Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SEPTIC CARE INSTRUCTIONS
SEPTIC D-BOX INSTALL REPAIR
SEPTIC DRAINFIELD FAILURE DIAGNOSIS
SEPTIC DYE TEST PROCEDURE
SEPTIC FAILURE SIGNS
SEPTIC INSPECTION & TEST GUIDE
SEPTIC LIFE EXPECTANCY
SEPTIC SUPPLIES & PARTS
SEPTIC SYSTEM DESIGN ALTERNATIVES
SEPTIC SYSTEM DESIGN BASICS
SEPTIC SYSTEMS, HOME BUYERS GUIDE to
SEPTIC SYSTEM SAFETY WARNINGS
SEPTIC TREATMENTS & CHEMICALS
SEWAGE BACKUP PREVENTION
SEWAGE EJECTOR / GRINDER PUMPS
SEWER GAS ODORS
SEWER LINE REPLACEMENT
SINKHOLES, WARNING SIGNS
SOAKAWAY BED FAILURE DIAGNOSIS
SULPHUR & SEWER GAS SMELL SOURCES
TOILETS, INSPECT, INSTALL, REPAIR
TRAPS on PLUMBING FIXTURES
TREATMENTS & CHEMICALS, SEPTIC
VIDEO GUIDES: Septic Videos
WATER CONSERVATION MEASURES
WATER SOFTENERS & CONDITIONERS
WATER SUPPLY & DRAIN PIPING
WATER, WELLS, WATER TANKS: TESTING GUIDE
WASHING MACHINES & SEPTIC SYSTEMS
WASTEWATER TREATMENT BASICS
WINTERIZE A BUILDING
Aerobic Treatment Unit Septic Tank Sizes: Here we provide the size and design requirements for aerobic septic tanks or ATUs. Here are designs and products for aerobic septic treatment units (ATUs, or in the UK, Australia, New Zealand, Aerobic Wastewater Treatment Units or AWTs) for onsite waste disposal, also called fine bubble aeration systems. We address aerobic septic system design, features, inspection, repair, and maintenance.
Aerobic septic system product sources are also listed. Qualified aerobic septic tank designers, producers, or service providers may be listed at this website at no fee. The page top illustration of a four-chamber aerobic wastewater treatment unit is adapted from the New Zealand Taranaki Regional Council's sewerage system guide.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
ATU size or capacity is determined as for a conventional septic system, by allowing 50 to 100 gallons of wastewater per day per building occupant.
Some jurisdictions require that the system minimum capacity accept 500 gallons of wastewater daily.
Safe aerobic treatment tank size advice
A "safe" design size for an aerobic treatment tank that allows for temporary power outage (and thus loss of the aeration pump) is an aerobic treatment tank at least as large as the conventional tank that would have been required for a given site.
Aerobic treatment tanks in cold climates
If your ATU tank is being installed in a cold climate, it may be necessary to insulate the treatment tank (use 2" solid foam panels) to keep the tank temperature high enough (above 54 degF) for the aerobic processing to continue in cold weather. (Some thermophilic microorganisms require temperatures as high as 131 to 149 degF.)
Intermittent flow aerobic septic systems
Just as most residential septic systems do not receive wastewater continuously but rather intermittently, the ATU may be designed to turn the aerator and agitator on and off as needed. Intermittent flow septic systems, including aerobic or aeration treatment designs are also called a "batch system" septic design approach.
Continuous flow aerobic treatment system designs
Other aerobic or aeration septic treatment systems, particularly aerobic systems which have to serve a larger facility where wastewater inflow may be continuous, may themselves operate continuously. Obviously these designs are called "continuous flow" aerobic treatment systems.
Continue reading at AEROBIC SEPTIC DISINFECTANTS - Calcium Hypochlorite or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about septic effluent disinfection systems - chemicals to use and others to avoid using
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References