Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ELECTRICAL INSPECTION, DIAGNOSIS, REPAIR
AFCIs ARC FAULT CIRCUIT INTERRUPTERS
ALUMINUM WIRING HAZARDS & REPAIRS
AMPS VOLTS DETERMINATION
AMPERAGE MEASUREMENT METHODS
APPLIANCE EFFICIENCY RATINGS
BACKUP ELECTRICAL GENERATORS
BACK-WIRED ELECTRICAL DEVICES
BOOKSTORE - ELECTRICAL
CADET & ENCORE HEATER RECALL
CHALLENGER ELECTRIC PANELS
CIRCUIT BREAKER SIZE for A/C or HEAT PUMP
Classified CIRCUIT BREAKER WARNING
CUTLER HAMMER PANEL FIRE
CORROSION in ELECTRICAL PANELS
DEFINITIONS of ELECTRICAL TERMS
DIRECTORY OF ELECTRICIANS
DMM Digital Multimeter HOW TO USE
ELECTRIC METERS & METER BASES
ELECTRIC MOTOR DIAGNOSTIC GUIDE
ELECTRIC MOTOR OVERLOAD RESET SWITCH
ELECTRIC PANEL AMPACITY
ELECTRIC PANEL INSPECTION
ELECTRIC PANEL MOISTURE
Electric Power Frequency Table
EMF RF FIELD & FREQUENCY DEFINITIONS
ELECTRICAL GROUND SYSTEM INSPECTION
ELECTRICAL SERVICE DROP
ELECTRICAL SERVICE ENTRY WIRING
EMF RF FIELD & FREQUENCY DEFINITIONS
FIRE SAFETY Checklist, CPSC
GFCI PROTECTION,Testing GFCIs AFCIs
HEATING COST FUEL & BTU COST TABLES
HEAT TAPE USAGE GUIDE
Hertz - Definitions of KHz MHz GHz THz
KNOB & TUBE WIRING
LIGHTING, EXTERIOR GUIDE
LIGHTING, INTERIOR GUIDE
LIGHTNING PROTECTION SYSTEMS
LOW VOLTAGE BUILDING WIRING
LOW VOLTAGE TRANSFORMER TEST
MAIN ELECTRICAL DISCONNECT
MAIN DISCONNECT AMPACITY
MOISTURE SOURCES in PANELS
MURRAY SIEMENS Recall
PHOTOVOLTAIC POWER SYSTEMS
PUSHMATIC - BULLDOG PANELS
REMOTE ELECTRIC POWER, PHOTOVOLTAIC
RUST in ELECTRICAL PANELS
SAFETY for ELECTRICAL INSPECTORS
SE CABLE SIZES vs AMPS
SIEMENS MURRAY Recall
THERMAL EXPANSION of HOT WATER
THERMAL EXPANSION of MATERIALS
UNDERGROUND SERVICE LATERALS
VOLTS / AMPS MEASUREMENT EQUIP
VOLTAGE MEASUREMENT METHODS
WIND TURBINES & LIGHTNING
ZINSCO SYLVANIA ELECTRICAL PANELS
How to strip insulation from electrical wires when wiring a light switch or electrical receptacle.
Here we explain how much insulation to remove and to avoid damaging the electrical wire when preparing wires for connections to receptacles or switches.
This article series describes how to choose, locate, and wire an electrical receptacle in a home. Electrical receptacles (also called electrical outlets or "plugs" or "sockets") are simple devices that are easy to install, but there are details to get right if you want to be safe.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
If the wire insulation is stripped the perfect amount then after it has been inserted into the clamp or wrapped around the screw you'll see that no wire insulation is under the connector itself, but little or no bare wire is exposed past the edges of the connector.
Above our white wire was stripped correctly - the stripped end was pushed into the clamp until it stopped, and the screw was tightened against bare copper, but just about 1/16" or less of bare copper shows above the screw (photo shown above left).
Our black wire was stripped too much (photo above-right) and some unnecessary bare copper remains exposed after the screw was tightened.
If you going to wrap the electrical wire around the terminal screw on the electrical receptacle (or a light switch terminal) you need to strip back a bit more than 1/2-inch in order to have enough copper to go around the screw leaving no insulation under the screw head when it is tightened.
Our photo (left) shows the strip gauge marked on the edge of our receptacle - those two parallel lines cast into the black plastic housing just below our stripped-back white wire.
This website provides information about a variety of electrical hazards in buildings, with articles focused on the inspection, detection, and reporting of electrical hazards and on proper electrical repair methods for unsafe electrical conditions. Critique and content suggestions are invited. Credit is given to content editors and contributors.
Nicks in Stripped Electrical Wires Make a Bad Connection & Risks Broken Wires
Don't damage electrical wires by nicking them: When installing, securing, or stripping insulation from wiring in order to make a connection, the wire and its insulation must not be nicked or damaged, as we show in the sketch at left, courtesy of Carson Dunlop Associates. Why?
The risk of breakage is increased at an electrical receptacle (compared with say a light fixture) because repeated insertion and removal of wall plugs from the receptacle device itself tend to jiggle the device around in its mount, moving the wires connected to it, flexing them, and breaking at nicks.
Typically the ground wire is bare of plastic insulation, but it may be necessary to remove paper around the wire before connecting it. We like to remove all of the paper around the ground wire rather than leave electro-kindling inside the junction box.
In our photo, left, I've pushed the paper off of the ground wire - but have not yet torn it away from the assembly.
If there is more than one feeder wire entering the electrical junction box then all of the grounds are connected together as well as being connected to the ground screw on the receptacle itself. Special crimp-on connectors are used by professionals to join multiple ground wires in the electrical box, but it is also permitted to use a twist-on connector (which takes more space).
If the junction box is plastic, you're done.
If the junction box is metal, a ground wire is also connected to the metal box using an approved grounding screw or clamp device to tie the wire end to the box.
Most metal electrical boxes have a threaded hole intended for use as a connection point for the ground wire connecting screw, as illustrated in our photograph (left).
Details about how to wire up an electrical receptacle are at CONNECTION DETAILS - where to connect black, white, red, green, ground wires.
Continue reading at TYPES of ELECTRICAL RECEPTACLES or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
Question: armor around wire through concrete?
I am running a new 15A outlet into the back of a bookcase in a 50 year old house with updated electrical. The wire runs out the back of the retrofit box and down through the concrete foundation into the crawlspace to a wire I plan to splice into. Do I need to put armor around the wire run through the foundation? It goes through open air for about 2 feet and there is no way to secure it to anything.
You need to look at the type and rating of the electrical wire to determine if it is permitted to bury it in concrete or not.
Question: how do I fix a stripped screw opening in an electrical box?
The little metal tabs to which the electrical outlet screws should mount have holes that have been stripped. Can I just use a sheet metal screw to hold the receptacles in place?
Reply: step by step tips for replacing a stripped electrical receptacle or switch box mounting screw