InspectAPedia^{®}  Question? Just ask us! 
InspectAPedia
 
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair 
InspectAPedia ^{®} Home ENERGY SAVINGS in buildings INSULATION IDENTIFICATION GUIDE INSULATION INSPECTION & IMPROVEMENT ACOUSTICAL SEALANT CHOICES AIR LEAK DETECTION TOOLS AIR LEAK MINIMIZATION AIR LEAK SEALING PROCEDURE AIR SEALING STRATEGIES ROOF ICE DAM LEAKS BATHROOM VENTILATION BASEMENT CEILING VAPOR BARRIER BASEMENT HEAT LOSS BLOWER DOORS & AIR INFILTRATION BRICK LINED WALLS BRICK VENEER WALL AIR LEAKS BUCKLED FOUNDATIONS due to INSULATION? CATHEDRAL CEILING INSULATION CATHEDRAL CEILING VENTILATION CRAWL SPACES CONDENSATION or SWEATING PIPES, TANKS COOLING LOAD REDUCTION by ROOF VENTS DEHUMIDIFICATION PROBLEMS DEW POINT CALCULATION for WALLS FIBERGLASS INSULATION FIBERGLASS HAZARDS FRAMING DETAILS for BETTER INSULATION FRAMING DETAILS for DOUBLE WALL HOUSES FRAMING METAL STUD PERFORMANCE FREEZEPROOF A BUILDING FROST HEAVES, FOUNDATION, SLAB GREENHOUSE DESIGN for SOLAR HEATING HEAT LOSS in BUILDINGS HOT ROOF DESIGNS: UnVented Roof Solutions HOUSEWRAP AIR & VAPOR BARRIERS HUMIDITY LEVEL TARGET INDOOR AIR QUALITY & HOUSE TIGHTNESS INSULATION INSPECTION & IMPROVEMENT INSULATION RValues & Properties LEED GREEN BUILDING CERTIFICATION MOISTURE CONTROL in BUILDINGS NOISE / SOUND DIAGNOSIS & CURE ODORS GASES SMELLS, DIAGNOSIS & CURE RADIANT BARRIERS SOUND CONTROL in buildings STAIN DIAGNOSIS on BUILDING INTERIORS THERMAL MASS in buildings THERMAL TRACKING & HEAT LOSS VAPOR BARRIERS & CONDENSATION in buildings VENTILATION in BUILDINGS WALL CONSTRUCTION BARRIER vs CAVITY WIND WASHING INSULATION At EAVES WINDOWS & DOORS WINTERIZE A BUILDING WOOD, COAL STOVES & FIREPLACES WOOD STOVE SAFETY ZONE DAMPERS ZONE VALVES, HEATING More Information 
How to calculate building heat loss rates R, U and K. This article gives details and formulas for calculating Rvalues, Uvalues Ucoefficient of heat loss resistance, and Kvalues, all ways of looking at insulation values or building heat loss rates. Our page top photo of aboveground building perimeter & foundation insulation using styrofoam board was observed at a home Maine  Ed. Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved. Definition of & How to Calculate the R value or Rcoefficient of Resistance to Heat Loss in a Building or its InsulationThe "R" value of a material is defined as the material's resistance to heat flow through the material. For purposes of insulation, you might think of "R" value as the opposite of thermal conductance, since it's described as thermal resistance or resistance to heat flow. And you'd be correct. If thermal resistance to heat flow is "resistance" we can say that the thermal conductivity of a material is equal to the reciprocal of its thermal resistance. More practically, by convention we use thermal resistance or Rvalue when buying various insulation materials. You will almost always see an "R" value quoted for the material. In general, higher "R" means more resistance to heat loss and therefore lower heating or cooling bills for the building. [Assuming all other fadctors like air leakage are either equal or have been factored into the Rvalue calculation.] Mathematically, but in painfully circular reasoning, "Rvalue" is simply the reciprocal of the two measures of resistance to heat flow "Kvalue" (R = 1/K) or "Uvalue" (R_{(whole building)} = 1/U) that we define further below. What do U and K values have to do with Rvalues?As you'll read below "K" measures the heat flow through an individual substance and "U" as most folks use it measures the overall building heat loss by adding all of the various areas and substances together. Uvalues measure the thermal transmittance of heat in or out of a building and combines heat movement by all principles that are occurring at a building: radiation, convection, and conduction. So you can see that "U" values are more complex but really more complete than "R" values. Escaping the Circular Reasoning of R=1/KWe can escape the horrible circular reasoning that appears in some writing about heat loss measurements if any one of the three values, R, U, K is defined independently. We'll take a stab at this just below. The Rvalue of a material is typically expressed as R [resistance to heat flow] per inch of material thickness. More technically, "Rvalue" is measured in mete Watt [metric system] or h/Btu [U.S. measurement system]. Materials may be rated in R per inch or R per meter or similar measures. Here are Some Basic Formulas for Calculating RValuesRvalue = temperature difference [in degF] x area [sq ft] x time [in hours] / heat loss[in BTUs] Calculating RValue [U.S. metrics] R = (Heat Resistance x Degrees F x square feet) / BTUs or stated in metric: (Rvalue) = t/k, measured in [editing needed] Definition of & How to Calculate the U value or Ucoefficient of heat loss resistanceComputing "K" values tells us the heat loss rate for a specific material, thickness, area, and temperature difference but while we need to be able to calculate "K" values, those alone don't tell us what's going on in an actual building. We need to be able to combine all of the rates of heat loss (or gain) across all of the types of surfaces, insulation, and building material for the whole building  at least for all of its external or perimeter surfaces including roofs, walls, and floors as well as windows and doors. That's where the "U" value makes its appearance. A building's "U" value or Ucoefficient of resistance of heat loss is a related measure of resistance to thermal energy or heat flow out of a building (if it's warmer inside than outside) or conversely the same concept works in a warm climate where air conditioning is in use, except that we expect outside heat to be flowing into the building. A building's "U" value is much more complete, and therefore useful than "K" values alone because a building's "U" value combines the "K" factors for all of the building's surfaces and materials. In other words, we add the effects of heat loss (or gain), still expressed in the number of BTU's per hour per square foot of area, and still expressed per degree of Fahrenheit of temperature difference and still expressed per inch of thickness of material (just as with "K" values), for all of the substantial areas and surfaces of the exterior of a building's floors, walls, windows, doors, ceilings, or roofs (if cathedral ceilings are present). To calculate the "U" value, or overall heat loss (or gain if we're air conditioning) for a building, we need to add the "R" values for each material in the structure, and to factor in the total area of each material in the structure. We discuss this procedure in more detail below at "Calculating Heat Loss for a Building". Uvalue = BTUs / (hours x Degrees F x Square Feet) A building's "U" value or Ucoefficient of resistance of heat loss is a related measure of resistance to thermal energy or heat flow out of a building (if it's warmer inside than outside) or conversely the same concept works in a warm climate where air conditioning is in use, except that we expect outside heat to be flowing into the building. A building's "U" value is much more complete, and therefore useful than "K" values alone because a building's "U" value combines the "K" factors for all of the building's surfaces and materials. In other words, we add the effects of heat loss (or gain), still expressed in the number of BTU's per hour per square foot of area, and still expressed per degree of Fahrenheit of temperature difference and still expressed per inch of thickness of material (just as with "K" values), for all of the substantial areas and surfaces of the exterior of a building's floors, walls, windows, doors, ceilings, or roofs (if cathedral ceilings are present). To calculate the "U" value, or overall heat loss (or gain if we're air conditioning) for a building, we need to add the "R" values for each material in the structure, and to factor in the total area of each material in the structure. We discuss this procedure in more detail below at "Calculating Heat Loss for a Building". Formulas Used to Calculate the Rate of Building Heat Loss Per Hour for a Building Using it's "R" Values or "U" ValuesFormulas and an explanation of how we use R U or K values to determine the rate of heat loss at a building (or heat gain if we are cooling it) are at HEAT LOSS in BUILDINGS or within that articler at section Formulas to Calculate the Rate of Heat Loss Per Hour for a Building Using it's "R" Values or "U" Values. Definition of & How to Calculate the K value or Kcoefficient of heat transmissionA building's K value or Kcoefficient of heat transmission is one way to express the heat loss in a building. "K" is defined as the number of BTU's of heat moving through any material with these details:
So "K" takes a lot of variables into consideration and gives us the rate of heat loss per square foot of building surface, per inch of thickness of material in that building surface, per degree of temperature difference in Fahrenheit, in BTUs per hour. By "degree of temperature difference in Fahrenheit" we mean that we are taking into consideration the difference in temperature on the two sides of our building surface. For example, if the indoor temperature in a building is 68 deg. F. and the outdoor temperature is 48 deg. F., then we have a 20 degree temperature difference on the two sides of the building (wall or roof for example). This temperature difference on the two sides of a surface, say an insulated building wall, for example, is very important in understanding how