InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Plumbing drain noise diagnostic FAQs:
Frequently-asked questions & answers about the types, causes, & remedies for plumbing drain noises & sounds.
This article series explains how to determine the causes of plumbing drain noises, and we refer to key companion articles that assist in that diagnosis, and we include plumbing noise cures.
Green links show where you are. © Copyright 2017 InspectApedia.com, All Rights Reserved.
Recent Reader Questions & Answers about Plumbing Drain Sounds posted either at the end of this article or at the topic home PLUMBING DRAIN NOISE DIAGNOSIS
On 2018-02-07 by (mod) - better sewer line under a road or driveway
It might be possible to excavate the soil pipe trench, install solid (maybe concrete walls and top) reinforcement over the piping so that it's not affected by over-traffic - that might also reduce the chances of breaking the sewer line. Or replace under-specified sewer piping with the proper weight and strength pipe rated for under drives (sch. 80?
On 2018-02-06 20:19:35.387616 by beoffwith you
I have a plastic soil pipe outside serving an upstairs bedroom cars passing the house run over a road access hatch and the drum sound travels all the way up the pipe and into the house where there is 1 meter of soil pipe running to the toilet is there any way that I can stop this constant noise inside or outside the house
On 2018-02-07 by (mod) - assistance with a drain line that keeps clogging - after tank is pumped
If you still get sewage backups then the problem hasn't been identified correctly. Pumping the septic tank will never fix sewage backups, just defer them for a few days. You need to know if the issue is damaged sewer piping or a failed drainfield.
You might start at SEPTIC SYSTEM INSPECTION & TEST GUIDE
On 2018-02-06 by Shirley R Edwards
I need assistance about a possible vent problem. I had my septic tank pumped, my drain fields cleaned and my lines cleared of clogs, ut i still get back ups after s few days
On 2018-02-03 2 by (mod) - signs of drain venting problem
Sounds to me as if the new drains are not properly vented. When water rushes down the un-vented drain the vacuum that slug of water or waste creates draws air into the drain through nearby traps, causing gurgling. That's not safe in the long run as there is a risk of sewer gases entering the building through a dry trap. Sewer gases smell and are also potentially explosive.
If the work was done with proper permits and inspections I'd expect the plumbing inspector to have wanted proper venting. If not we missed a chance to do the job right.
On 2018-02-03 by AnnMarie
The gurgling sounds is in the tub
On 2018-02-03 by AnnMarie
We just had our bathroom remodeled. New sink, toilet, tub. Now we have a gurgling sounds when we flush the toilet. What could be causing this
On 2018-01-22 by Jenni
I have a new home with a high effeciency furnace. The condensate drip line drains into the same line as my washing machine.
However, the condensate drip line ends where the opening for the wash machine line starts, therefore when the condensate drains as it's supposed to, it drips all the way down to the P trap so I get to constantly listen to dripping water. Any suggestions on how to quiet this drip, it's driving me insane!!!!
On 2017-11-26 by (mod) -
What you describe is a bit unusual in my experience. Let's start by checking the length of the tailpiece that is above the actual P trap.
It may be this length is quite great and that if you move the Trap up you can reduce the noise of water falling into the bottom of it.
On 2017-11-26 by (mod) -
What you describe is a bit unusual in my experience. Let's start by checking the length of the tailpiece that is above the actual P trap. It may be this at length is quite great and that if you move the Trap up you can reduce the noise of water falling into the bottom of it.
On 2017-11-21 by Dave
Just put in a bathroom sink....when I run the water, the draining water makes a loud noise as it hits the water in the p-trap. Wrapping the p-trap won't make much of a difference since the nice is coming from the drain itself....what can I do to reduce the draining sound?
On 2017-11-02 by Megan
I've got 2 sinks in my kitchen, The sink in the island gurgles if pouring a lot of water at once into the other sink which is right across it. Sometimes the washer down in the basement floods as a result.
we had 2 major floods and thought it was blockage and had called ppl in to unclog it but soon after it starts gurgling again. We never know when we'll have another flood again. Any ideas as to why this happens? Thanks!
On 2017-10-16 by Lauren
Intermittently I have heard the sound you hear after you flush the toilet - the water running- but it's sounds if it is coming from my below my bathtub a good 30 sec
I heard it this morning when I got up to use the restroom. Toilet hadn't been flushed since night before
On 2017-10-03 by Renee
One of my 2 bathrooms has gurgling noises coming from the toilet and/or bathtub. This happens when water drains from sink or toilet is flushed. Both the sink and toilet are draining into the bathtub.
Liquids or solid like tissue will come back up through the bathtub. The water drainage from a shower or bath causes water to flow from under the toilet. The bathtub is the only 1 out of the 3 to drain slowly.
I have a second bathroom towards the from of my home that is draining normal. No noises either. All other drains don't have any issues. I have tried augers up to 25 ft. in the toilet, bathtub, and roof vent. I ran a stream of water by hose down the roof vent and no water returned, but it all went into the bathtub and from under the toilet. It may help to know that we experienced this problem 4 weeks ago, but a 10 ft, manual auger cleared the problem
It has now returned. Is there anything else I might look at? Would a bad wax seal cause these problems (since I didn't change it 4 weeks ago during initial problem)?
On 2017-09-28 by (mod) - kitchen sink has sound of running , dripping water in the drain
If a careful inspection below the area convinces you that there is no leak I would be looking for a partially blocked drain
On 2017-09-28 1 by Anonymous
Our kitchen sink has sound of running , dripping water in the drain area . It's a double sink noise not in the garbage disposal area. What to look for to fix.
On 2017-09-18 22:31:26.236867 by Anonymous
Water heater exposed next to has stove no drain no vent! Is this legal?
On 2017-06-11 1 by (mod) - glug noise when toilet on flat above is flushed
That sounds to me like a clogged drain or a defective plumbing vent system. As the problem is recent a clog is more likely than an original design problem with the drain or venting system. A plumber can inspect or use a sewer camera to scope drains and vents to look for a blockage.
On 2017-06-11 by Bill
Hi, when person in the flat above flushes toilet there is a loud 'glug glug' sound accompanied by a 'slight drains smell' in our bathroom. Person upstairs does not notice anything unusual, nor does person below us. Flats are 5 years old. This is only a recent problem. Can you help?
