InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
This article gives a definition of AFUE and explains AFUE (Annual Fuel Utilization Efficiency) or heating system efficiency ratings and numbers.
The articles at this website describe the basic components of a home heating system,
how to find the rated heating capacity of an heating system by examining various data tags and components, how to recognize common heating system operating or safety defects, and how to save money on home heating costs.
We also provide a MASTER INDEX to this topic, or you can try the page top or bottom SEARCH BOX as a quick way to find information you need.
How is heating boiler efficiency or economy measured? What does boiler AFUE mean?
How is heating boiler efficiency or economy measured? What does boiler AFUE mean?
In short, the AFUE (Annual Fuel Utilization Efficiency) tells you,
for each dollar you spend on energy for heating by gas, oil, or another fuel, just how much of your dollar shows up inside the occupied space of your building as heat.
Here's a very rough example: if the AFUE number for your heater is 80%, that means that for every dollar you spend on heat, twenty cents "goes up the chimney" or is lost in various other ways, and eighty cents of each heating dollar shows up in your occupied space as heat.
[Click to enlarge any image]
Each model of heating boiler or furnace is assigned an AFUE number. Our page top sketch of a high efficiency furnace is provided courtesy of Carson Dunlop Associates.
At left we illustrate a high efficiency gas furnace - expected to have a high AFUE number. Sketch courtesy of Carson Dunlop Associates.
AFUE is an abbreviation for Annual Fuel Utilization Efficiency. In short, the AFUE tells you, for each dollar you spend on energy for heating by gas, oil, or another fuel, just how much of your dollar shows up inside the occupied space of your building as heat. Higher AFUE is better.
If your boiler or furnace or steam boiler has an AFUE rating of 90, that means that for every dollar you spend on fuel, 90 cents worth of heat is delivered into your building. The remaining 10 cents is lost in inefficiency such as heat that escapes up the chimney along with the products of combustion.
How is the Efficiency of a Gas or Oil Fired Boiler Actually Measured?
The combustion efficiency of an oil or gas fired heater is in effect a measurement of how effectively the heating appliance is converting the chemical energy of its fuel (oil or gas boilers or oil, gas or electric furnaces) into heat. Combustion air, burner adjustments, temperatures and other factors in the heater's design determine the actual efficiency of its burner.
The output of these heating appliances will be in the form of heated air (furnaces), heated water (hydronic or "hot water" boilers), or steam (steam boilers).
Details of the test procedure used to determine AFUE for a heating appliance are specified in the U.S. by ASHRAE Standard 103 cited below.
You'll notice in ASHRAE 103 that the standard writers took care to note that the "factory" AFUE cannot be assumed to be the actual AFUE for a specific installation in the field.
But efficiency is usually measured as well in the field at installed heating appliances as a final step in the annual cleaning and tune-up of the heater. In our opinion this is likelty to be a more accurate measurement than the factory specified AFUE as it is measuring the actual heater in-situ, even though those results cannot be extended to other installations whose site conditions will be different.
A technician actually determines the combustion efficiency of the heater by using instruments to measure both the operating temperature (measured in the exhaust gases in the flue) and the carbon dioxide level (CO2) in the exhaust gas exiting the heater in the breech - an area in the flue vent connector between the surface of the the heater and the draft regulator (if one is present there). The heater has to have been on or operating long enough to have reached full operating temperature or to be in "steady state" condition.
at OIL BURNER CO2 TEST you can see an example of this procedure for oil burner fired heating appliances.
Watch out: do not make heating appliance measurements before the heater has been on long enough to have reached steady state; that's often about 5 minutes, and it's easy enough to determine by simply monitoring the flue temperature.
When the flue temperature stops increasing the heater is at steady state. This is critical because combustion will be incomplete and thus inefficient when the heating appliance and its combustion chamber have not reached full operating temperature.
Given the CO2 measurement the technician simply looks up the corresponding fuel efficiency number (a percentage) in a table for the fuel being used (oil or gas).
Details of this procedure and charts describing key relationships like the important effects of both inlet water temperature and return water temperature on the efficiency of a condensing boiler, were given by Durkin (2006).
Below in our citations the Cold Climate Housing Research Center has published an excellent article reviewing AFUE and how it is obtained and used for buildings in a cold climate.
Research & Standards on AFUE Definition, Measurement Standards, & Heating System Efficiency Measurements
The Cold Climate Housing Research Center is an industry-based nonprofit corporation created to facilitate the development, use, and testing of energy-efficient, durable, healthy, and cost-effective building technologies for people living in cold climates.
