Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
WATER PUMPS, TANKS, TESTS, WELLS, REPAIRS
WATER CONSERVATION MEASURES
WATER CONTAMINANT LEVELS
WATER FILTERS, HOME USE
WATER HAMMER NOISE DIAGNOSE & CURE
WATER ODORS, CAUSE CURE
WATER PUMP REPAIR GUIDE
WATER PRESSURE LOSS DIAGNOSIS & REPAIR
WATER PUMP SHORT CYCLING
WATER SOFTENERS & CONDITIONERS
WATER TANK REPAIR PROCEDURES
WATER TANK: USES, TROUBLESHOOTING
WATER TESTS, CONTAMINANTS, TREATMENT
WATER TREATMENT EQUIPMENT CHOICES
WELLS CISTERNS & SPRINGS
WELL CHLORINATION & DISINFECTION
WELL FLOW RATE
WELL WATER PRESSURE DIAGNOSIS
WELL YIELD IMPROVEMENT
WINTERIZE A BUILDING
Water odor diagnosis & cure:
This article discusses how to identify, diagnose, and cure rotten egg or sulphur odors in drinking water.
We also discuss which of these odors may warn of unsanitary conditions. Edits, content addition, & web page design
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
If your source water runs through an area where naturally occurring sulfur is present, some sulfur may dissolve into the water. We provide a diagnostic procedure to track down the source of sulphur smells in water just below.
Some of this dissolved sulfur turns to the gas, hydrogen sulfide, and this can give the water a rotten egg type smelly odor.
Sulphur odors can also be caused by a failing hot water heater component, or by certain bacteria in the building plumbing system, conditions we also discuss below.
Sulphur smells in water can also occur in rivers, lakes, streams, ponds, and can be caused by anoxia and algae which in turn may be caused by high nitrogen from agricultural runoff - a condition we discuss
Watch out: methane odors in a building water supply can be explosive -
Watch out: Sulphur smells, rotten egg smells, or sewer gas smells can be caused by a variety of problems that we describe here. The sulphurous odor may be due to sulphur in the building water supply, bacteria in water, deteriorating water heater electrodes, dangerous sewer gas leaks, hydrogen sulfide gas forming in the water heater itself, even contaminated drywall or perhaps human or animal flatulence. Some of these gases and the implications of their source can be very dangerous, as we describe here and in related articles.
What if the Sulphur Odor is Not Traced to the Water Supply?
If the source of rotten egg smells or sulphur in your building is not traced to a water supply problem, see these related articles
Continue reading at WATER ODOR TREATMENTS, CURES - SULPHUR or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References