On 2017-06-05 by (mod) -
I agree that the dream noise situation that you described sounds puzzling. However it is still possible that the problem is a partial drain blockage a bit Downstream in your system.
The probability that the specific fixture causes the drain noise that you describe maybe in part a function both its drainage rate and the volume of water that is run through the fixture. For example taking a shower probably runs a total larger volume then emptying lav basin. And the rates of drainage are different as well.
If the blockage is farther Downstream than the length of your plumbing snake, you would not detect it who you tried a longer snake or perhaps and a sewer camera through the drain system. That's what I would try. Do keep me posted as what you learn will help other readers.
On 2017-06-05 y Bobk - new noise at sink drain when shower runs
When my second floor shower drains, my kitchen sink drain on the first floor has started to make a glug, glug sound. The kitchen sink is diagonally below the shower drain.
The noise is new. I have checked both drains for blockage and there does not appear to be any interference as both drains freely and quickly. Also, the same drain handles the shower/sink and I don't hear any noise when draining a Full sink.
Do you have any recommendations?
On 2017-05-22 by (mod) - whistling noise when water runs
Marie if the whistling noise occurs only when water is running then it's a water supply pipe noise not a drain problem nor a septic tank issue. Let's start with that diagnostic step.
On 2017-05-22 by Marie
My restroom sink is making a whistling sound, I dont know if its the septic tank or what.
On 2017-04-23 by (mod) -
Great. Good detective work. Keep me posted.
On 2017-04-23 1 by John Mathisen
That is a useful suggestion. We don't have AC but we do have MVHR which has a condensate drain.
The MVHR is in the loft and the drain goes down inside the wall of the bathroom and presumably joins the main drain there. The installation instructions say this should go into a u bend to create a trap if it discharges into a soil pipe. I can't see a u bend! The next time I hear the noise I will power off the MVHRto see if that stops it.
On 2017-04-21 by (mod) -
I don't have a good guess, John, but I'd look for equipment that might be dumping wastewater into the drain system - HVAC equipment for example.
On 2017-04-20 22:20:05.597861 by John Mathisen
I have a newly built house. One shared bathroom with bath, shower, basin and WC sometimes gets an ocillating noise as if water is swishing back and forth at about 72 beats per minute. It can carry on for hours but stops overnight. It's not clear what starts it and why it does not happen every day.
All the fittings have full traps and when they drain, there is no delay. There is a Durgo air inlet valve in the bathroom. The noise can also be heard when you lift the cover on the main drain just before it joins the public drain in the road.
An ensuite bathroom with its own external stack has no noise. What can be causing this annoying drain noise?
On 2017-04-17 by (mod) -
That's indeed curious. Are you sure that there are no nighttime uses of your drain system such as a water softener regenerating or rental tenants in other areas of the building?
On 2017-04-17 by hudson valley family dental
why leaks..gurgling...water splashing throgh sink drain only in the morning
On 2017-04-06 by (mod) -
I'm not sure, Wendy, but if the problem is new I suspect a remote partial drain clog;
You may need to hire a plumber who can run a camera through the drain line.
If you do so, let me know what you're told and we can perhaps offer some suggestions.
On 2017-04-06 1 by Wendy
We have a tapping or drumming noise when water drains out of our kitchen sink....what is the likely cause and a solution... We have tried drano to it and no success.
On 2017-03-25 by (mod) -
Sounds like a venting problem. If new, then a vent may be clogged by an insect nest or something like that.
On 2017-03-25 by Doris
When I empty the kitchen sink, the drain in the laundry room gurgles.
On 2017-03-18 by (mod) -
Typically that's a clogged drain or main drain - especially likely to be the case if the gurgling is a new or just-recent problem
On 2017-03-18 by Joyce
My drains are gurgling and I smell sewage what is wrong
On 2017-03-16 1 by (mod) - sink water won't stop running
Heck I hate when that happens.
If you're lucky there's a separate shut-off valve on the hot and cold supply riser pipes below your sink. Close those.
If there are no shutoff valves there there may be other shut-off valves feeding that area of your home.
Otherwise your plumber will simply turn off all water to the building while fixing your sink faucet or control.
That's a good time to be sure that other shutoff valves are installed and working too, making repair easier next time.
Also see WATER SHUTOFF VALVE LOCATION - at http://inspectapedia.com/plumbing/Water_Shutoff_Valve_Location.php
On 2017-03-16 19:25:52.059634 by Renee
My sink water won't stop running and my water is turned off, I also hear a noise like coming from the knob on the hot water only
On 2017-03-16 15:35:24.598475 by (mod) -
Interesting question Jose. Perhaps a partial blockage in the drain line; water passing over such a block might cause vibration.
On 2017-03-16 15:10:08.740738 by JoseW
What would cause the main drain pipe from the second floor to vibrate after the toilet is flushed? This started about 2 months ago, and is getting a little louder. It doesn't happen after every flush, only after flushing that included toilet paper.
There is no gurgling in the sink or tub and all drains in the house drain as they should, so I'm assuming the vent is clear. Just to be clear, the main drain pipe is vertical and all the smaller drains feed into it.
The bathroom on the second floor, then the kitchen sink and dishwasher on the first floor.
On 2017-11-20 by (mod) - why is water running in our sink drain when the sink isn't in use?
Depending on brand, model, age, a refrigerator might drain during defrost cycle, but usually that just spills into a pan in the fridge base where it is "disposed-of" by evaporation.
Still, 1/4" is so small that I'd bet on a refrigerator or A/C condensate drain line or maybe, depending on how the water filter works, filter wastewater (such as from an RO system).
Below in my first test of a new Comments Box feature I'm clicking the little image icon next to the "Comment" button to see if I can drag in a photo of a more-typical under-sink appliance drain connection into the sink drain tailpipe.
You could test the theory by turning off the water supply to your refrigerator for a bit.
On 2017-11-20 by thomasmyers21
Thanks, mod. I totally get that. When I look at the connections under the sink I can see a small (maybe 1/4" diameter) black plastic hose connected directly to the drain pipe about 5 inches down from the drain base.
I cannot tell where this line runs to, however. With my fingers it feels as though it parallels the copper water line that runs to the refrigerator, but cannot be certain. I confess that I don't have a good knowledge of how the refrigerator water system works
. Our fridge has a filtered water system for drinking water and ice making. With that said, are you saying that there is a problem perhaps with the refrigeration filtration system or something??