a building loses heat (in the heating season) or gains heat (in the cooling season). That's because the rate of heat transfer through a material increases exponentially as a function of the temperature difference. This is intuitively obvious and is confirmed by physicists. For example, if the temperatures on either side of a building wall were the same, there would be no heat loss or gain through the building wall. As the temperature difference on either side of that same wall increases, say from one degree of difference to 20 degrees of difference the rate of heat transfer increases. An interesting version of this heat transfer theory was shared with the author in a class on how to minimize building heating costs when the instructor told us that "the thermal conductivity of finned copper heating baseboard is exponentially greater at higher temperatures". He was saying that if we ran heating water from our heating boiler through the baseboards at 200 deg.F. we would see much more efficient heat transfer from the heating baseboards into the building. There are other factors involved in heating system efficiency such as the length of boiler on cycle (longer is more efficient), so there was more to think about, but the instructor was applying classic heat transfer theory that is reflected in the "K" values of building insulation as we've discussed here. Computing "K" values tells us the heat loss rate for a specific material, thickness, area, and temperature difference but while we need to be able to calculate "K" values, those alone don't tell us what's going on in an actual building. We need to be able to combine all of the rates of heat loss (or gain) across all of the types of surfaces, insulation, and building material for the whole building  at least for all of its external or perimeter surfaces including roofs, walls, and floors as well as windows and doors. That's where the "U" value makes its appearance. Sorting out the Definitions of U.S. kvalues, lambda or values, and European kvaluesNote: In the U.S. kvalue when discussing the heat loss resistance of window glazing is equivalent to lamdavalue in Europe, and in case that's not confusing enough, an older European kvalue (the total insulation value of a building) is currently referred to in Euripe as Uvalue. You'll recall from our notes above that Uvalue is a reciprocal or 1/Rvalue.  Wikipedia web search 03/11/2011 see "Thermal Conducitivity". To convert U.S. Rvalues to European Uvalues: [ (1 / Rvalue _{USA}) x 0.176 ] / 1 = U _{Europe} and U _{Europe} = [watts / kelvin x meters^{2}] Related Building Heat Loss ArticlesBeginning at HEAT LOSS in BUILDINGS article series explains how to insulate a building and how much insulation is needed including how to measure or calculate heat loss in a building, defines thermal terms like BTU and calorie, provides measures of heat transmission in materials, gives desired building insulation design data, and shows how to calculate the heat loss in a building with R values or U values Also see HEAT LOSS INDICATORS (where is the building losing heat during the heating season, or gaining unwanted heat during the cooling season),see HEAT LOSS DETECTION TOOLS for both tools and procedures, and see HEAT LOSS R U & K VALUE CALCULATION for a guide to calculating heat loss (or gain) rates for buildings and building insulation. At INSULATION RValues & Properties we give a detailed table of insulating material Rvalues & properties. Be sure to review the definitions of R, U, & K Values at DEFINITION of HEATING & COOLING TERMS. Because no amount of insulation can keep a drafty building warm, also review ENERGY SAVINGS PRIORITIES. Also see our detailed table of Insulation RValues & Properties and our list of building HEAT LOSS INDICATORS (where is the building losing heat during the heating season, or gaining unwanted heat during the cooling season). FormulaR™ and Owens Corning™ which may be visible in this photograph of pink Styrofoam™ insulation boards are registered trademarks of Owens Corning® and were photographed at a Home Depot® building supply center. ...
Frequently Asked Questions (FAQs) about how to calculate R U K heat loss rates for buildings or insulation systems... Ask a Question or Search InspectApediaQuestions & answers or comments about how to calculate building heat loss rate, Rvalues, Insulation Values, Heating Efficiency. Check the FAQs just above, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly. Search the InspectApedia website HTML Comment Box is loading comments...
Technical Reviewers & ReferencesRelated Topics, found near the top of this page suggest articles closely related to this one. Click to Show or Hide Citations & References
Books & Articles on Building & Environmental Inspection, Testing, Diagnosis, & Repair
