Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
Ask a Question or Search InspectAPedia
InspectAPedia ® Home
WATER PUMPS, TANKS, TESTS, WELLS, REPAIRS
WATER CONTAMINANT LEVELS
WATER HAMMER NOISE DIAGNOSE & CURE
WATER ODORS, CAUSE CURE
WATER PUMP REPAIR GUIDE
WATER PRESSURE LOSS DIAGNOSIS & REPAIR
WATER PUMP SHORT CYCLING
WATER SOFTENERS & CONDITIONERS
WATER TANK REPAIR PROCEDURES
WATER TANK: USES, TROUBLESHOOTING
WATER TESTS, CONTAMINANTS, TREATMENT
WATER TREATMENT EQUIPMENT CHOICES
WELLS CISTERNS & SPRINGS
WELL FLOW RATE
WELL WATER PRESSURE DIAGNOSIS
WELL YIELD IMPROVEMENT
WINTERIZE A BUILDING
This article describes how to identify, diagnose and repair of WellMate™ water tanks, including both internal air bladder-type tanks (WellMate™ captive air water tanks) and bladderless traditional or hydro pneumatic type water pressure tanks such as the WellMate™ Traditional Air/Water tank: how they work, what goes wrong, how to fix it.
Readers of this document should also see WATER TANK BLADDER PRESSURE ADJUSTMENT where we describe adjusting air pressure in a bladder type water tank to factory specs, and also see Water pump and pressure tank repair diagnosis & cost an specific case which offers an example of diagnosis of loss of water pressure, loss of water, and analyzes the actual repair cost. The illustration at page top is courtesy of Carson Dunlop Associates.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved. Author Daniel Friedman.
Reader Nancy Martin asked how to diagnose well pump short cycling and a possible water tank or bladder problem for the WellMate bladder-type water tank which uses the tank bladder to retain the air charge in a water pressure tank. WellMate™ describes two types of water pressure tanks used in residential and light commercial applications:
Captive air tanks that incorporate an internal, replaceable air cell or bladder, and bladderless hydro pneumatic water tanks (shown at the top of This article ), also called traditional residential water tanks that incorporate no internal bladder but use a tank top mounted air volume control. Our WellMate links near the bottom of This article can direct you to photographs that help identify which type of water tank is installed at your property.
Which Type of WellMate or Fiberglass Water Tank is Installed?
These are different tank designs so first we need to know which type you have - take a look at the photos at the two WellMate links.
Captive Air Water Pressure Tanks with an Internal Air Bladder
Type 1 or captive air water pressure tanks sold by WellMate and some other manufacturers are constructed of fiberglass and use an internal bladder to hold the air charge.
If the air bladder has ruptured, the water tank will begin to act like an old-fashioned steel water tank - air absorbs into the water until there is not much air charge, the tank becomes water logged, and the well pump will short cycle on and off. Our description of conventional steel water tanks adds details. If the air bladder has failed, the tank will act much like a type 2 hydro pneumatic or traditional water tank.
Tips for Testing & Repairing a Captive Air Water Tank Bladder
Try this: if you have this type of tank, remove the valve step cap covering the bladder inflator valve located on the top of the tank. Using a small implement, MOMENTARILY (just for a second) depress the valve pin in the center of the valve stem down to see if air or water comes out. If water comes out of this valve the air bladder has burst. But the bladder could be burst but blocking the valve in which case nothing will happen. If air comes out of this valve the the tank bladder contains air and may not have burst.
If air comes out of the valve, use an accurate tire gauge to check the air pressure at the valve. If the air pressure is 4 psi below the well pump cut-in pressure then the air bladder is probably fine. If the air pressure is less than that figure, using a bicycle pump, just add a little air to the bladder until it is set to the proper number - 4 psi below the pump cut-in pressure.
Draining the water tank itself and adding air to a bladder type tank itself through the (ruptured) bladder valve at the tank top of a tank with a failed bladder MIGHT work to improve performance for a while (until the air is reabsorbed back into the water over time) but you need to replace the bladder. A guide to replacing the air bladder in the WellMate captive air tank is provided by the company at http://www.wellmate.com/pdf/Residential_AirCell_Replace_Instructions.pdf
The air bladder in the WellMate™ type water tank is to be inflated to 4 psi below the well pump's "cut-in" pressure.
The installation manual for this tank is at http://www.wellmate.com/pdf/Residential_CaptiveAir_Tank_Install_Manual.pdf
Tips for Testing & Repairing a Traditional Hydro-Pneumatic (no internal bladder) Fiberglass Water Tank
Type 2 tanks, described by WellMate as hydro pneumatic water tanks, do not incorporate an internal bladder but rather an air volume control valve that replaces air into the tank as needed. These tanks will perform better than older steel water pressure tanks because we don't face the concern of rust perforation of the tank.
If the air volume control (AVC) fails, the tank will act much like a type 2 tank (See TANK TYPES: WATER, OIL, EXPANSION, ALL and scroll down to the description of older steel water tanks. In this case you may need to replace the AVC. See the installation manual at http://www.wellmate.com/pdf/UT_HP_SPTank_Install.pdf
Draining and adding air to an AVC type tank with a failed AVC also MIGHT work to improve performance for a while (until the air is reabsorbed back into the water over time) but you need to replace the AVC.
Water tank bladder air pressure adjustment: also review WATER TANK BLADDER PRESSURE ADJUSTMENT if you are adjusting, tuning, or replacing the air pressure in your bladder-type well tank.
Frequently Asked Questions (FAQs)
Use the search box below to ask a question or to search the InspectApedia.com website.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.
Water Supply & Drain Piping, Wells, Pumps, Water Supply Equipment