Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
WATER PUMPS, TANKS, TESTS, WELLS, REPAIRS
WATER CONSERVATION MEASURES
WATER CONTAMINANT LEVELS
WATER FILTERS, HOME USE
WATER HAMMER NOISE DIAGNOSE & CURE
WATER ODORS, CAUSE CURE
WATER PUMP REPAIR GUIDE
WATER PRESSURE LOSS DIAGNOSIS & REPAIR
WATER PUMP SHORT CYCLING
WATER SOFTENERS & CONDITIONERS
WATER TANK REPAIR PROCEDURES
WATER TANK: USES, TROUBLESHOOTING
WATER TESTS, CONTAMINANTS, TREATMENT
WATER TREATMENT EQUIPMENT CHOICES
WELLS CISTERNS & SPRINGS
WELL CHLORINATION & DISINFECTION
WELL FLOW RATE
WELL WATER PRESSURE DIAGNOSIS
WELL YIELD IMPROVEMENT
WINTERIZE A BUILDING
Smells & odors in drinking water:
This article describes water treatment methods to remove sulphur odors or rotten egg smells from the building water supply. This is the second part of our article discussing how to identify, diagnose, and cure common odors that may be present in drinking water.
We also discuss which of these odors may warn of unsanitary conditions.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
If the source of rotten egg smells or sulphur in your building is not traced to a water supply problem, see these related articles
Because sulphur-reducing bacteria are normal flora, or naturally occurring bacteria, you probably can't get rid of them altogether, but annual dosing of your well with chlorine bleach will help keep them at bay.
Shock chlorinating your home system may, or may not solve the problem because the chlorine might not circulate into the dead-leg area of plumbing. If this happens, just have a plumber remove that portion of pipe. The easiest way to get rid of sulfur odor is to use a filter with activated charcoal or carbon.
If your sulphur odor is from the water heater, changing the anode should do the trick.
Water treatment systems to remove sulphur odors are available from water treatment companies. What you need to cure a sulphur odor depends on the duration (seasonal versus all year), cause (water supply versus piping or water heater), and severity.
Water softeners are designed to remove minerals from water, such as calcium or magnesium that make "hard" water. However many softeners will also handle low levels of sulphur odor. Just be sure the odor source is not a dirty water softener salt tank!
Common treatment methods use "green sand" filters or exchange tanks (potassium permanganate) or other chemical treatments, or chlorinators followed by a charcoal filtration system.
Water or Well Treatment to Remove Bacteria-produced Odors
Above we discussed odors in drinking water caused by Manganese, Iron in the water supply which in turn support the growth of foul-odor-producing bacteria such as Gallianella. You probably can't get rid of Gallianella because they are normal flora, (naturally occurring bacteria), but annual chlorination of your well will help keep them in check.
An ultraviolet disinfection system can disinfect the water as it comes into distribution to remove bacteria within the system [but keep in mind that UV treatment does not remove any other contaminants such as particles or chemicals]. Chlorination may also be used, but is not a great choice if there is a lot of iron and manganese, as the chlorine will precipitate the metals out of solution and discolor the water.
If it's necessary, a (more costly) cascade of water treatment equipment, installed in the proper sequence, can first remove un-wanted minerals such as iron and manganese, second, chlorinate the water to reduce bacterial levels, odors, and other chemical contaminants in water, and third, post-process the water often using charcoal filtration, to remove remaining chlorine from the water.
Here's A Free and Simple Way to Get Rid of Sulphur Odors in Drinking Water
A great way to get hydrogen sulfide reduced water to drink for free is to fill a clean milk jug three fourths full of tap water. Cover, and shake vigorously for 20-30 seconds. Remove the cover and let set on the counter for ten minutes or so, allowing time for the hydrogen sulfide you released from the water to vent out of the jug - providing you with sulfur free or reduced drinking water - at no expense!
Continue reading at WELL CHLORINATION SHOCKING PROCEDURE or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
we have a new presure tank with a bladder. we also have a rotten egg smell in our water. I read on your web sight that a snifter valve would eliminate that.I wonder if it would make sents to put the bladderless tank in ahead of the bladder tank. Thanks Joe ps. your wed sight is very good. - J.M. 1/18/2014
A snifter valve (SNIFTER VALVES ) is a device that adds air to a pressure tank system where a submersible pump and a bladderless pressure tank are installed. It has nothing to do with the elimination of a sulfur odor or rotten-egg smell in water. IF the odor is in incoming cold water I agree that it's probably originating in the well, and that a treatment system may be what's needed.
I suggest taking a look at either or both of these two articles
A second question arises from your note: I don't have a clear picture of what water equipment you have installed, but it sounds a bit odd to have both a bladderless water pressure tank and a bladder tank on the same system unless the bladderless tank is a large water quantity storage system (as we might have on a well with a poor water flow rate - WATER STORAGE TANKS, LARGE).
Perhaps with more details about & photos of your system I could comment further.
Questions & answers or comments about how to get rid of or prevent sulphur or rotten egg smells in drinking water.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References