Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AGE of WATER HEATERS
AIRBOUND HEAT SYSTEM REPAIR by WATER FEED VALVE
ALTERNATIVE HOT WATER SOURCES
ANODES & DIP TUBES on WATER HEATERS
ANTIFREEZE for BOILERS
ANTI SCALD VALVES
APPLIANCE EFFICIENCY RATINGS
AQUASTAT CONTROL Functions
BACKDRAFTING HEATING EQUIPMENT
BACKFLOW PREVENTER VALVE, HEATING SYS
BACKFLOW PREVENTER, HEATER WATER FEEDER
BACKUP HEAT for HEAT PUMPS
CARBON MONOXIDE - CO
CHECK VALVES, WATER SUPPLY
CHEMICAL CONTAMINANTS in WATER
CHIMNEY INSPECTION DIAGNOSIS REPAIR
CLOGGED DRAIN DIAGNOSIS & REPAIR
CLOGGED SUPPLY PIPING
CROSS CONNECTIONS, PLUMBING
DEBRIS in WATER SUPPLY, Water Heater
DRAIN a WATER HEATER TANK
ELECTRIC WATER HEATERS
FLOODED HEATING EQUIPMENT REPAIR
FLOODED WATER HEATER REPAIR
FREEZE-PROOF A BUILDING
FROST HEAVES, FOUNDATION, SLAB
GALVANIC SCALE & METAL CORROSION
GAS BURNER Flame & Noise Defects
GAS FIRED WATER HEATERS
GAS PIPING, VALVES, CONTROLS
HEAT TAPES, Heat, Insulation prevent Freeze-Up
HEATING COST FUEL & BTU Cost Table
HEATING COST SAVINGS METHODS
HOT WATER SUPPLY
HOT WATER IMPROVEMENTS
HOT WATER DELIVERY SPEED UP
HOT WATER EFFICIENCY IMPROVEMENT
HOT WATER PRESSURE EXPANSION RATE
HOT WATER PRESSURE LOSS
HOT WATER PROBLEM DIAGNOSIS
HOT WATER QUANTITY IMPROVEMENT
HYDROGEN SULFIDE GAS
INDIRECT FIRED WATER HEATERS
MANUALS & PARTS GUIDES - HVAC
MIXING / ANTI-SCALD VALVES
NO HEAT - NO HOT WATER: HEATER DIAGNOSIS
NOISE / SOUND DIAGNOSIS & CURE
NOISE CONTROL for HEATING SYSTEMS
NOISE, PLUMBING CHECKLIST
NOISE, WATER HEATER
ODORS GASES SMELLS, DIAGNOSIS & CURE
ODORS IN WATER
PIPING IN buildings, Clogs Leaks Types
PLASTIC HEATER VENT
PLUMBING FIXTURES, KITCHEN, BATH
PLUMBING VENT DEFECTS & NOISES
PUMPS, HEAT PUMPS
PUMPS, OIL BURNER
PUMPS, PONY PUMPS
PUMPS, SEPTIC PUMPS
PUMPS, SEWAGE EJECTOR / GRINDER PUMPS
PUMPS, SUMP PUMPS
PUMPS, WATER PUMPS
PUMPS, WATER REPAIR
RELIEF VALVE LEAKS
RELIEF VALVES - TP Valves on Boilers
RELIEF VALVES - STEAM TP VALVES
RELIEF VALVES - Water Heaters
RELIEF VALVES - Water Tanks
SAFETY, HEATING INSPECTION
SCALE REMOVAL, WATER HEATERS
SEWER GAS ODORS
SOLAR HOT WATER HEATERS
SOOT on OIL FIRED HEATING EQUIPMENT
SPILL SWITCHES - Flue Gas Detection
TANKLESS WATER HEATERS
THERMOSTATS, HEATING / COOLING
THERMOSTATS, WATER HEATER
TIMERS for ELECTRIC WATER HEATERS
WATER CONTAMINANT LEVELS
WATER HAMMER NOISE DIAGNOSE & CURE
WATER HEATER ALTERNATIVES
WATER HEATER ANODES, DIP TUBES
WATER HEATER AIR INLET
WATER HEATER DEBRIS FLUSH
WATER HEATER DRAIN PROCEDURE
WATER HEATER EFFICIENCY
WATER HEATER FLUSH PROCEDURE
WATER HEATER NOISES
WATER HEATER PROBLEM DIAGNOSIS
WATER HEATER PROPERTIES
WATER HEATER SCALE - De-Liming Procedure
WATER HEATER SCALE PREVENTION
WATER HEATER SAFETY
WATER HEATERS for HOME HEATING USE?
