Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
WATER PUMPS, TANKS, TESTS, WELLS, REPAIRS
WATER CONSERVATION MEASURES
WATER CONTAMINANT LEVELS
WATER FILTERS, HOME USE
WATER HAMMER NOISE DIAGNOSE & CURE
WATER ODORS, CAUSE CURE
WATER PUMP REPAIR GUIDE
WATER PRESSURE LOSS DIAGNOSIS & REPAIR
WATER PUMP SHORT CYCLING
WATER SOFTENERS & CONDITIONERS
WATER TANK REPAIR PROCEDURES
WATER TANK: USES, TROUBLESHOOTING
WATER TESTS, CONTAMINANTS, TREATMENT
WATER TREATMENT EQUIPMENT CHOICES
WELLS CISTERNS & SPRINGS
WELL CHLORINATION & DISINFECTION
WELL FLOW RATE
WELL WATER PRESSURE DIAGNOSIS
WELL YIELD IMPROVEMENT
WINTERIZE A BUILDING
This article describes the sequence of operating steps in a submersible well pump water system. The process of diagnosis and the costs of the repair are explained. Consumer advice on saving money on water supply repair costs includes a review of the parts and labor costs of a typical well pump and pressure tank replacement case.
Carson Dunlop's sketch at page top shows the components of a submersible well pump water supply system.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
What happens when you turn on the water at a faucet in a building whose water is supplied by a submersible well pump?
The following steps describe normal operating of a building well pump and water supply system. Other cases in which the well pump controls are not working properly, there is a problem with the controls, pressure tank, pump, or well itself are discussed at WATER PRESSURE REPAIR GUIDE & COSTS and at WELL WATER PRESSURE DIAGNOSIS. Our sketch (left) shows a cutaway view of a submersible well pump.
Take a look at our well casing photograph at left. See that small gray conduit rising at the left side of the well casing? The conduit carries electrical wires into the well. That's one way to recognize that a submersible pump is installed.
When a water pump is inside the well, it can be tricky to know when the pump is actually on or off, though usually we hear the pump relay clicking, and some relays have a light that indicates that the relay is telling the pump to run.
The pressure switch calls for pumping by switching a relay in the pump relay, that actually turns the pump on and off. So a secondary potential problem would be in the relay itself, but we would look at the pump pressure control switch first.
Separately we also provide a WATER PRESSURE PROBLEM DIAGNOSIS TABLE. The following articles pertain if you have a private well, pump, and tank system for your building or if your incoming community water supply pressure and flow are just too low to start with:
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about how submersible well pumps work and the sequence of operating steps - help in diagnosing well pump troubles.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References