Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
CHIMNEY INSPECTION DIAGNOSIS REPAIR
BACKDRAFTING HEATING EQUIPMENT
CARBON MONOXIDE - CO
CHIMNEY CAP & CROWN
CHIMNEY CLEANING PROCEDURES
CHIMNEY COMPONENT DEFINITIONS
CHIMNEY CRACK DETECTION & DIAGNOSIS
CHIMNEY DRAFT & PERFORMANCE
CHIMNEY FIRE ACTION / PREVENTION
CHIMNEY HEIGHT & CLEARANCE CODE
CHIMNEY INSPECTION, FLUE INTERIOR
CHIMNEY LEANING, SEPARATION, MOVEMENT
CHIMNEY REPAIR METHODS
CHIMNEY STAINS & LEAKS
CHIMNEY TYPES & MATERIALS
COAL STOVE OPERATION & SAFETY
DIRECT VENTS / SIDE WALL VENTS
DRAFT HOOD, GAS HEATER
DRAFT REGULATOR, DAMPER, BOOSTER
FIRE CLEARANCES INDOORS
FIREPLACES & HEARTHS
FLUE VENT CONNECTORS
MASONRY CHIMNEY GUIDE
METAL CHIMNEYS & FLUES
SAFETY RECALLS CHIMNEYS VENTS HEATERS
SOOT AT CHIMNEY TOP
STAIN DIAGNOSIS on BUILDING EXTERIORS
WOOD-OIL COMBINATION HEATERS
This article describes exceptions to the general case of prohibiting shared chimney flues, multiple heating appliances, fireplaces, woodstoves all using the same chimney venting path through a building and to outside.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
Shared flues can create fire and smoke spread hazards and carbon monoxide hazards in buildings. In some communities or jurisdictions for certain cases, it is permissible to share a single chimney flue among more than one heating appliance or fireplace. But important safety constraints still apply.
[Click to enlarge any image]
Our photo (page top) shows two gas-fired appliances sharing a single flue. Here are some additional examples of commonly occurring shared chimney flues, courtesy of Carson Dunlop.
A wood-fired heating appliance may be vented into the same chimney flue as an oil-fired heating appliance provided that they are on the same floor - in some jurisdictions.
Combination wood-oil fired heating boilers join wood and oil burners in the same physical unit, making this exception necessary if the boiler is to be used at all.
However we found some difficulty in tuning the oil burner to work at its best when a combined fuel unit was installed, because on the models we serviced the draft requirements were different depending on which fuel was in use, and because it was not the case of these systems working in an "either-or" mode - that is exclusively burning only heating oil or only wood at a particular time.
More common, the wood fire might be burning down low and no longer providing enough heat, requiring the oil burner to turn on.
We also opine that it is very important to keep the chimney well cleaned in a combination unit or a shared wood and oil device chimney. A slow-burning woodstove can deposit thick combustible creosote on chimney walls, especially if the users are burning wood that is still green, or if the wood heater is not run at a sufficiently hot temperature.
We worry that the oil burner exhaust or the exhaust from a later and hotter wood fire might set the creosote afire - causing a very dangerous chimney fire.
Be sure your chimney is inspected and cleaned at least as often as the manufacturer of your appliances and your local fire marshal recommend.
In some locales fire officials also permit two gas appliances to vent into a single flue when the heaters are on different floors, as we see in Carson Dunlop's sketch.
Since there is a potential of increased risk of fire or gas leak spreads between floors in this shared flue arrangement, additional installation details may be required, if this is permitted at all. Check with your local fire officials and building code enforcement officers.
Multiple oil-fired devices may be vented into the same flue from the same utility area and same building floor provided the flue capacity is adequate. Also see safety and functional notes about draft balance and regulation at Draft Regulators, Dampers.
In some jurisdictions it is permitted to vent a gas fired appliance into a chimney where oil fired appliances are also vented, with special design details needed to prevent back-drafting out of the gas fired appliance
This installation may not be permitted in your locale, and there are fire and smoke spread hazards as well as possible draft adequacy questions.
Be sure you have your fireplace flues inspected for safety, and where a shared flue is discovered check with your fire marshal and local building code official before attempting to use either fireplace.
Sketch courtesy Carson Dunlop.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about cases when shared chimneys or chimney flues may be permitted.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References