InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Heating zone circulator pump mounting position: is it ok to mount a circulator pump vertically, on an angle, or in some other position?
What do heating circulator pump manufacturers say about the mounting position of the circulator motor above or below the pumping impeller assembly? What about the location of wiring, oil cups, and related controls?
This article series describes how to diagnose & fix circulator pump problems on hot water or hydronic heating systems.
Question: circulator mounting position vs system pressure
Question: direction of hot water flow through the circulator pump and piping loop
(Feb 18, 2013) greg said:
I am installing a circulator pump on an outdoor wood boiler I have been told that some stove have been installed to pull water from toward the bottom and returning on top and also the other way around. what is your advise?
Greg I don't know quite what's the design of your system. In general, some installers like to put the circulator pump on the return side of the hot water piping loop, figuring that by running the cooler water rather than the hotter water through the pump assembly it will last longer.
Reader opinion on circulator pump images: up vs down:
(Mar 2, 2012) Ken said:
I'm seeing pictures of products installed incorrectly with no mention that they are wrong. You should only post pictures of the items that your talking about that are correctly installed.
The circulators at the top with the motor in the up position is incorrect unless your are running over 20lb's of system pressure, there are also pictures of oil filters mounted right at the burner on other pages which doesn't allow enough distance for the oil to stabilize before enturing the pump. There is more, but enough. Please upgrade your pictures.
Thanks Ken, interesting points, though in some cases lacking authoritative citation of expert sources. If you can give me a source citation for oil stabilization problems, for example, we'd be very glad to add that to our information. We also welcome reader contributions of photographs of both correct and problematic equipment installations.
The photos shown throughout these heating articles are indeed from "real world" rather than theoretical installations and are indeed deserving of comments about good and bad practices.
I have indeed observed circulator pump assembly bearing failures that occurred when a pump was not properly mounted, but generally that failure occurred because the motor was not properly supported or a new motor was mounted into an old, askew mounting bracket.
There are constraints on the location of wiring boxes and oil ports on some equipment but there is actually quite a bit of flexibility about the position of the circulator motor with respect to the pumping impeller assembly and with respect to the direction of piping.
I agree that some heating system oil piping installations place control valves (FIRE SAFETY CONTROLS) or heating oil filters (OIL FILTERS on HEATING EQUIPMENT) at less than ideal positions that make maintenance inconvenient for the service technician. We generally comment on these observations at those photos. So if you see comments missing at specific photographs in specific articles please let me know.
But your comments about oil stabilization and hot water heating system pressure vs. circulator position are not cited in the manufacturer's literature we have on review nor have I found references to your view in the literature. So some citations explaining your comments would be most helpful. Thanks.
Continue reading at CIRCULATOR OPERATION CHECKS or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES.
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
"Instruction Manual, Bell & Gossett Series LR Circulators" P86101D, Mayu 2012, Xylem Inc. 8200 N. Austin Avenue Morton Grove, Illinois 60053 Phone: (847) 966-3700 Fax: (847) 965-8379 www.xyleminc.com/brands/bellgossett
"Installation and Operation Instructions, Raytherm Residential Boilers," courtesy of Raypak®, and technical advisor Wayne Hoffman, personal communication 5/11/2009. Mr. Hoffman is a technical advisor with more than 30 years experience in the heating field. Raypak is a Rheem company that provides hydronic heating boilers for residential, pool, and commercial use. Raypak can be contacted at 866-583-0664 for technical support or for assistance in selecting the proper heating equipment for a specific application.
Rheem Corporation is a manufacturer of water heaters and heating equipment including Ruud heating and cooling products.
Bell & Gossett Air Separators and other heating system components, 8200 N. Austin Ave., Morton Grove IL 60053, USA - Tel 847 966-3700 Fax 847 965-8379 . Air separators are discussed by B&G at http://www.bellgossett.com/homeowners/BG-airseparator.asp
Taco air scoops and other heating system components & controls: Taco Inc., 1160 Cranston Street, Cranston, RI 02920 / (401) 942-8000 / Fax (401) 942-2360 Taco (Canada) Ltd., 6180 Ordan Drive, Mississauga, Ontario L5T 2B3 / (905) 564-9422 / Fax (905) 564-9436 www.taco-hvac.com
Taco also has some helpful FAQs that are useful in diagnosing circulator problems - see http://www.taco-hvac.com/en/faq.html#
Sparco air purgers, air scoops, and other heating system components & controls:
"Residential Hydronic (circulating hot water) Heating Systems", Instructional Technologies Institute, Inc., 145 "D" Grassy Plain St., Bethel, CT 06801 800/227-1663 [home inspection training material] 1987
Heating, Ventilating, and Air Conditioning Volume I, Heating Fundamentals,
Boilers, Boiler Conversions, James E. Brumbaugh, ISBN 0-672-23389-4 (v. 1) Volume II, Oil, Gas, and Coal Burners, Controls, Ducts, Piping, Valves, James E. Brumbaugh, ISBN 0-672-23390-7 (v. 2) Volume III, Radiant Heating, Water Heaters, Ventilation, Air Conditioning, Heat Pumps, Air Cleaners, James E. Brumbaugh, ISBN 0-672-23383-5 (v. 3) or ISBN 0-672-23380-0 (set) Special Sales Director, Macmillan Publishing Co., 866 Third Ave., New York, NY 10022. Macmillan Publishing Co., NY
Installation Guide for Residential Hydronic Heating Systems
Installation Guide #200, The Hydronics Institute, 35 Russo Place, Berkeley Heights, NJ 07922
Books & Articles on Building & Environmental Inspection, Testing, Diagnosis, & Repair
The ILLUSTRATED HOME illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The HOME REFERENCE BOOK - the ENCYCLOPEDIA of HOMES, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The HORIZON SOFTWARE SYSTEM manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones