HEAT PUMP COP - CONTENTS: Definition, sources of variation in heat pump operating efficiency & cost. Definition of COP for heat pumps. Definition & explanation of the balance point in a heat pump COP. How to adjust heat pump electricity costs to include the effects of variations in outdoor temperature
POST a QUESTION or READ FAQs about the definition of heat pump COP and how to calculate true electricity costs when using a heat pump system
InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Heat pump COP, definitions, efficiency, true electricity cost calculations. This article defines heat pump COP (coefficient of performance) and explains why the operating efficiency of heat pumps varies as a function of outdoor temperature. We include a table of factors used to convert electricity costs to true electricity costs as a function of outdoor degree days in the heating season - a calculation that makes comparison of heat pump operating costs with those of other heating methods much more accurate. Illustration at page top provided by Carson Dunlop Associates.
What is the COP or Coefficient of Performance of Heat Pumps?
The COP or coefficient of performance describes the ability of a heat pump to extract heat from outdoor air down to some low temperature, typically 25 degF. for modern equipment. The COP determines how effective a heat pump can be at providing heat during cool or cold weather.
The COP or co-efficient of performance for a heat pump can be expressed as a curve showing energy consumed to operate the equipment versus the amount of heat energy provided to the building.
Because COP curves show that we cannot continue to make effective use of a heat pump at very low or very cold outdoor temperatures, a backup heating system is required where heat pumps are installed in cold climates.
[Click any image to see an enlarged version and to read details.]
Watch out: As we explain in details at HEAT PUMPS, GROUNDWATER, you can't tell which COP and EER measurement for groundwater based heat pump systems is "right" without additional data describing the testing conditions.
The balance point in a COP curve for a heat pump describes the point beyond which it is not efficient to continue to run the equipment to try to heat a building - because we are obtaining less heat energy to put into the building than the energy we are using to operate the equipment.
Where a heat pump is used to provide part of the building's heat requirements, the efficiency of the air-to-air heat pump will be less at lower temperatures.
Spies (1971, 1977)  notes that heat pump efficiency when outdoor air is warm is quite different from at cold temperatures, making its use of electricity more complex.
The coefficient of utilization may be as high as 3.0, falling to 1.0 as outdoor temperature approaches 10 degF. In 1971 when Spies wrote that note for the Small Homes Council, few heat pumps worked at temperatures that low, Also that this was in 1971, newer equipment is capable of efficient heat extraction from colder air. Spies provided a calculation to transfer heat pump efficiency or COP into electrical costs when comparing heating fuel type cost alternatives:
Table of Electricity Cost Divisors for Heat Pump Operating Cost vs Degree Days - Outdoor Temperature
Degree Days for Your Location
Electricity Price Divisor
8000 degree-day heating season
6000 degree-day heating season
4000 degree-day heating season
Henry Spies, "Fuels & Burners", Small Homes Council - Building Research Council Circular Series #G3.5, 1971. 1977
Example: If you live in a climate in which the average number of degree days in the heating season is 4000, then to compare heat pump operating costs (using electricity) to other fuels and heating methods,
divide your current electricity cost (say 5 cents per kwh) by 2.2.
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
 Thanks also to Alan Carson, Carson Dunlop, Associates, Toronto, for technical critique and for providing a copy of Carson Dunlop Weldon & Associates Technical Reference Guide to manufacturer's model and serial number information for heating and cooling equipment ($69.00 U.S.).
 Henry Spies, "Fuels & Burners", Small Homes Council - Building Research Council Circular Series #G3.5, 1971. 1977 [copy on file as PDF]
Geothermal HVAC, [Amazon.com] Jay Egg & Brian Howard, McGraw-Hill Professional; ISBN-10: 0071746102, ISBN-13: 978-0071746106, quoting:
This definitive guide covers commercial and residential geothermal heating, ventilation, and air conditioning technologies and explains how to take advantage of their money- and energy-saving features. Geothermal HVAC: Green Heating and Cooling reviews the array of choices currently available, offers market values for systems based on varying options and conditions, and describes how to pair the best systems for each application and budget. Whether you're a contractor or a consumer, you'll find out what you need to know to implement a geothermal HVAC system in a retrofit or new construction project, and start benefiting from this sustainable, affordable technology.
Geothermal Heat Pumps is the most comprehensive guide to the selection, design and installation of geothermal heat pumps available. This leading manual presents the most recent information and market developments in order to put any installer, engineer or architect in the position to design, select and install a domestic geothermal heat pump system. Internationally respected expert Karl Ochsner presents the reasons to use heat pumps, introduces basic theory and reviews the wide variety of available heat pump models. Expertly reviewed and adapted for the most geographically broad application possible, the book offers the reader valuable tips for planning and system control using data, graphics and tables from a growing and innovative market.
Readers will learn how heat pumps are able to extract heat from relatively low temperature water circulating in ground loops and raise it to a temperature high enough to heat a home. They will also learn how to estimate the size of the heat pump required and the ground loop size as well for straight 2-pipe, 4-pipe, 6-pipe and Slinky loop configurations. This is important in order to verify that the installer correctly sizes the system. Both horizontal and vertical loop systems, for GX and DX, are covered.
Some of the technical issues that are addressed include: Loop water flow rates and Reynolds Number, heat of extraction/rejection, heating capacity, de-superheater setup, open-loop/closed-loop, SCW, pond loops, DX, Manual-J, COP. The final chapter consists of a set of flowcharts guiding the homeowner to ask the pertinent questions needed for a successful installation.
Books & Articles on Building & Environmental Inspection, Testing, Diagnosis, & Repair
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: firstname.lastname@example.org. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones