Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SEPTIC CARE INSTRUCTIONS
SEPTIC D-BOX INSPECTION
SEPTIC DRAINFIELD FAILURE DIAGNOSIS
SEPTIC DYE TEST PROCEDURE
SEPTIC FAILURE SIGNS
SEPTIC INSPECTION & TEST GUIDE
SEPTIC LIFE EXPECTANCY
SEPTIC SUPPLIES & PARTS
SEPTIC SYSTEM DESIGN ALTERNATIVES
SEPTIC SYSTEM DESIGN BASICS
SEPTIC SYSTEMS, HOME BUYERS GUIDE to
SEPTIC SYSTEM SAFETY WARNINGS
SEPTIC TREATMENTS & CHEMICALS
SEWAGE BACKUP PREVENTION
SEWAGE EJECTOR / GRINDER PUMPS
SEWER GAS ODORS
SEWER LINE REPLACEMENT
SINKHOLES, WARNING SIGNS
SOAKAWAY BED FAILURE DIAGNOSIS
SULPHUR & SEWER GAS SMELL SOURCES
TOILETS, INSPECT, INSTALL, REPAIR
TRAPS on PLUMBING FIXTURES
TREATMENTS & CHEMICALS, SEPTIC
VIDEO GUIDES: Septic Videos
WASHING MACHINES & SEPTIC SYSTEMS
WATER SOFTENERS & CONDITIONERS
WATER SUPPLY & DRAIN PIPING
WASTEWATER TREATMENT BASICS
WATER, WELLS, WATER TANKS: TESTING GUIDE
WINTERIZE A BUILDING
Guide to septic tank baffles & tees: this document describes how to inspect the condition of septic tank baffles at the septic tank inlet baffle and septic tank outlet baffle ports. Septic tank baffles are a key component of septic tanks which prevent damage to the drainfield by reducing effluent agitation as sewage enters the septic tank, and by preventing solids from flowing out of the tank to the drainfield. If the septic tank baffles are damaged, missing, or were never provided in the first place, the life of the drain field or leach field will be seriously shortened. Inspecting concrete septic tanks is a key component in onsite wastewater disposal systems. See SEWAGE LEVELS in SEPTIC TANKS for details on normal and abnormal levels and what they mean. Our page top photo shows a typical concrete septic tank baffle at the inlet pipe. Steel septic tanks have a similar barrier installed. When repairing or installing a septic tank baffle or tee, to extend drainfield life see Using Septic Filters.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved.
If your septic tank baffles are damaged and need repair or replacement, see SEPTIC TANK TEES how to install septic tank tees when tank baffles are damaged or missing. It's an easy repair. We also recommend septic tank outlet filters installed at the tank outlet tee to extend the drainfield life. See Using Septic Filters.
In the sketch at left the inlet and outlet septic tank baffles or "tees" are shown in brown and light blue respectively. You can see that the inlet tank baffle or tee will direct incoming wastewater down into the tank (not zooming across a tank to rush to the outlet opening). Forcing the incoming sewage to make a right turn (down) also slows its impetus. This turn and downwards direction are even more critical in a one-compartment septic tank.
Image adapted from Alaska DEC  The dashed lines illustrate the liquid level (red) and the difference in elevation (green) between the inlet and outlet septic tank pipe connections. More about these measurements is at SEPTIC TANK TEES where we discuss repair procedures and backwards septic tanks.
You can see that both of these septic tank baffles or tank tees keep the floating scum and grease from blocking the septic tank inlet (at left) and importantly, the tee or baffle keeps the floating scum and grease from exiting the septic tank outlet (where it would clog the drainfield). If these components have been lost or damaged in your septic tank they need to be replaced or repaired, as we explain here.
This is a chapter of Septic Systems Inspection, Testing our online book about septic system inspection procedures, defects in onsite waste disposal systems, septic tank problems, septic drainfield problems, checklists of system components and things to ask. Readers of this page who discover that their septic tank baffles need repair should see Septic Tank Inlet and Outlet Tee Installation Details.
If at the septic tank outlet the baffles are damaged or missing, or if no replacement "tee" has been installed, you can be sure that sewage has been pushed into the drainfield or absorption system, reducing its future life by speeding soil clogging there.
If septic tank baffles are lost or damaged (rusted off on a steel tank or broken off on a concrete tank), they can be repaired or replaced. For example at a steel tank the contractor may simply insert a plastic piping "Tee" into the tank inlet or outlet to create a new baffle system.
Baffles in a septic tank are provided to keep solids and floating scum and grease inside the tank. Baffles are provided at both the inlet to the tank (from the building) and the outlet from the tank (to the absorption system). The steel septic tank shown above at left has a baffle that is rusted away at its top. On pumping this old steel septic tank one expects to see the baffle bottom has rusted off too. The home made septic tank shown above at right had no inlet baffle and a broken outlet baffle, factors in the rapid destruction of the leach field for this septic system.
Broken septic tank baffles or high sludge levels can cause solids to flow out of the tank and into the absorption system. The result is reduced absorption into surrounding soil and eventual failure of the system. Floating scum thickness and settled solids thickness can be measured through access ports into the tank or cesspool.
Our photo (left) shows an old steel septic tank with the baffle at the right side of the photo. Just touching the baffle with a tool showed us that it was rusted and collapsing. This septic tank was pumped out, filled-in, and abandoned. But had the owners intended to use it they'd have needed to excavate the tank to install a baffle. That procedure is described in detail at SEPTIC TANK TEES.
Finding solids at or covering the outlets or damaged baffles should result in report of a very questionable adsorption system and possible major repair cost.
Depending on how long the tank was used without good baffles, the volume of solids and grease that moved from the tank to the absorption system will have begun clogging soils there and will have reduced the future life expectancy of the absorption system.
Baffle damage and repair, or even a complete tank replacement when the absorption system has been left alone always lead the author to warn the building owner that the future life of the absorption system may be in doubt and that additional expense will be involved.
As we mentioned above, see SEPTIC TANK TEES for instructions on how to install septic tank tees when septic tank baffles are damaged or missing.
Inspecting for Septic Tank Baffle Overflow
You cannot see the entire condition of the septic tank baffle before the tank is pumped, but inspect the baffle tops for evidence of corrosion, damage, total absence, or of sewage flowing over the baffle top (an indication of excessive in-tank sewage levels). Photos of the septic tank baffles in a concrete tank, as seen from inside the septic tank are provided at "Septic Tank Pumping Procedure" for which we provide a link at "More Reading" below.
The sewage level inside a septic tank should always be several inches below the baffle top but within a right at at or just below the bottom of the tank inlet pipe. If sewage level is low inside a septic tank which is in use, it is almost certain that the tank has been damaged and is leaking into surrounding soil.
Septic tank maximum scum and sludge buildup prior to pump out, and instructions for measuring the floating scum layer thickness and settled sludge layer thickness in a septic tank are available at SEPTIC TANK PUMPING SCHEDULE. Also see MEASURE SCUM & SLUDGE for details of how we make these measurements.
Readers who discover that their septic tank baffles need repair should see SEPTIC TANK TEES: "Septic Tank Inlet and Outlet Tee Installation Details".
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the search box below to ask a question or to search the InspectApedia.com website.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.