Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
CHIMNEY INSPECTION DIAGNOSIS REPAIR
BACKDRAFTING HEATING EQUIPMENT
CARBON MONOXIDE - CO
CHIMNEY CAP & CROWN
CHIMNEY CLEANING PROCEDURES
CHIMNEY COMPONENT DEFINITIONS
CHIMNEY CRACK DETECTION & DIAGNOSIS
CHIMNEY DRAFT & PERFORMANCE
CHIMNEY FIRE ACTION / PREVENTION
CHIMNEY HEIGHT & CLEARANCE CODE
CHIMNEY INSPECTION, FLUE INTERIOR
CHIMNEY LEANING, SEPARATION, MOVEMENT
CHIMNEY REPAIR METHODS
CHIMNEY STAINS & LEAKS
CHIMNEY TYPES & MATERIALS
DIRECT VENTS / SIDE WALL VENTS
DRAFT REGULATOR, DAMPER, BOOSTER
FIRE CLEARANCES INDOORS
FIREPLACES & HEARTHS
FLUE VENT CONNECTORS
MASONRY CHIMNEY GUIDE
METAL CHIMNEYS & FLUES
SAFETY RECALLS CHIMNEYS VENTS HEATERS
SOOT AT CHIMNEY TOP
STAIN DIAGNOSIS on BUILDING EXTERIORS
WOOD, COAL STOVES & FIREPLACES
This article describes structural movement of chimneys that can be observed or predicted indoors in buildings. Our page to photo shows a leaning brick chimney in the attic of an older home. The lean may be excessive in this flue - making further detailed inspection of the chimney for gaps, cracks, leaks, fire or gas hazards important.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Chimney Movement detected indoors in masonry chimneys can cause damage to the flue liner or openings that might admit sparks (fire risk) or gases (carbon monoxide hazards) into the building structure or even into occupied spaces.
The photograph here shows a leaning, corbelled brick chimney in a pre-1900 home.
[Click to enlarge any image]
When inspecting an old chimney which was corbelled over at an angle to come out at the center of the building roof's ridge (done for aesthetic reasons) inspect the chimney carefully at the attic floor where the chimney changes from angled (corbelled) to vertical.
This floor-level inspection, that is, inspection at the point from which a leaning masonry chimney begins to deviate from its original vertical structure, is a critical space to look for hidden and possibly dangerous damage, especially if the chimney is small, possibly constructed of a single brick wythe in thickness.
If the corbelled chimney flue has sagged along with the roof, the chimney may be cracked and open at this point even though other cracks were not seen.
In the attic inspect the chimney thoroughly at all accessible surfaces, floor to roof.
Our photo at left shows severe movement and openings in this brick chimney in an attic close to the roof surface. The vertical mortar joints between the bricks show openings of about 3/4" in width - you can see that the mortar has fallen over on an angle in these openings.
This chimney is a fire hazard, a carbon monoxide hazard, and a collapse hazard. Further inspection would be needed to determine if the damage was only in this area and due to water and frost (no chimney cap or crown) or if the chimney was moving and settling - leading to a need for reconstruction.
This damage pattern is more likely to be found on single-wythe thick brick chimneys than on chimneys built with multiple wythes of bricks forming the chimney wall.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about diagnosing & repairing cracked, leaning, separating or moving chimneys - clues visible from inside the building.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References