This article series describes good practices for clothes dryer vent installation, lint traps, wall vents, filters, and screens. We include a list of clothes dryer fire safety hazards and other clothes dryer installation or maintenance mistakes that are either unsafe or that interfere with effective, economical dryer operation. We discuss types of dryer vent ducting and dryer vent doors or opening protection devices.
We explain and illustrate problems that result from improper dryer vent installation design, materials, routing, and filtering including dryer vent clogging, clothes dryer fire hazards, building moisture and mold problems, and increased clothes dryer operating costs due to poor or blocked dryer vents.
Our page top photo shows a clothes dryer vent that we inspected in a building crawl area. The sagged dryer vent was completely blocked with water from condensation in the sagging flex-duct line. At above left we show an improvement in clothes dryer venting at the home of my daughter Michelle, though the installation looks a bit sloppy. Mishee used metal ductwork for smoother vent interior surfaces and less lint accumulation, and the dyer vents directly to the outdoors with a minimum number of bends or turns.
Proper installation and maintenance of clothes dryer exhaust vents, filters, and lint screens are important for safety (avoiding fires) as well as important in keeping the operating costs of clothes drying down to a minimum by making sure that the dryer operates efficiently.
As we discuss in more detail in the article below, among house fires that occurred during 1998, approximately 15,600 fires, including 20 deaths and 370 injuries were traced to clothes dryer fires. And a clothes dryer whose venting is blocked will require much longer operating time to actually dry the clothes, increasing dryer operating costs as well.
How Proper Clothes Dryer Vent Duct Installation Saves Energy & Lowers Clothes Dryer Operating Costs
Our clogged dryer vent duct photo shown at left illustrates just how much lint can collect inside of even a smooth metal duct over the course of years of dryer use.
Any defect that restricts air flow through the clothes dryer exhaust vent system, by slowing the flow of air through the dryer intake, through the wet contents of the dryer, and out through the exhaust vent, increases the length of time that the dryer has to operate before the clothing or other dryer contents will be adequately dried.
Longer dryer operating time means higher energy costs for the laundry system. We have seen laundry dry time decreased by as much as 75% when we replaced a clogged flex-duct dryer vent with an open, clean, straight and smooth metal duct system.
Clothes Dryer Inspection Checklist
31 Signs that a clothes dryer vent or laundry vent installation is unsafe or improper
CPSC's List of Clothes dryer fire hazards: Signs that a clothes dryer vent or laundry vent installation may have problems or risk a fire include:
Our photo above-left shows an upper floor clothes dryer vent through a building gable end wall. The lint on the roof below the vent opening may not itself be a problem but its presence made us worry that because this vent opening is difficult to access the system could easily become clogged with lint, leading to higher dryer operating costs and risk of a building fire.
Proper clothes dryer exhaust venting installation, routing, materials, and lint screening are important to prevent building fires, excessive clothes drying time and dryer operating costs, moisture damage buildings, decay, rot, or insect attack on the structure, saturation of building insulation, and building mold contamination.
The U.S. CPSC clothes dryer lint fire study (2003) notes these details about fire hazards common in clothes dryers:
The temperatures measured inside the heater box, heater intake, and intake into the
tumbler increased when the exhaust vent was partially blocked or fully blocked. The
temperatures inside the tumbler, blower and exhaust vent decreased when the
exhaust vent was partially blocked or fully blocked.
When the exhaust vent was 75 percent or 100 percent blocked, temperatures
in certain areas inside the dryer increased significantly.
Seals in the dryer’s interior exhaust venting may not be adequate to prevent linty air
from escaping into the dryer’s interior.
Lint that accumulates on the heater housing can easily ignite under conditions of a
failed high-limit thermostat and a blocked exhaust vent. Lint accumulating near the heater intake can ignite before the high-limit thermostat
switches the heater element off. Lint ingested by the heater and embers expelled from the heater outlet can easily
ignite additional lint or fabric in the air stream, resulting in additional embers in the
dryer system and exhaust vent.
