Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ELECTRICAL INSPECTION, DIAGNOSIS, REPAIR
ACCURACY vs PRECISION of MEASUREMENTS
AFCIs ARC FAULT CIRCUIT INTERRUPTERS
ALUMINUM SECs & WIRING
ALUMINUM WIRING HAZARDS & REPAIRS
AMPS & VOLTS DETERMINATION
AMPACITY - the LIMITING FACTOR
APPLIANCE EFFICIENCY RATINGS
BACKUP ELECTRICAL GENERATORS
BACK-WIRED ELECTRICAL DEVICES
BOOKSTORE - ELECTRICAL
BUILDING SAFETY HAZARDS GUIDE
Cadet & Encore Heater Recall
CIRCUIT BREAKER FAILURE
CIRCUIT BREAKER SIZE for A/C or HEAT PUMP
Classified CIRCUIT BREAKER WARNING
CORROSION in ELECTRICAL PANELS
CORROSION & MOISTURE SOURCES in PANELS
CUTLER HAMMER PANEL FIRE
DEFINITIONS of ELECTRICAL TERMS
DIRECTORY OF ELECTRICIANS
DMM Digital Multimeter HOW TO USE
ELECTRIC METERS & METER BASES
ELECTRIC MOTOR DIAGNOSTIC GUIDE
ELECTRIC MOTOR OVERLOAD RESET SWITCH
ELECTRIC PANEL AMPACITY
ELECTRIC PANEL INSPECTION
ELECTRIC PANEL MOISTURE
Electric Power Frequency Table
ELECTRICAL DISTRIBUTION PANELS
ELECTRICAL GROUND SYSTEM INSPECTION
ELECTRICAL SERVICE DROP
ELECTRICAL SERVICE ENTRY WIRING
EMF RF FIELD & FREQUENCY DEFINITIONS
FEDERAL PACIFIC FPE HAZARDS
FIRE SAFETY Checklist, CPSC
GFCI PROTECTION,Testing GFCIs AFCIs
HEATING COST FUEL & BTU COST TABLES
HEAT TAPE USAGE GUIDE
Hertz - Definitions of KHz MHz GHz THz
KNOB & TUBE WIRING
LIGHTING, EXTERIOR GUIDE
LIGHTING, INTERIOR GUIDE
LIGHTNING PROTECTION SYSTEMS
LOW VOLTAGE BUILDING WIRING
LOW VOLTAGE TRANSFORMER TEST
MAIN ELECTRICAL DISCONNECT
MAIN DISCONNECT AMPACITY
MOISTURE SOURCES in PANELS
MURRAY SIEMENS Recall
PHOTOVOLTAIC POWER SYSTEMS
PUSHMATIC - BULLDOG PANELS
REMOTE ELECTRIC POWER, PHOTOVOLTAIC
RUST in ELECTRICAL PANELS
SAFETY for ELECTRICAL INSPECTORS
SE CABLE SIZES vs AMPS
SIEMENS MURRAY Recall
UNDERGROUND SERVICE LATERALS
VOLTS / AMPS MEASUREMENT EQUIP
VOLTAGE MEASUREMENT METHODS
WIND ENERGY SYSTEMS
WIND TURBINES & LIGHTNING
ZINSCO SYLVANIA ELECTRICAL PANELS
This article describes replacement Bulldog Pushmatic circuit breakers: The article gives advice to building owners whose building is served by a Pushmatic electrical panel, and we discuss both compatibility of and concerns when using replacement circuit breakers or used Pushmatic circuit breakers sold by salvage operators.
We solicit field failure and field inspection reports of questionable or possibly problematic electrical equipment in buildings such as the Bulldog™ and ITE-Pushmatic® brands described here.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Our photo (left) illustrates a typical single-pole 20-A Pushmatic replacement circuit breaker that is widely available.
Synonyms for this product include Bulldog or Bulldog Pushmatic circuit breakers, ITE Bulldog, ITE Pushmatic, and Siemens Pushmatic circuit breaker.
The photos below illustrate some of the variety of replacement Pushmatic type circuit breaker replacements and name their manufacturer and/or supplier.
Watch out: Replacement Pushmatic type circuit breakers are sold by several suppliers as well as "used" or "salvaged" - a status that should raise a question about the unknown condition, history, and thus reliability of salvaged breakers and thus of their safety.
Watch out: as we detail at PUSHMATIC - BULLDOG PANELS there are safety hazards and warnings concerning use of Pushmatic-type circuit breakers that should give pause about replacing or repairing these panels versus replacing them entirely. Examples that suggest that the problems are more than just theoretical arm-waving can be read at PUSHMATIC BREAKER FAILURE REPORTS.
At below left is a 15-A Pushmatic replacement circuit breaker provided by ITE-Siemens.
At below left is a Bulldog Pushmatic replacement circuit breaker distributed by Connecticut Electric. At below right is at Siemens P240 2 Pole 40A Pushmatic Breaker produced
by Siemens Electric.
At left is another example of a used Pushmatic circuit breaker for sale on EBay.
As we warned above, the use history, exposure to moisture history, and thus the condition of used circuit breakers is unknown - such devices may carry an extra reliability hazard (and thus a fire hazard) beyond the other Pushmatic, ITE Pushmatic, and Bulldog Pushmatic circuit breaker hazards discussed in the article above.,
Continue reading at PUSHMATIC - BULLDOG PANELS or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs) about buying a replacement circuit breaker for Bulldog Pushmatics or ITE Pushmatics
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References