Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
WATER PUMPS, TANKS, TESTS, WELLS, REPAIRS
WATER CONSERVATION MEASURES
WATER CONTAMINANT LEVELS
WATER HAMMER NOISE DIAGNOSE & CURE
WATER ODORS, CAUSE CURE
WATER PUMP REPAIR GUIDE
WATER PRESSURE LOSS DIAGNOSIS & REPAIR
WATER PUMP SHORT CYCLING
WATER SOFTENERS & CONDITIONERS
WATER TANK REPAIR PROCEDURES
WATER TANK: USES, TROUBLESHOOTING
WATER TESTS, CONTAMINANTS, TREATMENT
WATER TREATMENT EQUIPMENT CHOICES
WELLS CISTERNS & SPRINGS
WELL CHLORINATION & DISINFECTION
WELL FLOW RATE
WELL WATER PRESSURE DIAGNOSIS
WELL YIELD IMPROVEMENT
WINTERIZE A BUILDING
This article describes Water Tank Pressure Relief Valves - how to find buy, or where to install safety valves on water tanks and on well water systems. We explain where a pressure relief valve is usually installed on well water pressure tanks, how the valve works, and why pressure relief valves are an important safety feature on well tanks.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
WATER TANK PRESSURE RELIEF VALVES: installation, inspection, troubleshooting, repair, code requirements for
Early in our building inspection career plumbers in our area were skeptical when we identified the absence of a pressure relief valve as a safety concern (and a building or plumbing code violation). Then in about 1984 a local plumber was killed by a bursting water pressure tank.
The water pump was a submersible unit located (remotely) inside of the water well. The plumber was leaning over the water tank repairing a fitting, unaware that the water pump had turned on, and unaware that the pressure control switch had been damaged or modified so that it failed to turn off the water pump at a safe pressure.
The water tank burst, metal fragments severely injured the plumber who, working alone, bled to death. After that terrible event all of our local plumbers took this relief valve requirement seriously.
How to Buy & Install the Right Water Tank Pressure Relief Valve for Water Storage Tanks or Water Pressure Tanks
Question: What size or capacity of pressure relief valve should be installed on a water pressure tank?
My water tank pressure switch is set to 20 - 40 psi. How do I gage the size of a relief valve I need to put for my tank? - D.R.
Reply: typical water tank pressure relief valves are 1/2" or 3/4" in diameter orifice and are set to open at 75 psi.
The water tank pressure relief valve shown in our photo (above) is marked indicating that it will open at water pressure equal to or greater than 75 psi. That pressure is pretty standard and you'll see the 75 psi figure on valves used on water tanks and on some tankless water heaters too.
According to the Water Systems Council, [quoting, paraphrasing, and expanding - Ed.]
High pressure in a building water supply system can result if the water pressure switch that controls the well pump is damaged, or if the pump stays on too long.
Most submersible well water pumps can develop pressure exceeding the rated working limits of the water pressure tank or building water distribution system piping, fittings, and fixtures. Excess water pressure can damage water system component as well as the pressure tank if not corrected immediately, and can also cause leaks within the piping system or at faucets and fixtures. Therefore on all building water supply systems using a private well and pump, a pressure-relief valve is recommended.
Water pressure relief valves are spring-controlled and open only in response to system pressure. That is, water temperature is not a controlling factor for these valves. For water service, these important safety devices are generally adjusted to relieve pressure higher than 75 psi. 
Watch out: water pressure tank fatality: we [Ed] are aware of a fatality that occurred in the Hudson Valley of New York State when a plumber, working alone on a water pressure tank and pump system was killed as the water pressure tank burst. There was no pressure relief valve on the water system; a submersible well pump was installed; the well pump pressure control switch stuck in the "on" position. We suspect that because the submersible pump was located inside the well and thus there was little or no operating noise when the pump was on, the plumber had no idea that the pump was running. When the pressure inside the water tank exceeded the tank's design specifications the tank burst open. The plumber, leaning over the water tank to perform some task, was cut and killed by the "shrapnel" formed when the water tank burst. - ED.
Examples of water tank and similar pressure relief valves include
But check with the manufacturer of your water tank to determine if a different relief valve opening pressure is required.
Standard water tank pressure relief valves are sold at plumbing suppliers and are pre-set with a "safe" pressure for most home water tanks, provided that the water tank, piping, and controls are properly installed and adjusted. A professional plumber would select and install a water tank pressure relief valve that opens to spill water and relieve pressure at a point well below the rated burst pressure of the tank.
The burst-pressure of a water tank, provided it's undamaged and properly installed, should be well above the opening pressure on the tank relief valve. But to choose a specific valve matched to your water tank, you should consult the manual for your water tank and pump and their manufacturer to be sure you've got the right part.
If a pressure relief valve is not installed on your water tank ask your plumber to provide one promptly.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about the requirement for pressure relief valves on well water pressure tanks
Try the search box just below or if you prefer, post a question or a comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.