Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AIR CONDITIONING & HEAT PUMP SYSTEMS
BACKDRAFTING HEATING EQUIPMENT
BACKUP HEAT for HEAT PUMPS
BANGING HEATING PIPES RADIATORS
BLOWER FAN OPERATION & TESTING
BOOKSTORE - InspectAPedia
BTU USAGE MONITORS
CARBON MONOXIDE - CO
CIRCULATOR PUMPS & RELAYS
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DIRECT VENTS / SIDE WALL VENTS
DRAFT REGULATOR, DAMPER, BOOSTER
DUCT SYSTEM & DUCT DEFECTS
ELECTRIC MOTOR DIAGNOSTIC GUIDE
FAN, AIR HANDLER BLOWER UNIT
FLOODED HEATING EQUIPMENT REPAIR
FLUE SIZE SPECIFICATIONS
GAS BURNER FLAME & NOISE DEFECTS
GAS PIPING, VALVES, CONTROLS
GEOTHERMAL HEATING SYSTEMS
HEAT PUMPS, DIAGNOSIS, REPAIR
HEATING COST SAVINGS METHODS
HEATING OIL PIPING TROUBLES
HEATING OIL TANKS
HEATING SYSTEM NOISES
HEATING SYSTEM TYPES
GAS LP & NATURAL GAS SAFETY HAZARDS
MANUALS & PARTS GUIDES - HVAC
MIXING / ANTI-SCALD VALVES
MOTOR OVERLOAD RESET SWITCH
NOISE, HEATING SYSTEMS
ODORS FROM HEATING SYSTEMS
OIL FILTERS on HEATING EQUIPMENT
OIL FILL PIPE LEAKS
OIL SPILL CLEANUP / PREVENTION
PLASTIC PLEXVENT ULTRAVENT RECALL
PUFFBACKS, OIL BURNER
RELIEF VALVE LEAKS
RESET SWITCH, HEATER PRIMARY CONTROL
RESET SWITCH, ELECTRIC MOTOR
RESET SWITCH, STACK RELAY
SAFETY, HEATING INSPECTION
SAFETY RECALLS CHIMNEYS VENTS HEATERS
SOLAR HEATING SYSTEM DESIGNS
SOOT on OIL FIRED HEATING EQUIPMENT
STEAM HEATING SYSTEMS
THERMOSTATS, HEATING / COOLING
VIDEO GUIDES: HEATING SYSTEMS
WINTERIZE A BUILDING
WOOD, COAL STOVES & FIREPLACES
WOOD STOVE SAFETY
ZONE VALVES, HEATING
This article describes the purpose and setting of tiny switches found inside of some room thermostats. These little slide or toggle switches may control the heating system on-off cycle rate or burner-on time in a manner similar to the heat anticipator feature found in other room thermostats.
Here we describe various types of internal or "hidden" switches found in some wall thermostats and in a table form we summarize their proper setting.
In most cases you can safely install a new room thermostat without worrying about these switches - just leave the switch or switches in the factory-set position. But in some circumstances setting the switches correctly may involve a change .
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Here we describe various types of internal or "hidden" switches found in some wall thermostats and in a table form we summarize their proper setting. In most cases you can safely install a new room thermostat without worrying about these switches - just leave the switch or switches in the factory-set position. But in some circumstances setting the switches correctly may involve a change .
At HEAT ANTICIPATOR Operation we explained that on some room thermostats internal switches are used to control the heating system on-off cycling rate, sensitivity, or fan functions in a manner that provides benefits similar to the heat anticipator found on other room thermostat devices.
Continue reading at THERMOSTAT SWITCHES, EXTERNAL or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References