On 2017-11-20 by (mod) - where's the drained-water coming from?
A sink cannot be draining water unless there is water to be drained. Take a look under the sink to see if there are not connections to its drain line such as water from a refrigerator condensate drain, a dishwasher, an air conditioner condensate drain.
On 2017-11-20 by thomasmyers21
Hi - our kitchen sink will spontaneously start draining water when there's no water in the sink nor is the faucet running. This is a dual sink and I am able to peer into the drain and visually see the water trickling through the drain.
Just prior to this we had our septic lines cleaned and also prior to this we could hear air knocks in the lines. What could be causing this?
The ONLY thing that makes sense to me could be that the refrigerator water system is flowing back into the sink, because I cannot figure any other source where the water could be coming from. I've tried shutting off all the valves under the sink when I see this happening.
On 2017-10-24 by vee
Please help , gurgling noise always in washer dryer unit in highrise condo
On 2017-09-19 by (mod) - water supply pipe vibration sources
Typically that's a water supply pipe vibration due to the water velocity, pipe size, routing, length, elbows, and other factors. Often a simple small change in the velocity made by party closing the main water supply valve will fix the problem. That's a good place to start. Details are at WATER SUPPLY PIPE WHISTLE NOISE https://inspectapedia.com/noise_diagnosis/Water_Pipe_Whistle_Noise.php
On 2017-09-18 by Alice
Hello, the pipes in our bathroom (before once a day, now worryingly more frequently) have been making a horrendously loud, vibrating / throbbing sound that lasts for over a minute (used to be more like 30 seconds, now more like 2 minutes).
The noise has happened after we use the bathroom but also, and more often, tends to wake me up between 1 and 5 am. I've lived here 4 months and this has been the past week only, do you have any suggestions as to what it could be? We obviously need a plumber to come check but I'm panicking in the meanwhile. Honestly, it's loud enough to be genuinely a bit scary, not a noise I like any part of a house making, can't think what the neighbours think. Thanks so much for any help!
On 2017-07-24 by (mod) - sources of water backflow into a sewage pump or ejector pump making it run "for no reason"
Wow, several hours, how odd. Is there at your property:
a sewage ejector or sewage pump system that is cycling on later is most-likely being triggered by
On 2017-07-22 by Terry Medearis
After turning off a bathtub shower and waiting several hours, a vacuum sound comes from the fixture. If I turn the bathtub water on-off quickly, the vacuum sound goes away, only to return several hours later. Any idea what might cause this?
On 2017-07-17 by (mod) - test to see where gurgling sound is coming from
Try pouring a bucket of water, or running a lot of water, into that same sink and see if that also causes a gurgling sound.
Separately when the sink is empty, try flushing the nearby toilet to see if that causes a gurgling sound at the same sink drain. If neither of those events causes gurgling then you are hearing the trickling sound of the condensate draining into the fixture but there is probably not a drain blockage nor a ventng defect
On 2017-07-17 by Nathan
Ok that makes sense. I've noticed now too a slight gurgling in where the ac unit is and this is the sink that the ac drains into. I seem to be the only unit this is happening to. I'm not sure if there's anything I can do about that.
On 2017-07-17 by (mod) - A/C condensate drainage as drain noise source
Good sleuthing. So try temporarily re-routing the A/C condensate as a diagnostic step. If you're in a hot humid climate it's possible that quite a bit of condensate production is continuous.
On 2017-07-16 by Nathan
Ok so I have some more variables here. The bathroom sink that is gurgling is also hooked up to my AC condensation line. And I heard it gurgling a little this morning when I woke up. The sink drain hasn't stopped gurgling in 3 days.
On 2017-07-16 by (mod) - a partly blocked drain can cause drain noises
No Nathan. A partially-blocked drain, particularly if the blockage is pretty far distant from the fixtures or even outside and distant from the building itself, will accept a considerable volume of wastewater, say several toilet flushes in succession, without backing up into the building.
But wastewater "stored" in the waste line upstream from the blockage will then continue to seep through the blockage and give the gurgling you describe. That problem is more likely to be noticed if venting is also inadequate - the seepage of waste past the blockage creates a vacuum behind it (upstream).
If venting is working air is drawn into the waste piping and building plumbing drain traps remain silent and un-bothered. But if venting is blocked or inadequate, that vacuum "sucks" air into the drain system from the building, down through sink, shower, or tub traps and thus, as air passes through those water-filled traps, the gurgling may appear right at the fixture.
Gurgling may continue for some time as wastewater continues to drain past the blockage, even when the fixture isn't in use.
If after hours of no water being run at fixtures you still hear the sound I suspect that there is water entering the drain system somewhere that has escaped attention, such as
- a running toilet
- roof drainage into the waste pipe system
- groundwater leaking into a septic system or wastepipe system
On 2017-07-16 by Anonymous
ok but if it was clogged wouldn't it be backing up some? It drains perfectly just has a constant gurgling sound that doesn't stop ever and is getting louder.
On 2017-07-15 13:11:20.511741 by (mod) - drain clogs are more-common than vent clogs
Drain plugs are in my view much more common than vent clogs (unless it's a wet vent that also handles drainage). That's because of vent pipe in most Plumbing Systems is normally open and filled just with air while drains have Solid Waste flowing through them and are more prone to blockage.
So on my view I always start by attempting to clear a clogged drain. If plunging a toilet or a sink or a tub or shower drain doesn't clear it after a few minutes of trying I might then need to actually have the drain snaked or cleared with a power auger. If you use the inspectapedia search box above to find out article on kinetic water Ram you may find another neat tool that can often clear a blocked drain
On 2017-07-15 by Nathan
I've been living in this upstairs apartment for about 3 months now and just this week the bathroom drain has been glug gluging. It started real quiet and has been getting progressively louder. I now have to close the bathroom door and can still hear it
. I've done some research and people say it's probably the vent pipe or drain pipe clog/partial. My question is. How do I find out what one it is? Drain or vent? I'm on the second floor and it's technically a condo so no on site maintenance. Please help.
On 2017-05-16 by (mod) - Pumping the septic tank will never fix a clogged drain nor a failed draonfield.
Pumping the septic tank, while required to preserve the drain field, will never fix a clogged drain nor a failed draonfield. A septic tank, in nomal use, is always full..
What we don't know is if the clog is between your house and tank or rather if the draonfield is failing.
Motor noise that you hear sounds like a sewage ejector pump
On 2017-05-16 by Kristy
Live in Florida, been in home 13 years, have septic tank with sump pump tank and no filter between the two, never had to pump tank out until today. Kitchen sink has its own pipe to the main pipe running to the solids tank. Started to back up after few seconds of running water.
Snaked it 3 times, draino it twice. Thought it was just septic need pumping. Note V both full bathrooms drain fine. Started hearing what sounds like a motor, possibly the sump pump, running in the sink drain after the water would go down.
After septic was pumped today the sink was still clogged? Snaked it again and water appears to be draining only we hear this motor type sound coming up from the drain and is rather loud? NEVER heard this sound before after 13 years? What is it?? Husband says its the sump pump, so why have we never heard it before?
There's no baffle down low in the tank only at the top going to sump pump section. I disagree with him only because I know I have not run 1000 gallons of water in a few hours to fill tank and cause pump to kick on. What in the world could this be??? Please help so I don't feel like I'm starting to just hear things that were never there before? Lol
On 2017-05-06 by (mod) - why does kitchen sink noise change?
If the noise is coming from the plumbing drain, I suspect that we're seeing a difference in the rate of flow of water into the drain. If the noise is coming from the supply piping I suspect that when you move your sprayer you are thinking a flexible line under the sink and reducing the water flow rate.
On 2017-05-04 by babygirl
why does the kitchen sink make a diffrent nosie when i spray the spout in a diffrent spot
On 2017-04-24 by (mod) re: kitchen sink bubbles my toilet bubbles when my shower is on
It sounds as if the vent for the drain system you describe is clogged or incomplete, but it also sounds as if the main drain or toilet drain is clogged. If plunging for a while with a toilet plunger doesn't fix the problem start at BLOCKED DRAIN REPAIR METHODS
On 2017-04-24 by D
My kitchen sink bubbles my toilet bubbles when my shower is on and shower is clog up and water is staying in it toilet running overs please help me
On 2017-04-23 by (mod) re: After a hard rain dishwasher flooded
TR Yes what you suggest is possible - moreso if your home is connected to a private septic system.
On 2017-04-23 TRowe
Recently I had 2 odd things happen. After a hard rain I used my dishwasher as usual and it flooded. Thinking it was a fluke I got the water up after inspecting the dishwasher. I washed clothes all day and at the end of the day once again ran another load in the dishwasher while also washing a load of clothes.
The next thing I know the house is flooded. I think this was probably caused by a slow drain from the recent rain. Is that possible?
On 2017-04-19 by (mod) re: washer and its drainpipe, smell like sewer.
I suspect the drain is not vented,and it may also not be a proper destination for the washer drain.
On 2017-04-19 by Libby
My washer and its drainpipe, smell like sewer. The floor drain 5 ft from the washer waste line gurgles or makes sucking noise. Dehumidifier, AC and air exchanger have hoses draining into the this floor drain. Put water into floor drain, still makes noise.
On 2017-04-03 by (mod) re: low running noise in a home
I don't know, from just y our e-text, anon, what is causing a "low running noise" in your home. If you mean running water, I'd start by shutting off each plumbing fixture individually - that can diagnose the source, such as a running toilet.
On 2017-04-03 by Anonymous
We had new pipes installed in our home recently and now have a low running noise that I don't know where it is coming from. Could it be the new pipes?
On 2017-03-27 23:07:12.476657 by (mod) re: signs of a clogged drain or blocked vent show up at the kitchen sink when washing machine runs
Usually the problem is either a clogged drain or a defective or blocked vent. It sounds to me as if the kitchen sink drain comes down to a point where the washer drain joins it and then continues out of the building - if so I suspect that the vent is inadequate, missing, or clogged; the added drain volume of the washer flowing through the drain system creates a vacuum that is burbling back up through the sink because it's air -starved.
Most washers empty into a standpipe that acts as an indoor Vent. It's possible that your washer drain hose is tightly fit or even sealed into its standpipe, exacerbating the drain problem.
You may need added venting on the washer drain.
On 2017-03-27 by Carolyn
Help please my kitchen sink above the laundry room gurgle each time the washing machine empty! It is only the sink in the kitchen and not to the bathroom next to the laundry room It drains fine so the noise is only in the kitchen drain !!!
Been in the house 40 years and this problem is 2years old . I had a clog in 2015 and 2016 Plummer said it was from the wrong t paper so I switched!' And now that noise is back but drains run fine
Any thoughts that you can help me with
Oh yeah my second floor bathroom is fine also!! Just the noise in the kitchen from the washing machine
On 2017-03-18 by (mod) re: signs of inadequate venting of a sink or lav
Alex it sounds to me as if the way the sink drains are arranged one of them is inadequately vented. I speculate that using the sink that is more-remote from the actual drain line is when you hear the problem. But it could go either way. If the sink pair is inadequately vented, water passing down one of the drains may be creating enough vacuum to draw air in through the sister sink trap.
On 2017-03-17 by Alex
I wanted to clarify my previous comment I have two sinks next to each other both drain perfectly when you run one and not the other there's a bubbling noise coming out of the other drain. When I run the water in the other one that noise goes away. And if you run the one that has the bubbling noise and not the other one there is no bubbling in that other sink.
We have two bathroom sinks next to each other. Both work fine but when one of them is Only and not the other always same one) , there is a bubbling noise in the drain of the other sink not being used. If you run water in the other sink at the same time the bubbling noise goes away. and it IS NOT the same the other way around. Why is that both drains drain perfectly,
On 2017-02-22 by (mod) re: signs of a blocked or clogged soakaway bed or leach field
A failed or blocked septic drainfield
On 2017-02-21 by Mary
A vent pipe, located in the drain field occasionally has water pouring from it. What can cause this?
On 2017-02-14 by (mod) re: water pools in the shower and in the yard
Unlike Johnny Carson's Magician the Great Carno, I can't really see what's going on at your home, what plumbing system piping, drains, routing, vents, leaks or blockages are occurring as your message is (nicely) brief.
But I am GUESSING that your main drain is blocked (or if you're on septic, the tank or drainfield are blocked or in failure).
That might indeed cause drainage to back up to a level at which it empties at a vent opening the the drain system that is sometimes found on some buildings in a building wall or at an inspection port along the run of a sewer or septic line.
Time to call a plumber.
On 2017-02-14 by Vee
Water pours out of the drain on the side of our house when we use the shower.
For the first time today, the water actually pooled on top of drain after all shower water ran down the yard.
Why would the water come up out of drain and down the yard ?
On 2017-02-15 by (mod) re: mobile home drain noise diagnosis and repairMegan,
On 2017-02-13 by Megan
Recently we been having problems with our drains, we leave in a mobile home park,
I first noticed it when the toilet would flush the kitchen sink would gurgle, I informed our landlord about it and the maitence guy came and check things out, but of course it wasn't making any noises, he replaced the air vent thing to the kitchen sink drain, and it didn't do it again for a couple days, then started back up
, first the kitchen sink would gurgle, then later when my son took a bath and use the toilet shortly after and when he flushed it overflowed, and we noticed the tub didn't drain, plunging didn't help any, and it randomly drained by its self,
not sure what could be causing this problem, since it has drained its self the toilet keeps gurgling, and we ran the tub to see if it would drain and it did but then the toilet started gurgling again.
Also have high windy weather
On 2017-02-03 by Sherri
I have an older single wide mobile home and as I sit here I can hear water going through my pipes like it's pouring but I don't have any water turned on nor have I all day long. Why is this
On 2017-01-15 by (mod) re: plumbing noises from the toilet sound like it is self-flushing
Even changing a toilet flapper valve does not necessarily guarantee that you have fixed a slow, subtle leak out of the tank into the toilet bowl - that will ultimately lead to a minor self-flush. That's because the seal of the flapper to the valve base may still be poor unless the entire assembly is replaced. You're just replacing the flapper itself, not the seat to which it must seal.
Two things to try: dark food coloring (or septic dye) in the toilet tank may show up a leak in colour after a time. Or buy a new toilet fill valve from Fluidmaster - the model that includes a new feature: the valve will not drop and re-fill the tank if the tank is leaking. It only re-fills the tank in response to movement of the flush lever.
With that valve in place, if the tank is leaking it will indeed slowly leak out, but when you next check the toilet you'll find the tank low or empty.
Look for the Fluidmaster 400LSR Universal Fill Valve with Leak Guard.
InspectAPedia is an independent publisher of building, environmental, and forensic inspection, diagnosis, and repair information provided free to the public - we have no business nor financial connection with any manufacturer or service provider discussed at our website.
On 2017-01-15 by Help please !
House is 8 yrs old. On septic. We have two bathrooms. The one adjoining our bedroom (used the least) which is at the end of the house occasionally sounds like it tries to do a minor flush. I was thinking possible ball cock assembly or flapper
. The flapper has been changed a few times. Not the assembly. Nor has the septic been emptied as just my husband and I. What's weird is that sometimes...days on end.... when ever water is run at any point in the house even if that particular drain where the water is run is "closed off" at the time, when the water is turned off, it sounds in this one toilet like water is sloshing against the side.
I am so at a loss and quite worried as the inspector told our Government builders that if they ever used that Plummer again, he'd never inspect another of their houses.
Though he let ours through. Ohhh the troubles we've had. Shiver, shiver. I mean Who puts overhead plumbing in the walls and then runs outer wall insulation beneath the pipes instead of outside of them. That give you an idea of why I'm soooo worried ?
Though I will try to find your site again, is there anyway please that you could copy your answer to my email ??? PLEASE !! firstname.lastname@example.org Thank you. Am disabled so monies are snug. Maybe a pro can help us pinpoint the issue and still keep an arm if not a leg. Thanks again. :). Steff
On 2013-01-11 by E Wayne Rouse
I had the septic tank pumped recently. Now, when the outside air compressor comes on, I get a loud continuous thump from one sink in the bathroom. No other sinks make a noise. Occasionally, the toilet backs up, but it is not making any noise, and is flushing normally now. The thumping will cause the stopper to vibrate. Do you have any idea what I should do, or why it just started?
On 2013-01-09 by Help!:) - Every 2 seconds, "donk"
We are in a new home, so a new septic tank system. Been here two years now. It's a pump system into a mound it's been very very rainy, fromVanvouver. Anyway the tank outside is making a banging noise.
Every 2 seconds, "donk" loud enough that we heard it inside. The alarm on the pump has not gone off yet this banging noise can not be good. It's almost like a pump is going off with nothing inside. ... Like its lacking water.
On 2013-01-05 by Ellen
When it rains and when tub drains I then hear in the other bathroom the toilet seems to flush or water running in pipes. Or on its own the sound happens in the middle of the night What causes this?
On 2012-12-29 by Susan
We live in an apartment and can hear a glug glug glug noise in the wall between our apartment and the neighbor next door to us. We share a wall. Her bathroom is in the area we are hearing the noise.
Her unit and our unit are a bit staggered, so our bathrooms are not in the same places. Our kitchen wall is on the other side of her bathroom. So we are hearing this sound come and go constantly.
We will be sitting in our apartment and hear this glug glug glug noise for about 1-2 minutes and by the time we figure out exactly where it's coming from it stops. Then an hour later it's doing it again.
The noise is getting louder and louder. Any idea what this could be? I'm inclined to think it's an issue with her drain. Thankfully we don't share drains. our units have separate main drains that meat up in the back yard behind the building. (I know since I used to be an onsite manager).
On 2012-11-25 by (mod) -
Sewer gases may come up from the sink drain and the drain may be noisy because you have no working plumbing vent
On 2012-11-24 2 by trevor
my sink makes farting noises, what is it? why is it doing this? and it smells like fart gas HELP!
On 2012-11-23 by (mod) -
Often when we encounter the situation you describe the problem is a blocked or otherwise defective plumbing vent. If sufficient air cannot enter the drain line through the vent stack to satisfy the negative pressure in the drain as a surge of water flows through it, the suction created draws air into the drain through nearby traps, causing the sound you describe.
On 2012-11-22 by Jasen
also.... on that last question I noticed that my voice recognition on my phone is translating "and the" 2 in the :)
On 2012-11-22 1 by gurgle and draining sound coming
so here's my question, anytime I flush my master bath toilet I hear the flushing/gurgle coming from my jacuzzi overflow. when I run water down the drain of 1 of my master sinks I hear the water draining in the tub overflow.
when other toilets on the second and first floors are flushed I also sometimes hear it in the overflow. I don't think that I have ever heard it when I use the other sink in my master bath.
I do not seem to have any slow drains in the house. there appear to be at least four vent stacks on my roof 1 of which is a large.
Home is about 4500 square feet 2 floors in the basement with 2 bathrooms on the second floor in the laundry room 1 powder room on the first floor and the kitchen and 1 bathroom in the basement. interestingly enough it looks like the kitchen sink in the bathroom sink in the basement both have those cheater valves attached. home is only about 16 years old
On 2012-11-03 04:27:42.455876 by Richard A
I have a basement floor drain near washer that started to gurgle and bubble when clothes washer drains water. I noticed water level in drain was low which was not the case before. I can fill water in it and it does not overflow so I assume no blockage and I snaked it a couple months back.
Now the gurgle stopped after I filled drain whole back full of water. The drain for washer and drain in floor are same smaller diamater so I think they are connected before the main sewer drain.
No toilets or sinks gurgle and drain seems to only gurgle when laundry was done. Now that it stopped gurgling was this just because water level was lower than pipe at bend and allowed air to push through?
On 2012-10-17 00:16:24.879838 by (mod) -
If the basement drain never gave those problems before i suspect that either it was blocked or not connected to the main drain that was recently repaired, or during repair we lost a connection to a plumbing vent, or previously the floor drain was indeed drawing air in when the main drain was in use but was dry )no gurgling), or, another possibility is that your repair has lest a partial drain blockage downstream.
See if youncan have the drain system checked by camera.
On 2012-10-17 by (mod) - look for a shared drain or vent line
Debbie, look for evidence that your flat shares a drain or vent with another
On 2012-10-16 by Tim
We just had exterior plumbing work done on the sewer line between the house and the city main. Our basement floor drain is now wicking/siphoning/emptying and the smell of the CIPPs liner and sewer is coming into the house. I have done a brief check for causes of the emptying, but if you have any suggestions... thanks in advance
On 2012-09-29 by Debbie C
I also meant to point out I have only owned this property for 2 months, and the noise has become considerably more evident over this period so I assume it was there before. It was previously a rental property, so nobody had mentioned these issues to me at time of purchase.
Thanks for your message. The bath is gurgling without any taps run/toilet flusing etc in my property a lot more regularly now, so I'm not sure what to try in terms of checking for clogs?
Would you recommend either high strength cleaning agent down the plugholes, or snaking the bath drain perhaps?
If its any help, I have been informed that the bath drain is actually lower than the toile waste drain, so I don't know if that may be something to do with the noise? Just keen to make it stop now! :(
On 2012-09-28 by (mod) -
It sounds as if you may be describing a partly blocked drain or vent. Ask your plumber to check those.
On 2012-09-28 0 by (mod) -
the plumber had a good suggestion. To diagnose further, consider that as the noise is new we shouldnaskmwhat may have changed. A clog, for example wouldnbe a change. If the problem were due to originalndesign or installation the symptoms ought to have been present since the time of construction.
On 2012-09-21 by Debbie C, UK
I live on the 3rd floor of an apartment building in the UK. Whenever I use a toilet cleaning product, and flush away, the bubbles in the toilet bowl seems to cause the bath drain to gurgle loudly.
I spoke with a plumber who advised if it only occurs in this instance it is likely down to an anti-vac valve having been fitted, so left it at that. This morning however, the bath made the same noise although the toilet in my property was not flushed, so I can only assume was caused by a neighbour or flat above/below flushing their toilet
I then flushed mine twice (with no waste or cleaning products in) just to see if the flushing action caused the noise again, which it did - 3 times - so I am now concerned that this is maybe a fault with stack vent pipe or something in the building itself, rather than limited to my property.
Any help will be greatly appreciated.
On 2012-09-21 by Sharon
We live in a 20 yr old 2-story colonial with walk-out basement. Recently, our upstairs bathroom sink began emitting a stinky odor from the sink. I used drain cleaner several times but the smell remains.
A bit more recently, we began hearing a glub-glub sound in the powder room pipes when running the water in our kitchen (which is next to powder room). We only hear the sound when the water is run longer than 20 seconds or so.
Are the two connected? What needs to de done?
On 2012-09-16 by (mod) - unsuccessful effort to clear blocked drain
It sounds as if you are not actually reaching and clearing the drain blockage. For example if a sewer line is partly collapsed, the partial obstruction can cause solids to back up at that point; plunging or using other means such as a pneumatic drain blockage clearing tool can push the waste past the pipe damage but that point quickly clogs up again.
An experienced drain cleaner using a rotating snake can sometimes feel an obstruction or break in the sewer line, or s/he may pull out tree roots - both indications that excavation and line repair are needed. Or you could get lucky and clear a blockage that stays clear for a time.
On 2012-09-16 by joe b
i have 3 bathrooms two on the top floor one in the basement the one in the basement overflows when i plunge in it eventually goes down but then again fills up and very slowly drains also i hear gurgling sounds bubking sounds could my main drain need to be cleaned out or is it poor ventalation there is no smell
On 2012-09-06 2 by (mod) -
to unclog a pipe yourself, presuming we're talking about a drain pipe, follow instructions that start at
CLOGGED DRAIN DIAGNOSIS & REPAIR (links found at the INDEX to RELATED ARTICLES near the end of this page) - try a toilet plunger first.
On 2012-09-06 by (mod) - I can hear noises in the bathroom
It sounds pretty baffling, I agree; If close under the floor tile in the bath you describe there is a heating pipe or hot water pipe through which hot water has been flowing that could explain the warm tiles - or do you have radiant heat flooring?
But FIRST, check for a leak in the hot water piping in the area you desctibe - inspect that bath floor from below, looking for signs of a leak in a hot water pipe.
I'm not clear on a likely link between plumbing noises elsewhere in the house and warm bathroom floor tiles.
On 2012-09-05 by sandra
I can hear noises in the bathroom as if the water is on somewhere else in the house. At the same time, the tile feels hot to the touch in the same bathroom.