The high-limit thermostat may prematurely fail when subjected to high ambient
[Click to enlarge any image]
The clothes dryer safety sketch at above-left (US CPSC ) illustrates a typical clothes dryer installation and outlines a number of fire and safety recommendations.
Let's look at clothes dryer venting hazards in more detail:
Other signs of laundry dryer vent system troubles & safety hazards
Burning smells or odors: if you see smoke or if you smell a burning odor near the dryer or at the dryer vent termination opening at the building exterior you are risking a building fire. Watch out: turn off the clothes dryer (and any booster fans) immediately. Then check further for evidence of fire, heat, smoke. If you suspect that there is an actual fire, get everyone out of the building and then call your fire department.
Visibly blocked laundry dryer vent screen openings at the dryer duct outlet.
Our photo above illustrates what we found during a building addition project when we opened the dryer vent hood that had been mounted on a low slope roof. The dryer duct was nearly 100% blocked with lint. The homeowners had been operating their dryer only on its "low heat" setting for several years after observing that the clothing was always very hot at the end of the dryer cycle.
Check that the clothes dryer vent terminating screen is not blocked and check that movable flaps or other parts that should open when the dryer is in operation do in fact open fully.
See CLOTHES DRYER WALL VENT SCREENS
Booster exhaust fans for clothes dryer venting and auxiliary or secondary lint filters on clothes dryers are permitted and can improve dryer performance, reduce lint accumulation, and can permit longer dryer vent duct runs. Check with your dryer manufacturer and your local building official before adding such devices.
In any case, a dryer vent system and booster fan requires periodic inspection and maintenance (cleaning). If you hear buzzing or other noises at the vent fan it's probably in trouble and needs attention.
See CLOTHES DRYER VENT BOOSTER FANS for details.
and Watch out: if a clothes dryer system is relying on a draft boosting fan for safe operation (say for a long dryer vent duct run or a run with many bends), be sure that the fan is operational. Otherwise the system is unsafe.
Clothing is still damp at the end of a dryer cycle of normal duration or abnormally long time required for clothes to dry.
Crushed or crimped flexible dryer vent ductwork or sagged dryer ductwork collects moisture, water, lint, and obstructs air flow. An operating defect like the squashed flexible metal dryer duct shown above is a fire hazard. Take a look behind the dryer at the condition of the duct and its connections.
See CLOTHES DRYER VENT DUCT MATERIALS
Dryer exhaust vent disconnected: check the back of the dryer: if the exhaust vent has become disconnected you'll probably see lint blowing all over the place. But if the exhaust vent has become disconnected elsewhere in its routing to the building exterior you may miss that potentially dangerous condition unless you inspect the entire run. Start by checking for good dryer air output at the exterior side of the dryer vent termination. If airflow is weak there the system is unsafe.
Dryer exhaust vent under-sized: the clothes dryer vent diameter should be no smaller than 4" in diameter or the size of the dryer outlet. An under-sized dryer exhaust vent restricts air flow, overheats the dryer, and may be unsafe.
Dryer exhaust vented into the building interior: In addition to avoiding venting in to attics or crawl areas, you also should not vent the dryer exhaust into any interior room nor into a wall cavity.
Dryer exhaust vented into a chimney or into HVAC ductwork: don't do it. Venting a clothes dryer into a chimney is unsafe, risking fire or fatal carbon monoxide poisoning. Venting a dryer into HVAC ductwork clogs the HVAC system and also risks blockage and fire in both systems: the dryer and the HVAC air handler.
Hot dryer venting or hot clothing: Noticeably hot clothing found at the end of the clothes dryer operating cycle indicated a clogged lint filter, clogging in the dryer's air flow passages, or possibly a clogged outlet vent: all fire hazards.
Increased or excessive clothes dryer operating time needed to actually dry the laundry
Weak air flow: Feeling at the dryer exhaust vent outdoors you do not see that the vent is opening when the dryer is operating, is not opening fully, or has weak air flow. Also note that the vent should close when the dryer stops operating.
Sagged flex-ducting used for laundry dryer vent ducting collects lint and possibly condensation - water. The blocked duct invites a dryer fire.
