Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SEPTIC CARE INSTRUCTIONS
SEPTIC D-BOX INSTALL REPAIR
SEPTIC DRAINFIELD FAILURE DIAGNOSIS
SEPTIC DYE TEST PROCEDURE
SEPTIC FAILURE SIGNS
SEPTIC INSPECTION & TEST GUIDE
SEPTIC LIFE EXPECTANCY
SEPTIC SUPPLIES & PARTS
SEPTIC SYSTEM DESIGN ALTERNATIVES
SEPTIC SYSTEM DESIGN BASICS
SEPTIC SYSTEMS, HOME BUYERS GUIDE to
SEPTIC SYSTEM SAFETY WARNINGS
SEPTIC TREATMENTS & CHEMICALS
SEWAGE BACKUP PREVENTION
SEWAGE EJECTOR / GRINDER PUMPS
SEWER GAS ODORS
SEWER LINE REPLACEMENT
SINKHOLES, WARNING SIGNS
SOAKAWAY BED FAILURE DIAGNOSIS
SULPHUR & SEWER GAS SMELL SOURCES
TOILETS, INSPECT, INSTALL, REPAIR
TRAPS on PLUMBING FIXTURES
TREATMENTS & CHEMICALS, SEPTIC
VIDEO GUIDES: Septic Videos
WATER CONSERVATION MEASURES
WATER SOFTENERS & CONDITIONERS
WATER SUPPLY & DRAIN PIPING
WATER, WELLS, WATER TANKS: TESTING GUIDE
WASHING MACHINES & SEPTIC SYSTEMS
WASTEWATER TREATMENT BASICS
WINTERIZE A BUILDING
Septic dye handling: how to place septic dye into the plumbing system - avoiding spills, stains, and dye powder messes. How to clean up a dye mess; how to stop a toilet overflow.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
Septic System Loading and Dye Tests often requested by certain lenders, involve flushing a special dye down a toilet or other drain combined with a known quantity of water sufficient to put a working load on the absorption system.
If waste water leaks to the ground surface (an unsanitary condition indicating serious septic failure) one may find dye in that water provided the septic system is flowing at common rates.
Tips for Avoiding an Indoor Septic Dye Test Catastrophe
Watch out: Overflowing green or red septic dye into a building can create a horrible mess that is difficult to clean up. Above we already warned to be sure that the toilet flushes without overflowing before placing any septic dye into the fixture.
The mess you see on the outside of the Pylam Fluorescent Green septic dye container (left) is evidence of how difficult it is to handle septic dye powder without making a mess.
But because of inadequacies of using the neater dye tablets, many inspectors still prefer to use septic dye powder.
Be careful placing septic dye powder into the toilet - do it gently and with nearby windows closed and fans off.
Septic dye powder is so very fine that it is easy to accidentally get septic dye powder dust on other building surfaces.
If you do find that septic dye powder has spilled onto the toilet rim it is usually easy to wipe it off with a wad of damp toilet tissue.
If you find that dye powder has spilled onto a non-glazed tile floor you might need a dilute bleach solution to complete the cleanup. If you spilled septic dye onto a towel or drywall, good luck!
Wrapping Septic Dye into Packets to Avoid a Mess
Home inspector Arlene Puentes, agreeing that septic dye tablets can be ineffective (or you need too many) for a septic loading and dye test, uses septic dye powder. But to avoid spilling powder in the building, Puentes pre-wraps each dose of septic dye powder in a water soluble packet.
To wrap septic dye powder Puentes recommends Super Solvy™, a water soluble stabilizer used in sewing. SuperSolvy™ is a water-soluble synthetic plastic-like material used in quilting and embroidery or for other sewing applications to stiffen the fabric. It will dissolve in water. The manufacturer assures that the product is non toxic, and will dissolve in cool water in five to ten minutes.
As our photographs show, we tested Super Solvy™ in the InspectAPedia.com forensic laboratory, confirming that in less than 60 seconds the plastic-like material had dissolved, leaving an opaque goop in our 8 ounces of tap water. - Thanks to Arlene Puentes for providing our test sample.
Watch the Toilet for Overflow during A dye Test
Watch out: We flush the toilet once BEFORE starting any septic loading & dye test, to be sure that the toilet where we are putting our dye is one that is not going to overflow.
But just in case you need to know how to immediately STOP a toilet bowl fill-up that is about to overflow, see TOILET OVERFLOW EMERGENCY.
Inspect Indoors After Starting the Septic Dye Test
Watch out: remember to inspect indoors at the plumbing fixture where septic dye was flushed, at the plumbing fixture where septic dye test water is being run (to assure no backup, overflow, or indoor flood), and also in rooms below that plumbing fixture, all the way to the building basement or crawl space.
If you fail to make an indoor inspection while running the septic loading and dye test you risk overflowing from a plumbing fixture or from a leaky drain pipe that damages the building.
The presence of septic dye in the test water may even make it easier to spot an indoor plumbing drain pipe leak, as our photo (left) demonstrated.
If you don't understand what a colorful mess an indoor septic dye test can make, take a look at this red septic dye puddle found outdoors during one of our septic tests and this green septic dye puddle found outdoors, courtesy of Carson Dunlop Associates.
At INSIDE SEPTIC TEST STEPS we continue with details of exactly how to conduct a septic dye test.
These pages are part of our SEPTIC DYE TEST PROCEDURE for testing septic system function. Technical review by industry experts has been performed and is ongoing - reviewers are listed at REFERENCES. Comments and suggestions for content are welcome.
Continue reading at WATCH FOR INSIDE or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about handling septic dye: overflows, leaks, and cleanup
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References