On 2012-08-17 by Heather
How do I unclog a pipe myself?
On 2012-06-20 by (mod) -
Rick, I'd try using a mechanics' stethoscope or a similar device (Radio Shack) to see if you can zero in on (and photograph for us) just what you find. It could be a loose pipe mount., I wouldn't expect thermal movement alone, in a drain line, to explain this tapping sound.
Also, is there a check valve anywhere in the drain system? Could that be making the noise?
On 2012-06-20 0 by More on the "tapping" sound
Dan, Thanks for the reply. I tend to lean toward the latter, only because of the sound it makes. Sometimes (but not always), it will occur after the first person takes a shower in the morning.
That didn't happen today, but it did happen after my wife did a load of laundry. The sound is very rapid (about 5 per second), and above the master bathroom it literally sounds like someone is shaking the pipe back and forth.
On 2012-06-18 by (mod) - tapping noise in drains
a "tapping noise" coming from a drain line is often a drip - water droplets fall down a vertical section of vent or drain piping until they hit a bend or elbow where they can make a smack or tap noise.
See if you can track the tapping noise to use of certain plumbing fixtures - for example, a long hot shower taken in cold weather may lead to condensation inside the vent pipe as it passes through a cool attic. Also check for dripping faucets and running toilets that send a slow leak down a drain line.
Another source of "tapping" sounds we find in both supply and drain piping can be due to thermal movement of the pipes as temperatures change. Sound isolating fittings or more clearance at openings for pipes can cure that trouble.
On 2012-06-15 by Rick Bolan
I have an intermittent "tapping" sound that I can hear in the ceiling of my main bathroom, which can be heard very clearly in the drains of the kitchen sink
. The area of the ceiling is where a large drain vent pipe is located, and the kitchen sink is on the other end of the house. It seems to come back every week or so, and it continues on and off for maybe a 1/2 hour.
Initially I thought we had an animal in the attic, but there are no signs of that, and the sound is too "rythmic" to be an animal. It happens at no particular time of day, and doesn't seem to correlate with any large water use. Furthermore, all the drains in the house seem to work perfectly, especially the kitchen sin
k. I'd call a plumber in, but I can't predict or control when it's going to occur.
Any ideaa? It sounds almost like someone's upstairs shaking the vent pipe back and forth.
On 2012-06-14 19:29:44.363408 by (mod) -
Wendy, thanks for the question, but I just don't know what a steaming noise sounds like - do you mean hissing? Steam, produced by boiling water, is not itself a sound. As you hear the noise at drains, its a plumbing question not a furnace question.
On 2012-06-14 by wendy - steaming nooise at drains
my drains are making a steaming noise (best way i can describe it) i hearing it in all the drains (sinks, shower,etc) in the basement it sounds like it coming from a part of the furnace the humidifier...any suggestions as to whats wrong??? who do i call a plumber or some one for the furnace???
On 2012-05-31 by (mod) -
Trish: loud humming is not a sound I've found traced to drain piping, but the fact that you hear it increase when a fixture is used suggests to me, with so little information, that perhaps there is a pump involved in your drain or sewer piping? If so check for pump noise being transmitted through piping. The fact that you hear the humming when drains are not being used argues in the opposite direction, but if it's from a drain pump it may not be activated until a reservoir is filled to an action level.
In sum, accurate tracing of the sound to its source may be aided by more recording of times of occurrence, and observation of what other equipment may be operating at that time, or even wind, insect, or animal activity.
On 2012-05-31 by (mod) - air conditioner drain noises
Frank, regarding air conditioner drainage and pumping and drain noises: an A/C condensate line usually has a trap right at the cooling unit, then slopes continuously to its drain point - in your case a sump. If you can trace the sound to that drain system I'd look for a partial blockage in the drain piping.
I'm unclear on what you mean by water heater drain pans - perhaps you mean a pan under a water heater intended to catch a leak and prevent floor damage? That pan is piped to a drain? If that drain is a building drain and it's gurgling it suggests a partial blockage further into the main building drain piping system.
On 2012-05-31 by Trish
having problems with Loud humming noise in house located in bathroom - happens at night when the sink has not been used or the toilet has been flushed can hear this all though the house for hours on end. and gets worse if any fixture is used.
Plumbing is all new installed 3 years ago. Plumbers say no toilet leak and no leaks in the system and it is working as it should. had all vents spray jetted and flushed out and still had the noice that evening - City has ben out and replaced thier meter and still noise.
Sewer contractor after scoping entire sewer line that it is old and should be replaced but would not cause this noise...I am at my whits end and am getting no concrete answers as to how to fix this...but have spent a lot of money and gotten no where....any ideas
On 2012-05-30 by Frank
I live in a 7 story condo. Last year the association installed a outside sump to curtail flooding that was supposedly caused by the air condition drainage.
The sump, as explained to me was connected to only three unit stacks, e.g. units C, D, & E. In the last two to three months several neighbors have noticed a sort of knocking, gurgling sound coming from the line that serves the drain pan for the water heater, which I assume is also connected behind walls to the line that the air condition drainage for all units.
Maintenance people and on site manager say it isn't the sump! If water is poured into the drip line it does evacuate with no problems. What do you think? Sounds like something sucking air.
On 2012-05-29 by (mod) - water supply pipe noise may suddenly appear, in the form of running water,
A water supply pipe noise may suddenly appear, in the form of running water, might be traced to a lost or loose pipe support, insulation that has been removed or become wet (conducting more sound), or noticing a noise that actually was present before. Often when we first notice something we are sure it's new when in fact it may not be in some cases.
If the noise is in drain piping, your system may have developed a partial drain or vent blockage, leading to a new gurgling sound that was not there before.
On 2012-05-29 by (mod) -
Liam, check for a partially blocked drain or vent pipe.
On 2012-05-20 by deene
recently I'm hearing a noise in my walls whenever water is running upstairs and I'm downstairs. It can be a toilet flushing, the shower running or the washer running. I've never been able to hear it before and there haven't been any plumbing changes. What might be causing it?
On 2012-04-20 by (mod) -
I don't have a clear understanding of your question: a self-flushing toilet? The only versions of that I've seen use an IR sensor and are in public restrooms. I suspect you have a bad flush valve.
