debris, stray oil, or water in the refrigerant piping system.
See REFRIGERANT DRIERS & FILTERS
A vacuum is pulled on the entire system both to evacuate all air from the refrigerant lines and compressor and to check
for leaks in the system. Air contamination, if allowed to mix with the new refrigerant would change its operating characteristics and
would prevent proper operation.
Any water or moisture in the system is also removed and as we noted above, during re-connection of the refrigerant piping the technician may install a compressor burn-out filter-drier in the system to remove any trace moisture that remains behind after reassembly.
Refrigerant is added to the system at the proper charge amount. Residential air conditioner systems, unlike commercial units,
use a hermetically sealed compressor motor and there is no separate receiver to hold a large refrigerant charge, so the charge
must be measured precisely (including temperature, pressure, and volume during charging) for the system to work properly. Both
overcharging and under-charging refrigerants will lead to improper system operation.
The air conditioning system, with its new compressor installed, will be re-started and checked for proper operation
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Voltas Plus 1.5 Ton window ADC not working
(July 5, 2014) karan said:
i have the voltas plus 1.5 ton window ac the unit turns on and the fan works but I can't get the compressor to kick on. I have tired turning the power on and off. Unplugging the unit. Changing modes from "cool" to "fan" and back to "cool". Any suggestion..?
for diagnostics to address an air conditioner that won't start, please see
I suspect a bad control or a seized compressor motor
Question: replacement compressor motor now won't work
(Oct 10, 2014) RJ said:
Compressor on a spilit system air conditioning unit was replaced about a year ago, now the newer compressor wont operate. Checked the freon and blacken in color, what is the correct way to clean the system before installation of another compressor?
The system is emptied of refrigerant, a vacuum pulled for at least 24 hours, and a special burnout filter drier is installed along with the new compressor motor.
Ask a Question or Search InspectApedia
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
"Air Conditioning & Refrigeration I & II", BOCES Education, Warren Hilliard (instructor), Poughkeepsie, New York, May - July 1982, [classroom notes from air conditioning and refrigeration maintenance and repair course attended by the website author]
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: email@example.com. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones