Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
CHIMNEY INSPECTION DIAGNOSIS REPAIR
BACKDRAFTING HEATING EQUIPMENT
CARBON MONOXIDE - CO
CHIMNEY CAP & CROWN
CHIMNEY CLEANING PROCEDURES
CHIMNEY COMPONENT DEFINITIONS
CHIMNEY CRACK DETECTION & DIAGNOSIS
CHIMNEY DRAFT & PERFORMANCE
CHIMNEY FIRE ACTION / PREVENTION
CHIMNEY HEIGHT & CLEARANCE CODE
CHIMNEY INSPECTION, FLUE INTERIOR
CHIMNEY LEANING, SEPARATION, MOVEMENT
CHIMNEY REPAIR METHODS
CHIMNEY STAINS & LEAKS
CHIMNEY TYPES & MATERIALS
DIRECT VENTS / SIDE WALL VENTS
DRAFT REGULATORS, DAMPERS, BOOSTERS
FIRE CLEARANCES INDOORS
FIREPLACES & HEARTHS
FLUE VENT CONNECTORS
MASONRY CHIMNEY GUIDE
METAL CHIMNEYS & FLUES
SAFETY RECALLS CHIMNEYS VENTS HEATERS
SOOT AT CHIMNEY TOP
STAIN DIAGNOSIS on BUILDING EXTERIORS
WOOD, COAL STOVES & FIREPLACES
Metal chimney & flue bracing & support specifications: this article describes bracing and support requirements for metal chimneys.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Metal chimneys that are more than 5' tall above the roof (or 6' tall in some jurisdictions) require bracing at the rooftop. Sketch (above right) courtesy of Carson Dunlop.
Photo at left: metal bracking on a B-type vent metal chimney. Notice that metallic salts washing off of the metal bracing and other runout of the chimney flashing itself are preventing black algae from growing on some areas of this roof.
At Class A Chimneys we discuss the collapsing Class-A metal chimney shown at above left. As you can see, a metal chimney on the outside of the building will also require support listed and designed by the manufacturer.
Bracing can stabilize a manufactured chimney or it might stabilize a tall masonry chimney that is wobbly but on a good footing - also review moving/separated chimney repairs at Leaning Chimney Repair Methods.
Metal chimneys more than 5' tall require bracing that connects the chimney to the building. The crazy chimney shown at below left had visible openings at its tipped joints - this was an unsafe installation.
The very tall single wall metal chimney shown at below left is located on a building in Manhattan and was photographed from the Lotus Club. Although the chimney has bracing, chimney sections are loose at several locations giving a sort of drunken sailor look to this flue.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about bracing & support requirements for metal chimneys & flues.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.