If you mean you hear flushing water through the drain pipes but no water is being run in that bathroom, then clearly you've got water coming from somewhere else - perhaps a higher bathroom or nearby plumbing fixture? With so little information I can't diagnose it.
On 2012-04-18 2 by Anonymous
My downstairs bathroom will flush every 5 minutes without using the toilet. Flushing sound is coming from the piping. The home is over 60 years old with copper piping. What is causing this noise?
On 2012-04-17 0 by (mod) - gurgling noise that comes from all of my drains
Chris gurgling drains can mean a blocked vent or a partial drain blockage - as you've been exploring. The duration of the gurgling sound, if it's a blockage or a vent problem, varies by the amount of wastewater being sent down the drain. The toilet doesn't gurgle because it's in a sense self-venting - it draws air into the toilet bowl and drain during the flush cycle.
You can add a vacuum breaker "anti-siphon" device as a diagnostic - that will help only if the problem is inadequate venting or a blocked vent.
On 2012-04-13 2 by Chris R. Stevens
I have a gurgling noise that comes from all of my drains except the toilet. I have tried to auger all of the drains to no avail. The gurgling is loud and only lasted about 30 seconds. Now it is slower and last about 2 minutes or longer.
Th e house was built in the 30's and has only one bathroom on the main floor and a sink and drain in the basement. I have been told that I should add an anti siphon trap as a remedy. If that is the problem where is it installed?
On 2012-04-07 by (mod) - hissing at a tub drain
Ted, hissing at a tub drain is not a sound I've come across, but I still suspect it might be a combination of a partial clog and an incomplete plumbing vent system - it sounds a bit fantastic but if a lower drain has water running through it and needs to pull air into the DWV system, and if that air is blocked from the vent piping, air might get sucked into the drain from any other plumbing fixture.
We can get past this arm-waving speculation with a test: try filling the un-used tub drain with water - just to fill the trap. Then run water or flush toilets in baths on the lower floors or at other fixtures nearby. Listen at the (rarely-used) tub drain. Do you hear gurgling or bubbling?
Keep us posted - it'll help other readers and might also permit a smarter comment.
On 2012-03-26 by Ted Kierzyk
Got a question for you. Just started hearing a hissing noise coming from the master bath tub drain this morning.
This tub is rarely used and we have a septic system. No city drain. Any ideas what this might be & should I act quickly and get a plumber out there today?
Thanks in advance for your prompt response.
On 2012-02-28 by Judy Baca
I have a knocking noise in one of the sinks in my bathroom whenever the heater comes on. It is a heat pump. Can you give me any clues as to why?
we had yhe tank pumped but we still here this noise when the toilet is flosh
On 2012-02-07 by (mod) - signs of inadequate drain venting include noises
The noise you describe is often caused by either inadequate drain venting (or a blocked vent) or by a partially clogged main building drain. In the second case, water runs down the drain until it hits the obstruction then slows and "gurgles" as it makes its way through the partial blockage.
Wade: there may be another cause but I've seen the bubbling toilet drain behavior you describe when there was inadequate venting and on occasion in response to a blocked drain. If you're pretty sure the vent is ok and if none of the drains in the same bath ever seem slow or blocked,
I suppose it could also be an artifact of the particular toilet tank and flush valve. Take off the toilet tank lid and look into the tank during flush - is there a lot of agitation of the flush water mixing air into the system as water leaves the tank and enters the bowl? (It's cold water, not hot, right??)
On 2012-02-04 by Mark
After running the water in our bathroom sink, the water drains out completely, then a couple seconds later, we hear, "glub, glub, glub." It lasts only a couple seconds and is gone. The bathroom is on the ground level, and we have a finished basement, if that means anything.
On 2012-02-01 by Wade
When I flush my old American Standard toilet the bottom of the bowl at the beginning of the flush lets a couple of air bubbles up. It does this every time, all drains seem to work and no other problems than it just seems wrong.
What is with the air bubbles at the very bottom of the bowl on the front side of the toilet. Please solve this mystery nobody else can and it is only when I flush. We flush and listen for sucking of other drain pipes to see if that is a clue the main stack vent is plugged but everything seems fine. Help !
On 2012-01-23 03:19:48.853998 by Joe
When the second floor toilet is flushed, a loud almost grinding or whining noise can be heard in plumbing -coming from somewhere between basement and second level.
Nose is delayed by about 20 seconds after flushing, and lasts about 10-15 seconds. Unsure of cause, just started. In freezing climate, will head to roof to check vent as a start - any advice?
On 2012-01-06 by (mod) - clogged drains and glub glub sounds,
Mike: re clogged drains and glub glub sounds, I've posted our discussion in the FAQs above. Take a look at CLOGGED DRAIN DIAGNOSIS & REPAIR (links found at the INDEX to RELATED ARTICLES near the end of this page) for suggestions on how to proceed.
On 2012-01-06 by (mod) -
Louis, I've moved our discussion of noise complaints around a V-200 anti-siphon valve up to the FAQs section of the plumbing drain noise article just above. Further questions & comments are welcome.
On 2012-01-04 1 by (mod) -
Presuming that there are normal distances between your patio and the neighbor's plumbing vent roof pipe, what you describe is unusual. I wonder if perhaps the neighbor has
- a problem with their vent system leading to gurgling?
- a new high velocity low-water using flush toilet?
You might ask the neighbor if flush noise is a problem inside their own home, or if there is a drain problem - if the answer is no to both cases, ... well I've asked for additional thoughts from our noise and sound expert and we'll follow-up here.
On 2012-01-04 by Bonnie
We have a covered patio that faces the side of our neighbors house.
We can hear his toilet flush through the vent pipe on his roof. Is that normal? We have never noticed it in other houses we have lived in where our outside space was in close proximity to our neighbors bathroom vent pipe. It is so annoying and embarrassing when we are outside. Is there anything we can have our neighbor do to eliminate the noise? Thanks, Bonnie
Continue reading at PLUMBING DRAIN NOISE REPAIR or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES below.
Or see CLOGGED DRAIN DIAGNOSIS & REPAIR - clogged drains may gurgle or burp
Or see PLUMBING VENT NOISE - since vent problems can cause gurgling at drain lines
Or see this
Or use the SEARCH BOX found below to Ask a Question or Search InspectApedia
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website