WATER ODORS, CAUSE CURE
WATER PIPES, Clogs Leaks Types
WATER PRESSURE & FLOW MEASUREMENT
WATER PRESSURE GAUGE ACCURACY
WATER PRESSURE LOSS DIAGNOSIS & REPAIR
WATER PRESSURE REDUCER / REGULATOR
WATER PRESSURE PUMP REPAIR GUIDE
WATER PUMPS, TANKS, TESTS, WELLS, REPAIRS
WATER PUMP REPAIR GUIDE
WATER QUALITY TESTS, CONTAMINANTS, TREATMENT
WATER QUANTITY IMPROVEMENT
WATER SOFTENERS & CONDITIONERS
WINTERIZE A BUILDING
Clogged tankless coils: here we explain how to correct clogging at the tankless coil in order to improve the hot water pressure, quantity, flow from a tankless coil used for making domestic hot water. We include a simple diagnostic procedure to find out if your bad hot water pressure is due to clogging in the hot water piping or in the tankless coil itself. If you need to improve the hot water temperature and flow from a tankless coil system that is not clogged, see Tankless Coil for Hot Water Increase.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved.
How to Check for and Correct Clogged Piping at a Hot Water Heater Tank or Clogged Tankless Coil to Improve Hot Water Pressure or Flow
Hot Water Heater Tank Clogging Diagnosis & Repair - Tankless Coil De-Liming Procedure Details
Accumulated debris in a water heater, and debris from a corroded or disintegrating hot water tank dip tube or hot water tank sacrificial anode can also block the hot water outlet opening, resulting in low hot water pressure in a building. See ANODES & DIP TUBES on WATER HEATERS
Clogged hot water supply piping:
Water supply pipes may be clogged at the water heater or at other locations, from minerals, soil, or other debris. See Water pipe clog diagnosis and WATER HEATER SCALE - De-Liming Procedure for diagnosis and repair procedures.
Tankless Coil Clogging Diagnosis & Repair - Removing Lime & Scale from a Tankless Coil Water Heater - also for Side-Arm Coils
Hot water pressure and hot water flow in a building may be poor even where a mixing valve has been installed. This condition could be due to poor overall building water pressure or due to clogged pipes.
If cold water pressure is good and hot water pressure is poor, the problem is not an overall building water pressure issue. There is a problem with the hot water system that needs to be found and corrected.
If hot water pressure is strong when the water is first turned on but flow quickly falls off to a weak hot water stream, it's likely that the hot water piping (or tankless coil) are clogged.
Often this repair involves using acid to try to remove minerals that are clogging hot water system piping or a tankless coil, or the tankless coil may need replacement.
Abandoning a tankless coil altogether: When we bought our house the tankless coil was almost totally clogged with minerals, and we figured that it wouldn't provide enough hot water anyway, so we abandoned it. In the photo at left you can see the round black tankless coil face, with two holes - where we removed the cold-water-in and hot-water-out pipes and simply abandoned the tankless coil.
A separate water heater was installed in our utility area. (We'd have preferred an indirect-fired water heater which is discussed later in this article but that's not what we got.)
Guide to Acid Flushing of Clogged Tankless Coils or Clogged Hot Water Piping
Photo at left: lime scale fragments collected from a water heater. Similar hard limescale forms inside of hot water pipes and particularly in tankless coils used to produce domestic hot water. [Click to enlarge any image]
The general procedure is the following:
Does acid flushing of water piping or tankless coils work?
Often an acid flush will indeed restore or improve water pressure and flow through previously-clogged building piping. But the process has these limitations:
Krappe described using an acid-resistant pump and tubing connected to fittings to circulate an acid-wash through scale-clogged copper piping back in 1940. Plumbers still use this method today. The apparatus must be designed to let the scale particles and gases escape. Plumbers may simply use an acid-proof pony pump and fittings to cycle the acid wash using a plastic bucket as the receiving sump.
Watch out: this is a dangerous procedure risking acid burns or other hazards. Don't try this procedure if you are not trained and equipped to do so.
But we have been informed by some plumbers that using acids to clean a tankless coil leave the coil internal surfaces etched and that the result can be faster scale formation than previously
See TANKLESS COILS for an explanation of how these water heaters work and why they clog up and how to stop clogging up the coil.
See Water pipe clog repair guide for a discussion of loss of water pressure due to clogged piping or clogged tankless coils.
At Larger Diameter Water Supply Piping we discuss the benefits of using larger diameter water supply piping both to improve water pressure and flow and also to delay the clogging of pipes due to minerals or rust.
How do we Prevent Tankless Coil Clogging Again in the Future?
Field Report: Two Extra Steps to Improve the Effectiveness of Tankless Coil De-Liming Procedure
Your information on how to remove scale in a tankless coil to improve hot water pressure and flow led to me doing this task myself. I am very mechanically inclined and rather technologically proficient but I still wanted to get an understanding of the processes.
I had a pump that would do the job but I was concerned about using an acid, even diluted.
I turned off the valves separating the tankless coil in my Burnham oil burner and luckily had tees in place already. All I had to do was get fittings for the garden hose adapters and screw them in place, I then connected the hoses to the pump and one to drain freely into my 5 gallon pail filled with about 2 gallons of water.
I then added a 28 ounce container of Lime-A-Way and started pumping. The water was nearly non-existent when I started and the pumps thermal overload went off giving me a break.
I did this pump on-thermal off routine about three times, each time letting the solution sit in the tankless coils for approximately a half hour. I was getting almost no improvement. I then decided to reverse the flow thinking what could be the harm. The pump started and the bursts of gray water were getting more and more frequent. After three more thermal overloads I was running freely. Success is at hand!
But wait! All this bragging of success has its downside. As best as I can remember this issue isn't covered anywhere on your site.
Flush Debris from Faucet Strainers & Valves after De-Liming Water Pipes or a Tankless Coil
What I found is that after the water flow had returned to normal I still had low flow after a few bursts in my faucets upstairs. I then removed the aerators and strainers from the faucets and all flow had finally returned!
It might be a good idea to add a step to your water pipe or tankless coil de-liming or de-scaling process to remove the strainers and aerators from their faucets before turning them all on to rinse the tankless coil and system.
Bernie Daraz, Newtown, CT
Watch out: using Lime-A-Way, EasyPaks®, or Jelmar CLR® ("stain removing" cleaners designed to remove rust, calcium or lime) and similar cleaners to remove the white mineral crust on exposed metal surfaces such as a stainless steel kitchen sink can leave a black stain that is difficult to remove. If you already have this problem, try using a nonabrasive cleaner designed for cleaning stainless steel surfaces, such as ScotchBrite™.
As we discussed beginning in the previous section of this article, there are several different hot water problems:
The articles listed below offer more details about steps one can take to increase hot water quantity, pressure, and flow in a building.
The topics discussed in this article address improving hot water flow and improving hot water total quantity.
The following articles discuss alternative ways to produce domestic hot water for washing and bathing.
Thanks to Carson Dunlop, a Toronto Home Inspection Firm and Home Inspection Educator, for permission to use sketches shown in this article. For an explanation of the role of boiler temperature in the rapid formation of lime and scale clogging in tankless coils used for domestic hot water production, see Water Heater Scale Prevention.
Readers should also see Water pipe clog diagnosis and Water pipe clog repair guide. Also see WATER PRESSURE LOSS DIAGNOSIS & REPAIR in a building and see MUNICIPAL WATER PRESSURE DIAGNOSIS or WELL WATER PRESSURE DIAGNOSISwhere we describe the effects of clogged piping on water flow and offer remedies for this problem. If only hot water pressure and flow are poor, also see CLOGGED SUPPLY PIPES, HOT WATER.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about how to un-block or de-clog a tankless coil used for making hot water.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.