ANSI/ASHRAE Standard 103. (2013). Method of Testing for Annual Fuel Utilization Efficiency of Residential
Central Furnaces and Boilers. Atlanta: ANSI/ASHRAE. Website: http://spc103.ashraepcs.org/ Description: 1. PURPOSE: The purpose of this standard to provide procedures for determining the annual fuel utilization efficiency of residential central furnaces and boilers.
2.1 This standard includes: (a) a test method for cyclic and part-load performance, (b) methods for interpolating and extrapolating test data, and (c) calculation procedures for establishing seasonal performance.
2.2 This standard applies to central furnaces with inputs less than 225,000 Btu/h and boilers with inputs less than 300,000 Btu/h, having gas, oil or electric input, intended for use in residential applications. This standard also applies to furnaces contained within the same cabinet with central air conditioners that have rated cooling capacities of 65,000 Btu/h or less.
2.2.1 This standard applies to equipment that utilizes single-phase electric current or low-voltage DC current.
2.2.2 This standard covers the effectiveness of electrical/mechanical stack dampers only.
2.3 The test procedures are intended to be used to compare energy consumption measures of various furnace and boiler models. They are not intended to provide an absolute measure of performance in any specific installation configuration since the effects of heating system installation variables are not fully taken into account.
Butcher, T. (2011). Performance of Combination Hydronic Systems. ASHRAE Journal , 36-41.
Chi, J., & Kelly, G. (1978). A method for estimating the seasonal performance of residential gas and oil-fired
heating systems. ASHRAE Transactions 84 , 405-421.
Durkin, T. (2006). Boiler System Efficiency. ASHRAE Journal , 51-57.
"FURNACES & BOILERS, AFUE & EFFICIENCY SUGGESTIONS", [PDF] U.S. Department of Energy, Office of Energy Efficiency & Renewable Energy
1000 Independence Avenue, SW
Washington, DC 20585 USA, retrieved 2017/05/23, original source: https://energy.gov/energysaver/furnaces-and-boilers
What is the Reliability & Accuracy of Heating System Efficiency Ratings - AFUE?
AFUE is not the whole story of heating cost efficiency. A high-efficiency heating system that has not been cleaned and serviced may be running poorly and wasting money.
In fact, an 85% AFUE heating boiler that has not been cleaned might be running at an efficiency much lower, perhaps 65%.
Furthermore, if your building is drafty or poorly insulated, you may be delivering heat at high efficiency but losing it from the building much faster than necessary.
Really? Well while AFUE is important in comparing two heating appliances that use the same fuel, the cost of yoru fuel and the general efficiency range of your fuel choice (oil, gas, propane, wood, electric) has a greater effect on othe actual annual cost to heat your building than the heater's AFUE rating, and
These articles can help with a more complete approach to saving money on heat:
HEATING COST SAVINGS METHODS - what steps can we take to increase the efficiency of the heating system installed at a building and what are the priorities of steps to take to save on heating cost?
Adapted from Wikipedia, "Annual fuel utilization efficiency", retrieved 2017/05/23, original source: https://en.wikipedia.org/wiki/Annual_fuel_utilization_efficiency , Wikipedia provided background information about some AFUE topics discussed at this website provided.
Because Wikipedia and other website entries can be amended in real time, we cite the retrieval date of such citations and we do not assert that the information found there is always authoritative.
These Wikipedia general AFUE numbers do not distinguish between heat media (boiler vs furnace or water, steam, air) and do not reflect the particular AFUE that will be measured at a specific residential building's heating furnace or boiler.
The author [DF] has been able to raise the efficiency of a pre-1970 cast iron heating boiler from 60% up to 76% by installing a new high-speed oil burner and adjusting the burner mount location - photo shown here.
We replaced an old 1725 rpm burner with a high speed Beckett 3450 rpm oil burner and we moved the oil burner up to fire through the upper door of a cast iron heating boiler that had originally been coal fired and that was installed in this Poughkeepsie NY home in 1900.
A Guide to Residential Wood Heating [PDF] (2008 ed.), ISBN 978-0-660-19848-4, Canada Mortgage and Housing Corporation, ed. (2008) retrieved 2017/05/23, original source http://publications.gc.ca/collections/collection_2009/schl-cmhc/NH15-436-2008E.pdf
Other Heating System Performance Measurements & Standards
Also see our definition of HSPF, SEER, and other measurements found at SEER RATINGS & OTHER DEFINITIONS [live linke just below] or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES below.
Continue reading at APPLIANCE EFFICIENCY RATINGS or select a topic from closely-related articles below, or see our complete INDEX to RELATED ARTICLES below.
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: firstname.lastname@example.org. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones