Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
A guide to light bulbs ("lamps"): Here we provide a guide to the different types of light bulbs (lamps) used in indoor light fixtures. We describe the indoor use of halogen lights, and low-voltage lights. We provide a guide for using fluorescent lights and compact fluorescent bulbs indoors and we include a table comparing fluorescent bulb light levels to incandescent light bulbs. And we discuss issues surrounding the color temperature of fluorescent lighting. This article series details guidelines for selecting and installing interior lighting to meet the requirements for different building areas.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Here we provide a guide to the different types of light bulbs (lamps) used in indoor light fixtures. This article series details guidelines for selecting and installing interior lighting to meet the requirements for different building areas. This article includes excerpts or adaptations from Best Practices Guide to Residential Construction, by Steven Bliss, courtesy of Wiley & Sons.
[Click to enlarge any image]
Our page top photo illustrates dramatic use of lighting at the Metropolitan Opera building in New York City.
More detail about lamp or bulb types including abbreviations and feature comparisons can be read at Lamp & Bulb Abbreviations & Types. Also see LIGHTING, INTERIOR GUIDE our home page for information about all lighting topics relating to building interior There is a vast array of choices in light bulbs, known in the lighting industry as “lamps.”
For residential lighting, the main choices are incandescent, halogen, low-voltage, tubular fluorescent, and compact fluorescent.
Which lamp to choose for a given application will depend upon the amount of light needed (lumens), color of light desired, type of fixture (luminaire), and whether the application calls for a directed beam or a diffused light source.
Also, some lamps are more energy-efficient, providing more lumens for the same amount of electricity consumed.
Fluorescent's are the most efficient, using up to 70% less energy than an equivalent incandescent bulb (see Table 5-22).
Incandescent's have a low color temperature of around 2700 K, which produces a warm light with lots of red and yellow tones that make skin, natural wood, and other warm colors look good.
To some extent, things look good to us under incandescent light because it is what we are most accustomed to.
Incandescent lamps are inexpensive and are easy to dim, but they are also the least efficient type of bulb and the shortest lived.
Our photo (above-left) illustrates an antique ceiling light fixture using incandescent bulbs in a home in Wappingers Falls, NY. Originally the fixture included small glass shades around each bulb - yet to be restored by the editor - DF.
And this bulb, a 75-watt unit was over-watted for the fixture whose sticker warned that 60-watts was its limit. Installing a bulb of higher watt-rating than the fixture permits is a fire hazard.
Halogen bulbs, also known as tungsten-halogen, is actually a kind of incandescent with more blue and less red light (3000 K), giving it a whiter appearance than standard incandescent lamps.
Halogen lamps provide good color rendition and good light for reading and fine detail work. When dimmed, however, halogen light becomes more yellow, like standard incandescent lighting. Also, dimming can cause a halogen lamp to darken due to tungsten evaporation. Turning the lamp to full illumination for about 10 minutes will restore its full power.
Halogen lamps tend to be smaller, produce 10 to 15% more lumens per watt than standard incandescent's., and last about twice as long. They come in a wide range of beam spreads and wattages. However, since halogen lights burn very hot, they must be shielded from contact with other materials or they can create a fire hazard.
The halogen bulb shown at left is used in work lights and security lights. Work lights using this bulb and in use indoors must be kept a safe distance from combustibles.
Also, the bulbs should not be touched without wearing a glove (since the oil from your skin can create a weak spot on the bulb), and should be cleaned with alcohol.
Halogen PAR (parabolic aluminized reflector) lamps are enclosed in a protective glass casing, which allows them to be handled like ordinary bulbs. (See the 12-V bulbs illustrated below).
Low-Voltage lamps are tungsten-halogen, incandescent, or the newer xenon lamps, operating at 12 volts DC. Their small size makes them ideal for under cabinet lighting, and their very precise beam control makes them well-suited to accent lighting of artwork. Many low-voltage fixtures allow the lamps to rotate within the housing to precisely aim the beam.
Most newer fixtures use solid-state electronics, which are more energy efficient and longer lasting than the older magnetic type.
Transformers are either attached to the fixtures or installed remotely.
Since the transformers, as well as the lamps and dimmers, emit a slight hum, remote location can be an advantage. However, locating the transformer too far from the fixtures can result in a loss of power and dimming of the lamps.
When using dimmers with low-voltage lighting, make sure they are specifically designed for low voltage systems and for the specific type of transformer.
Fluorescent bulbs or lamps produce light by energizing the phosphor coating on the inside of a glass envelope. A device called the ballast regulates the power needed to start the lamp and keep it going. Older magnetic ballasts caused humming and flickering, but new electronic or solid-state ballasts have eliminated these problems.
Fluorescent's produce three to five times the output as incandescent lamps [per watt of energy used], last about ten times as long, and stay very cool.
Because they reduce lighting bills by as much as 75%, and reduce cooling loads as well, they are heavily promoted by model energy codes and mandated in some areas. For example, the California Energy Code requires that the main lighting in kitchens and baths be fluorescent.
The downside of fluorescent's has always been their poor color rendering. Standard fluorescent's emphasize the blue range of the spectrum, giving skin an unflattering, pale appearance. Manufacturers have worked hard over the years to improve the light quality.
So-called “deluxe” fluorescent's offer CRI (color rendering index) values in the 85 to 90 range but with a 25% loss of efficiency. To achieve CRIs in the high 90s without sacrificing energy efficiency, manufacturers use more expensive rare earth phosphors, creating triphosphor and quad-phosphor lamps.
Fluorescent lamps with high CRIs, and color temperatures within the range of 2700 to 3500K, create pleasing light for skin tones and natural wood and can blend in with incandescent lighting. In applications where color accuracy is important, such as laundry areas, lighting artwork, and certain hobbies, full-spectrum daylight lamps may be preferred.
These lamps, which produce light similar to natural daylight, include General Electric’s Chroma 50 and Chroma 75.
Dimming also used to be a challenge with fluorescent's However, using solid-state dimming ballasts and special dimmers designed for fluorescent's can eliminate any humming sounds. These also allow a single dimmer switch to dim groups of fixtures with different length tubes.
Cold Cathode Bulbs
The super-compact fluorescent 120-V bulb shown at left using an Edison base and with a color temperature of around 2700 K is available from TCP, a company offering a wide range of lighting components, bulbs, ballasts. Shown is TCP's "Cold Cathode" 8-watt bulb, item 8G2508CL.
This bulb type emits very little heat and is described by the company as especially suitable for signs, marquees, and accent lighting both indoors and outside. The bulbs are also described as excellent for dimming & flashing applications. Photograph courtesy of our associate Charles Soberman.
Note: these Cold Cathode bulbs are UL approved for wet locations in Base Up Position ONLY.
Compact fluorescent lights have created a lot more flexibility, allowing fluorescent's to be used in recessed downlights, wall sconces, pendants, and just about any type of luminaire. Early compact fluorescent's were noisy, slow to start, and had a limited selection of color temperatures.
Newer products, however, are quiet and typically have rapid-start ballasts. Dimmable ballasts are also available for compact fluorescent's, but are costly. As with tube fluorescent's, look for high CRIs and lower (warmer) color temperatures from 2700 to 3500K to blend in with incandescent and halogen lighting. All compact fluorescent's have a minimum 80 CRI.
While some compact fluorescent's have been introduced that mimic R and PAR-type reflector bulbs, directional lighting is best achieved with incandescent or halogen lamps.
Fluorescent's are better used for ambient lighting, indirect lighting, and lighting of closets and storage areas. Although they cost $5 to $20 per bulb, depending on the wattage and configuration, they generally pay for themselves within two to three years in both energy savings and longevity of the bulbs.
-- Adapted with permission from Best Practices Guide to Residential Construction.
Guide to LED Light Bulbs
Please see LED BULB & LIGHTING TYPES for details about LED light bulbs used in building lighting & light fixtures.
LED bulb brigtness in lumens and energy costs are at our Table of Current LED Bulb Prices & Features.
-- Adapted with permission from Best Practices Guide to Residential Construction.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about the properties of different types of light bulbs or lamps for indoor lighting use.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References