Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AIR HANDLER / BLOWER UNITS
AIRBOUND HEAT SYSTEM REPAIR by WATER FEED VALVE
BACKDRAFTING HEATING EQUIPMENT
BACKUP HEAT for HEAT PUMPS
BLOWER FAN OPERATION & TESTING
BOOKSTORE - InspectAPedia
CIRCULATOR PUMPS & RELAYS
CONVECTOR HEATERS - HYDRONIC COILS
COOL OFF HEAT, Thermostat Switch
DEFINITION of Heating & Cooling Terms
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DUCT SYSTEM & DUCT DEFECTS
ELECTRIC HEAT, DIAGNOSIS, REPAIR
ELECTRIC MOTOR OVERLOAD RESET SWITCH
ELECTRICAL POWER SWITCH FOR HEAT
FAN, AIR HANDLER BLOWER UNIT
FAN AUTO ON Thermostat Switch
FAN, COMPRESSOR/CONDENSER UNIT
FAN CONVECTOR HEATERS - HYDRONIC COILS
FAN LIMIT SWITCH
FLOODED HEATING EQUIPMENT REPAIR
HEATING LOSS DIAGNOSIS-BOILERS
HEATING LOSS DIAGNOSIS-FURNACES
HEATING SYSTEM INSPECT DIAGNOSE REPAIR
LOW VOLTAGE BUILDING WIRING
LOW VOLTAGE TRANSFORMER TEST
MANUALS & PARTS GUIDES - HVAC
NO HEAT - BOILER
NO HEAT - FURNACE
ODORS FROM HEATING SYSTEMS
OIL FILTERS on HEATING EQUIPMENT
PULSE COMBUSTION HEATERS
Reset Switch - Heater Primary Control
Reset Switch Broken - Quick Repair
RESET SWITCH - ELECTRIC MOTOR
Reset Switch - Stack Relays
STEAM HEATING SYSTEMS
THERMOSTATS, HEATING / COOLING
THERMOSTATS, WATER HEATER
THERMOSTATIC EXPANSION VALVES
Thermostat heat anticipator testing & fine tuning procedure: this article explains how and why we fine-tune a room thermostat or wall thermostat by checking its heat anticipator using a mini ammeter. We describe the use of the T.D. Amps-Check mini ammeter specifically designed for thermostat heat anticipator adjustment. This mini ammeter gives precise amps readings in the 0 - 1.2A AC range. By measuring the current (amperes) flowing through the thermostat contacts on a call for heat we can adjust the heat anticipator precisely to its optimal setting.
We explain how heat anticipators work at HEAT ANTICIPATOR Operation and separately at HEAT ANTICIPATOR Adjustment. we explain how to adjust the heat anticipator on a room thermostat by moving its pointer arm.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved.
Since a room heating or cooling thermostat is really just a simple "on-off" switch, some fuzziness needs to be built into the thermostat's control of the air conditioner or heating system, lest it cycle on and off too frequently, oscillating very closely around the set temperature.
The job of the heat anticipator circuit in a wall thermostat is to prevent heating or cooling "overshoot" too far past the set temperature, but to permit some overshoot to prevent system on-off oscillation.
When we serviced heating systems and our clients sometimes complained that the thermostat did not seem to be responding as desired to room temperature.
The thermostat might permit the room to get much warmer, or much cooler than the temperature to which the thermostat was set.
This was a reason to whip out our little ammeter to see what was really going on with the thermostat circuit.
A second reason we'd use this ammeter to check the current draw of the thermostat circuit was to allow proper setting of a heating or air conditioning system control set which was made by a different manufacturer from the one who made the wall thermo sat.
For example, if the air conditioning or heating system control being switched on and off by the thermostat was not one of the ones in Honeywell's list, one of the checks we'd make is to actually measure the heating control circuit ampacity using a special mini ammeter sold just for that purpose, and shown in our photo at left.
Since we no longer service heating systems, we'll give our tool free to a trained heating service technician who'll pay the shipping postage.
Because some controls are used in common on hot water heat, hot air heat, and steam boilers, readers should see these other articles: see BOILER CONTROLS & SWITCHES, and also see BOILER COMPONENTS & PARTS for a detailed list of heating boiler controls, other heating system components, parts such as circulator pumps & draft regulators. If your building uses warm air heat, see FURNACE CONTROLS & SWITCHES. If your building uses steam heat see STEAM HEATING SYSTEMS. Also see Heat Won't Turn Off - Stop Unwanted Heat.
Usually these are "R" (red) and "W" (white wire) or "R" and "Y" terminals on thermostats.
Just connect the ammeter's leads to the thermostat terminals where you see the red and white wires coming from the heating system are already wired. (You'll have to remove the thermostat cover to perform these steps.)
The current flow (Amps) is read on the meter, and the heat anticipator is set to match the actual current that was just read.
How to Make the Correct Current (Amps) measurement at the thermostat heat anticipator
Watch out: T.D. points out that a few controls, such as motorized gas valves, draw more current while operating than when they are in the fully-open position. So if your ammeter shows an unusually high reading (say more than 1.2A) you should hold the ammeter leads on the terminals for an entire minute. By that time the motorized valve should be fully open and you should see a lower AMPS reading. Examples of equipment where you will face this problem include
Watch out: the amps reading made at the room thermostat can also indicate a system or wiring problem: if the meter continues to read current over 1.2A there is probably a system problem, risking damage to the thermostat itself.
What is the Exactly Correct Heat Anticipator Setting when Using an Ammeter?
This places the thermostat heat anticipator in exactly the right setting for the equipment to which it is attached. Then we simply removed our test leads and re-set the thermostat to the desired room temperature.
When the heat anticipator is working correctly, it prevents too much temperature "overshoot" when the thermostat is turning heating or air conditioning equipment on or off. Ultimately this means that the thermostat will maintain room temperature more accurately and more closely to the "SET" temperature set by the occupants.
Precaution when using this equipment: if the meter is wrapped in plastic there may be a static charge when you unwrap it. Because it is very sensitive, any static charge on this meter (or many other ammeters or VOMs or multimeters) can cause the dial movement to show an erroneous reading. Just wait 5 minutes before using the meter, allowing the static charge to dissipate.
The mini ammeter for adjusting thermostats to work precisely (shown at the top of this page) was produced by and may still be available from T.D. Instruments Corporation, 180 Charlotte St., Rochester, NY 14067 - 716-232-4208. We used model T.D. 2, which operates between 0 and 1.2 Amps A.C.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the search box below to ask a question or to search the InspectApedia.com website.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.