Air Conditioning & Heat Pump Air Handler Cooling Coil Blockage
DIRTY COOLING COIL / EVAPORATOR COIL - CONTENTS:Dirty or blocked air conditioner cooling coils (evaporator coils), how to diagnose & repair. Other Causes of Blocked Air Conditioning Evaporator Coil or Reduced Air-flow
InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Cooling coil blockage by debris, damage, or ice - diagnosis & repair:
This air conditioning repair article discusses the problem of dirt or debris blockage of the air conditioning system's cooling coil or evaporator coil in an air conditioning system air handler,
how the dirt gets there, what problems it causes, how to clean a cooling coil (or evaporator coil), and how to prevent future dirt on the coil.
Blocked Cooling Coil: Air Conditioner Evaporator Coil Blocked by Debris
This photograph shows how easily debris can stick to and clog the inlet side of the cooling coil in an air conditioning system. This evaporator coil was nearly totally blocked with dust and debris.
How does this happen?
[Click to enlarge any image]
There was no air filter installed in the system. Ordinary house dust is comprised largely of fabric fibers and skin cells.
These and other debris in building dust such as soot and organic particles like pollen and mold spores all join to form a gray mat on the
fins of the cooling coil in an air handler.
Debris sticks particularly quickly to this surface because of the combination of close spacing of the cooling fins (about 1/16" apart) and the fact that condensate forming on the coil keeps the surface damp.
Here is a close up photograph showing how fibers in building dust readily cross the blades of the cooling coil and how the fibers themselves then collect smaller particles to rapidly block air flow across the coil. The same principles that make an air filter work can also clog the cooling coil of an air conditioning system.
As a cooling coil (or evaporator coil) in an air conditioner becomes blocked with dust and debris the air flow across the coil is reduced.
This reduced air flow (in cubic feet per minute or CFM)
across the coil means that the cooling capability of the whole air conditioning system is reduced.
What Else Causes a Blocked Air Conditioning Evaporator Coil or Reduced Air-flow Across the Coil?
Dirty air filter: can be mistaken for a blocked cooling coil. Always check your air filter first. Replace it if it's clogged and dirty and check the filter regularly.
See AIR HANDLER / BLOWER UNITS
Air Conditioner Evaporator Coil Frost or Ice Formation: When the coil becomes sufficiently blocked with debris as to slow down the air flow enough, the coil may actually become so cold that the condensate forming
on its surface freezes, completely blocking the coil.
That's because the rate of release of refrigerant into the evaporator coil was designed with an assumption of a sufficient volume of air moving across the coil to keep it from becoming too cold.
When the surface temperature of an air conditioning
cooling coil drops below 32 degF or 0 degC, condensate forming on the coil surface begins to freeze, leading to sometimes some pretty weird behavior of the cooling system as we discuss
at FROST BUILD-UP on AIR CONDITIONER COILS where we explain that there can be more than one reason that a cooling coil ices-up but none of those conditions is desirable.
Damaged air conditioner coil fins: can occur on both the evaporator (cooling) coil and the outside condensing coil.
See CONDENSING COIL REPAIR REPLACE for discussion of repairing bent or damaged coil fins. Only in extreme cases will fin damage be so severe that air flow across the cooling coil is severely blocked - enough to cause loss of function or coil icing.
Dirty air handler blower fan: see AIR HANDLER / BLOWER UNITS and its section titled DIRTY A/C BLOWERS This article describes the very significant reduction in airflow across a cooling coil that can occur if the squirrel cage fan blades are dirty on the blower fan in the air handler. A dirty blower fan can be the cause of reduced airflow across the cooling coil and can even lead to coil icing.
Air leaks or unnoticed duct openings: in the duct system can interfere with proper airflow through the duct system, reducing air delivery into the building, and can be mistaken for a blocked or dirty cooling coil. Details are
at DUCT SYSTEM & DUCT DEFECTS.
Air Conditioner or Heat Pump Cooling Coil Articles
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Mark Cramer Inspection Services Mark Cramer, Tampa Florida, Mr. Cramer is a past president of ASHI, the American Society of Home Inspectors and is a Florida home inspector and home inspection educator. Mr. Cramer serves on the ASHI Home Inspection Standards. Contact Mark Cramer at: 727-595-4211 mark@BestTampaInspector.com
John Cranor is an ASHI member and a home inspector (The House Whisperer) is located in Glen Allen, VA 23060. He is also a contributor to InspectApedia.com in several technical areas such as plumbing and appliances (dryer vents). Contact Mr. Cranor at 804-747-7747 or by Email: email@example.com
Carson Dunlop, Associates, Toronto, have provided us with (and we recommend) Carson Dunlop Weldon & Associates' Technical Reference Guide to manufacturer's model and serial number information for heating and cooling equipment
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
"Air Conditioning & Refrigeration I & II", BOCES Education, Warren Hilliard (instructor), Poughkeepsie, New York, May - July 1982, [classroom notes from air conditioning and refrigeration maintenance and repair course attended by the website author]
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: firstname.lastname@example.org. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones