Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
PLUMBING SYSTEM INSPECT DIAGNOSE REPAIR
AGE of PLUMBING MATERIALS & FIXTURES
AIR DISCHARGE at FAUCETS, FIXTURES
ANTI SCALD VALVES
ANODES & DIP TUBES on WATER HEATERS
BACKUP PREVENTION, SEPTIC
BACKUP PREVENTION, SEWER LINE
BACKWATER VALVES, SEWER LINE
BATH & KITCHEN DESIGN GUIDE
CHEMICAL CONTAMINANTS in WATER
CHEMICAL ODOR SOURCES
CHLORINE IN DRINKING WATER
DEBRIS in WATER SUPPLY, Water Heater
DEPTH of SEPTIC TANK
DRAIN & SEWER PIPING
FAUCETS & CONTROLS, KITCHEN & BATH
FAUCETS, OUTDOOR HOSE BIBBS
FLOOD DAMAGE ASSESSMENT, SAFETY & CLEANUP
FLOOR DRAIN / TRAP ODORS
FLUSHOMETER VALVES for TOILETS URINALS
GAS PIPING, VALVES, CONTROLS
GALVANIC SCALE & METAL CORROSION
HARD WATER - SOFTENERS
HEAT TAPES, Heat, Insulation prevent Freeze-Up
LEAD POISONING HAZARDS GUIDE
LEAD IN DRINKING WATER, HOW to REDUCE
METHANE GAS SOURCES
MIXING / ANTI-SCALD VALVES
MUNICIPAL WATER PRESSURE IMPROVEMENTS
NOISE / SOUND DIAGNOSIS & CURE
ODORS GASES SMELLS, DIAGNOSIS & CURE
ODORS IN WATER
ODORS, SEPTIC or SEWER
ODORS SEWER GAS in COLD WEATHER
ODORS, SULPHUR SMELL SOURCES
ANIMAL or URINE ODOR SOURCE DETECTION
PIPING IN BUILDINGS, Clogs Leaks Types
PLUMBING FIXTURES, KITCHEN, BATH
PLUMBING NOISE CONTROL
PLUMBING VENT DEFINITIONS & CODES
PLUMBING VENT DEFECTS & NOISES
PUMPS USED in BUILDINGS
PUMPS, WATER REPAIR
RELIEF VALVE LEAKS
RELIEF VALVES - TP Valves on Boilers
RELIEF VALVES - STEAM TP VALVES
RELIEF VALVES - Water Heaters
RELIEF VALVES - Water Tanks
REPAIR BURST LEAKY PIPES
METHANE GAS HAZARDS
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SHUTOFF VALVE LOCATION, USE
SULPHUR & SEWER GAS SMELL SOURCES
SWEATING (CONDENSATION) on PIPES, TANKS
TOILETS, INSPECT, INSTALL, REPAIR
WATER, WELLS, WATER TANKS: TESTING GUIDE
WATER PRESSURE LOSS DIAGNOSIS & REPAIR
WATER PUMPS & TANKS
WATER SOFTENERS & CONDITIONERS
WATER SOURCE ALTERNATIVES
WATER SUPPLY & DRAIN PIPING
WATER SHUTOFF VALVE LOCATION, USE
WATER SHUTOFF VALVE, WELL PUMP
WATER TESTS, CONTAMINANTS, TREATMENT
WELLS CISTERNS & SPRINGS
WINTERIZE A BUILDING
Revere osmosis treatment systems, RO systems for water purification: Here we explain how to install, use, & repair or maintain drinking water reverse osmosis systems or RO systems as an option for high mineral content, odors, or for correcting unsanitary or unsatisfactory drinking water.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Definition of Reverse Osmosis or RO for water treatment
Reverse osmosis as used in water treatment systems is a purification process through which water molecules pass through a porous membrane while leaving other molecules, presumably of contaminants, behind.
Water pressure on the input side or supply side of the RO system is maintained at a higher force than that for "natural osmosis" which otherwise would allow water to flow in either direction across the membrane. Output from the RO system is taken from the "water only" side of the membrane and directed to drinking water faucets or other points of use.
Water on the supply side of the RO membrane along with contaminants accumulating there are flushed from the supply side of the RO membrane into the building's drain system.
How does reverse osmosis water treatment actually work?
Reverse osmosis (RO) systems take advantage of the ability of water molecules to pass through a filter cellulose acetate semi-permeable membrane which at the same time keeps out many other (non-dissolved non-chemical) contaminants.
"Semi permeable" means that the membrane is in effect an ultra fine filter whose openings pass water at a molecular level, leaving other larger molecules behind.
Water pressure (usually at 40 psi or more) forces water molecules through the membrane, leaving behind certain water contaminants including bacteria and sediment. Water on the output side of the filter has been treated or purified, depending on the capacity of the particular RO system.
Our photo ( left) shows a small point of use (POU) reverse osmosis water purifier installed below a kitchen sink. (Also notice that the corroded trap needs to be replaced.)
What contaminants do reverse osmosis water treatment systems remove?
For this reason some reverse osmosis water treatment systems include additional stages of pre or post filtering to remove bacteria, chemicals, odors, tastes.
Reverse Osmosis Water Treatment System Clogging
Watch out for water high in bacterial contamination. Reverse osmosis systems are not usually recommended for water supplies that are high in bacterial contamination because bacteria build-up on the input side of the RO filter tend to block and clog the system.
Watch out: also for water supplies high in sediment, debris, chemicals, odors, or bad tastes.
To avoid clogging the RO system a pre-filter to remove sediment may be needed, and to avoid chemical, taste, or odor complaints, a post-processing charcoal filter system may also be needed.
Reverse osmosis (RO) water purifiers (see sketch at below left) will remove nearly all water contaminants and also remove minerals from water leaving it soft and purified.
Reverse Osmosis Purifiers as Water Softeners
Unlike a conventional salt-based water softener, RO systems do not discharge salt into the drain system, though they do discharge four gallons of waste water for every gallon of purified water produced.
Because the design and capacity of various RO systems varies, only if a reverse osmosis system is registered and listed as a water purifier, can it be relied on to handle bacterial contamination in the water supply.
Disposal of Reverse Osmosis Water Purifier Concentrate
As it becomes high in contaminants, water on the input side of the RO filter is flushed to a disposal location.
See REVERSE OSMOSIS CONCENTRATE WASTE DISPOSAL for a discussion of the effects of disposing of reverse osmosis water treatment equipment wastewater - RO concentrate - into septic tanks and drainfields.
OPINION: this method works well for some contaminants, as a point-of-use system. RO wastes quite a bit of water and does not address some chemical contaminants.
We don't know (yet) which uses more discharge water - a water salt-based water softener or an RO system. That's because the quantity of water "wasted" by a reverse osmosis system depends on the quantity of water that is demanded from its output side.
Reverse Osmosis Water Treatment Effectiveness Research
Continue reading at REVERSE OSMOSIS CONCENTRATE WASTE DISPOSAL or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about choosing, installing, maintaining & repairing chlorinators or RO (reverse osmosis) water purifiers and water treatment systems
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References