Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
Ask a Question or Search InspectAPedia
InspectAPedia ® Home
ELECTRICAL INSPECTION, DIAGNOSIS, REPAIR
AFCIs ARC FAULT CIRCUIT INTERRUPTERS
ALUMINUM WIRING HAZARDS & REPAIRS
AMPS VOLTS DETERMINATION
APPLIANCE EFFICIENCY RATINGS
BOOKSTORE - ELECTRICAL
Cadet & Encore Heater Recall
CIRCUIT BREAKER SIZE for A/C or HEAT PUMP
Classified CIRCUIT BREAKER WARNING
CUTLER HAMMER PANEL FIRE
CORROSION in ELECTRICAL PANELS
DEFINITIONS of ELECTRICAL TERMS
DIRECTORY OF ELECTRICIANS
DMM Digital Multimeter, How to Use
ELECTRIC METERS & METER BASES
ELECTRIC MOTOR DIAGNOSTIC GUIDE
ELECTRIC MOTOR OVERLOAD RESET SWITCH
ELECTRIC PANEL AMPACITY
ELECTRIC PANEL INSPECTION
ELECTRIC PANEL MOISTURE
Electric Power Frequency Table
EMF RF FIELD & FREQUENCY DEFINITIONS
ELECTRICAL GROUND SYSTEM INSPECTION
ELECTRICAL SERVICE DROP
ELECTRICAL SERVICE ENTRY WIRING
EMF RF FIELD & FREQUENCY DEFINITIONS
FIRE SAFETY Checklist, CPSC
GFCI PROTECTION,Testing GFCIs AFCIs
HEATING COST FUEL & BTU Cost Table
HEAT TAPE USAGE GUIDE
Hertz - Definitions of KHz MHz GHz THz
KNOB & TUBE WIRING
LIGHTING, EXTERIOR GUIDE
LIGHTING, INTERIOR GUIDE
LIGHTNING PROTECTION SYSTEMS
LOW VOLTAGE BUILDING WIRING
LOW VOLTAGE TRANSFORMER TEST
MAIN DISCONNECT AMPACITY
MOISTURE SOURCES in PANELS
MURRAY SIEMENS Recall
PHOTOVOLTAIC POWER SYSTEMS
PUSHMATIC - BULLDOG PANELS
REMOTE ELECTRIC POWER, PHOTOVOLTAIC
RUST in ELECTRICAL PANELS
SAFETY for ELECTRICAL INSPECTORS
SE CABLE SIZES vs AMPS
SIEMENS MURRAY Recall
THERMAL EXPANSION of HOT WATER
THERMAL EXPANSION of MATERIALS
UNDERGROUND SERVICE LATERALS
VOLTS / AMPS MEASUREMENT EQUIP
WIND TURBINES & LIGHTNING
ZINSCO SYLVANIA ELECTRICAL PANELS
Lost neutral or weak neutral wire electrical connections at a building: what can happen? This document describes a case history of loss of the neutral connection in an electrical panel combined with failure to isolate the neutral and ground buses leading to an electrical shock.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved. Author Daniel Friedman.
Case History of an Electrical Ground Failure - Loss of a Neutral Connection in an Electrical Sub Panel Badly Shocks a Homeowner
Question: What did all of these sub panel neutral and ground wire problems & electrical wiring errors mean?
When the air compressor motor was running it was producing a significant current on the compressor's neutral circuit.
The garage neutral circuit had no connection back to the main building (where it would have been connected to earth in the main panel, but because the owner had (improperly) bonded together the ground and neutral bus in his garage sub panel, the garage neutral circuit was indeed finding a path to earth through a small diameter (and thus overheated and dark) copper ground wire and a local grounding electrode.
Bud, a master electrician from Minnesota points out that in the 2005 NEC there are 2 ways to connect a subpanel in a detached garage. In both methods grounding electrode(s) are required at the garage.
Normally the neutral-to-ground bond is made in the main electrical panel and not in sub panels, lest grounding conductors end up carrying current during normal operations - a shock hazard. As Bud describes above, in the now obsolete, not allowed case, it was possible to wire a remote outbuilding sub panel as if it were a "main", with no ground returning to the actual remote main panel, and with a neutral-ground bond in the sub panel plus an effective local grounding electrode. We do not recommend this obsolete wiring approach. - Ed.
The problem in this case is the loss of the feeder neutral.
Summarizing some key observations in this lost neutral sub panel case:
Summarizing our conclusions (we will amend if with readers we develop a different analysis of this case):
A combination of missing main neutral in sub panel back to main panel, connecting neutral and ground buses in the sub panel, local ground at the sub panel, connection of metal work bench to panel ground bus, and modified 3-phase compressor in operation produced an electrically live workbench (owner was shocked), and conspired to visibly overheat grounding conductors, hot wires to the panel, panel bus behind the breakers, and grounding wire to the local electrode.
Additional photographs from this case are shown just below. Thanks to reader Randy Gardner for discussing this lost neutral case and opening an argument for clarification of just what was going on.
Below left: metal workbench that was connected to ground wire bus in the sub panel. Below right: overheated corroded main bus connections in the sub panel.
Below left: 3-phase compressor "re-wired" to run on 240V (we suspect that a 3rd leg was connected to a neutral or ground wire at this hookup. Below right: overheated wires in the sub panel at circuit breakers (we suspect these were powering the compressor motor).
Why Do Electrical Power Surges or Lightning Strike Current Go to Ground While Short Circuits Follow a Path to the Utility Ground?
Question: We were a little unclear as to why surges find their way to the local earth connection (higher resistance path) while in an emergency such as a short circuit hot to neutral or hot to ground wire, the current does not.
Answer: Bud continued this helpful explanation:
Question: Isn't it the case that current always prefers the path of least resistance and that the current can actually be calculated to flow on two (for example) different paths as a direct function of the relative resistance of each path?
Answer: Nicely stated, particularly the end.
And in the case of the ground fault tripping a breaker there will be some current through the earth, just like there is some normal neutral current through the earth. But the resistance of the service neutral is far lower than the earth.
The root causes of this electrical shock were:
Frequently Asked Questions (FAQs) about electrical neutral wiring inspection, troubleshooting, repairs
Questions & answers or comments about neutral wire troubleshooting: what can happen when the neutral connections are lost or weak at a building? .
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.