Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
CHIMNEY INSPECTION DIAGNOSIS REPAIR
BACKDRAFTING HEATING EQUIPMENT
CARBON MONOXIDE - CO
CHIMNEY COMPONENT DEFINITIONS
CHIMNEY FIRE ACTION / PREVENTION
COMBUSTION GASES & PARTICLE HAZARDS
COMBUSTION PRODUCTS & IAQ
FLAME COLOR, BLUE vs YELLOW COMBUSTION
HEATING SYSTEM INSPECTION
HOME HEATING SAFETY
ODORS & SMELLS DIAGNOSIS & CURE
SAFETY RECALLS CHIMNEYS VENTS HEATERS
STAIN DIAGNOSIS on BUILDING EXTERIORS
WOOD, COAL STOVES & FIREPLACES
WOOD STOVE SAFETY
This article describes a collapsing brick chimney and gives simple advice for immediate life-safety measures to be taken in the building. Readers should also see CHIMNEY COLLAPSE Risks, Repairs.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved.
Watch out: Chimneys with splitting or movement such as that shown in our photographs below should not be patched, repaired, or re-lined. Nor can this chimney be used safely, not even for a moment. The chimney structure, material, and probably its footings are or were inadequate and unsafe. A chimney tear-down and replacement are in order. In some cases by converting a heating system to a direct-vent flue it may be possible to cut the costs of this repair in half.
Inspect chimneys carefully throughout the building for evidence of holes, cracks, or damage, but pay special attention to brick chimneys that may split and actually break apart in their lowest sections.
We suspect that the combination of the heavy weight of a very tall brick masonry flue combined with the use of soft bricks and construction that used only a single brick width to form the thickness of the chimney caused the severe splitting of the brick masonry flue shown in these two basement photos.
This damage pattern is more likely to be found on single-wythe thick brick chimneys than on chimneys built with multiple thickness of bricks forming the chimney wall.
This chimney was in use and was very dangerous. The hazards of a split brick chimney include at least these:
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about splits and gaps in brick chimneys: evaluation, diagnosis, repair or replacement .
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.