Tears, holes, punctures in flex-duct dryer vent material
Lint filter missing or clogged in the clothes dryer. Do not operate a clothes dryer without the lint filter in place as that accumulates lint inside the dryer body, increasing the risk of a clothes dryer fire. And remember to clean the dryer's built-in lint filter at each dryer use. Failure to keep the dryer lint filter clean increases the dryer temperature, possibly to unsafe levels, and by blocking air flow it also increases the time required to dry clothes, thus increasing the dryer's operating cost.
Lint on surrounding building surfaces near the dryer vent termination may mean that the vent is becoming blocked with lint/debris
Lint and debris collecting behind and around the clothes dryer may indicate that its exhaust vent is blocked.
Lint build-up inside the dryer and at the dryer back or bottom can not only obstruct air flow but such blockages form a common fire hazard. A blocked dryer exhaust vent forces lint back into the dryer where it accumulates.
Lint clogging at the dryer vent flap or louvered opening can prevent the louver from closing fully, inviting rodents, birds or other pests into the dryer duct system: a fire hazard. Check that the flapper door or louvers close fully and if they don't clean away lint with a soft brush. Below I'm checking for lint blockage of the two louvers that close this dryer vent terminal when the dryer stops: I want the louvers to open and close freely (opening to vent fully and closing to make it harder cold air or worse, cold animals to invade the duct system). You can see two clean streaks at the bottom of the metal duct just inside the opening: I wiped away lint to estimate its thickness in the dryer vent system.
Lint trap is installed on the dryer vent system. Lint traps are potential fire hazards.
Long clothes dryer venting duct runs or too many elbows or bends in the dryer ducting may violate the clothes dryer manufacturer's installation guide and warranty and may be a fire hazard as well as causing overheating or longer dryer run times and increased dryer operating cost. Most manufacturers want the dryer vent run length to be 25 feet or less. In calculating the clothes dryer vent run length, reduce the allowable total distance from dryer outlet to exterior wall vent by 5 feet for each 90 degree elbow and by an additional 2.5 feet for each 45 degree elbow in the vent duct system. You can exclude the "transition duct" or periscope (if used) that connects the dryer outlet to the exhaust duct system itself.
Note: Fantech notes that "The 2012 International Residential Code (IRC) is pretty specific when it
comes to dryer exhaust venting. The maximum length for dryer exhaust duct
cannot exceed 35 feet from the dryer location to the wall or roof termination. " (Fantech 2012).
Note: some high power and commercial clothes dryers are rated for "long dryer vent runs" and may handle longer vents than 25 ft.
Screws in the dryer vent connections that protrude into the vent or duct interior are not an approved duct connection method as lit collecting on those points can clog the system: a fire hazard. Use a foil or metal duct tape instead. Where dryer vent duct support is needed use external strapping or clamps.
See DRYER VENT INSTALLATION
Stains, thermal tracking, or mold growth on bathroom walls and ceilings, possibly also on bath vanities and cabinets in areas where dryer exhaust or moisture are accumulating
Nearby window condensation, and frost forming on windows during freezing weather, especially when the clothes dryer is in use
Frost or moisture condensation found in the building crawl space, basement, attic on the roof underside or other areas through which the dryer vent has been routed or where dryer vent air is being exhausted
Wrong dryer venting material: Beers (2003) points out that the common flexible white vinyl ducting sold at some outlets for dryer venting does not meet the Underwriters Laboratory Standard for dryer venting and is a fire hazard. UL required metal (or flexible metal) clothes dryer venting. Such flexible vinyl dryer ducting may also violate the dryer warranty. Metal dryer vents should be made of aluminum, stainless steel, or galvanized steel. Recommendation: use only clothes-dryer manufacturer-approved and in Canada CSA approved, or in the U.S. U.L. listed/approved clothes dryer vent ducting and duct closures or doors.
See CLOTHES DRYER VENT DUCT MATERIALS
Dryer vent sections installed wrong-way: metal dryer vent sections should be connected with the male or "inserted" end of each vent section at the outlete or downstream end of the exhaust vent. This ordering reduces the catchment of lint on to the exposed ends of the dryer vent sections inside the duct system. In our photo above the duct sections have been assembled in the proper order: you can see that lint is not collecting at the intersection of the male and female duct section ends (yellow arrow). Though we are also a little worried about screw or pop rivet intrusions into the duct system (orange arrow) we see no lint stuck on that fastener. I suggest that placing ducts in the right male-female orientation may be more significant in slowing the rate of dryer lint clogging.
Dryer vent terminates too close to other mechanical systems or building features such as a gas meter. Keep the exhaust vent at least 3 feet away from a gas meter or other outdoor mechanicals including electrical receptacles.
Safe & Effective Installation of Clothes Dryer Exhaust Vent Ducts
Lint blockage and clogging often occurs right at the dryer vent opening, particularly if there is a screen over the opening (an improper installation), causing longer dryer operating times and possibly overheating and a dryer fire. In addition some dryer vent terminations and covers, particularly those that rely on a flapper (photo above) that is opened by the moving exhaust air, can become stuck in the open position, inviting dangerous vent line clogging by entering birds or insects.
Air-Operated Exterior Wall Vents for clothes dryer vent lines are available at hardware stores, building suppliers, and from some online sources.
These devices use a movable plastic cylinder that lifts to permit venting of the laundry dryer exhaust when the dryer is operating.
Also see DRYER VENTING FAQs for more about dryer vents that resist lint clogging, and about use (or recommendations against using) supplemental lint filters in dryer vent and duct systems.
Fire Hazards from Clogged or Improperly-Installed Clothes Dryer Vents
Watch out: Clothes Dryer Lint Traps: like the unit illustrated above and sold a variety of manufacturers and online stores are intended to be installed somewhere between the clothes dryer outlet and the dryer vent outlet - these are are also not recommended in some dryer installation manuals, are prohibited by some building codes, and can similarly cause overheating and fires.
Research on Clothes Dryer Venting, Insect Pests, & Building Moisture: relationships
APPLIANCES, BARBECUE. "Clothes Dryer." Transfer 403 (1996): 2.
Beers, Jonathan. "Dryer Venting." HOME ENERGY 20, no. 6 (2003): 14-16.
This article notes that " Once a fire starts, the plastic vent hose burns, spreading the fire."
Brook, David M. Home moisture problems. [Corvallis, Or.]: Oregon State University, Extension Service, 1994.
Cheung, Kisuk. Engineering and Design: Clothes Dryer Exhaust Venting. No. ETL-1110-3-483. CORPS OF ENGINEERS WASHINGTON DC, 1998.
Abstract: This letter provides basic design guidance for exhaust venting systems for residential-type electric and gas clothes dryers.
Flynn, Jennifer D. US Structure Fires in Nursing Homes. National Fire Protection Association, 2008.
Franklin, Frederick F. "Survey of electrical fires." FIRE J. 78, no. 2 (1984): 41-44.
Geis, Aelred D. "Effects of building design and quality on nuisance bird problems." (1976).
Hayden, A. C. S. "Residential combustion appliances: venting and indoor air quality." Environmental progress 7, no. 4 (1988): 241-246.
Hoddenbach, Gerard, Jerry Johnson, N. P. S. Chief, and Carol DiSalvo. "RODENT-EXCLUSION MANUAL."
NFPA, "Dryer Safety Tips", Nationbasl Fire Protection Association (2013), retrieved6 Aug 2015, original source: http://www.nfpa.org/safety-information/for-consumers/causes/dryers-and-washing-machines/dryer-safety-tips
Sherman, Max H. "ASHRAE and residential ventilation." Lawrence Berkeley National Laboratory (2003).
Timm, Robert M., and Gerald R. Bodman. Rodent-proof Construction: Structural. Cooperative Extension, Institute of Agriculture and Natural Resources, University of Nebraska-Lincoln, 1983
U.S. CPSC, "Final Report on Electric Clothes Dryers and Lint Ignition Characteristics - May 2003", [PDF] cpsc.gov, original source: http://www.cpsc.gov/pagefiles/117075/dryer.pdf
Excerpts: In FY 2002, U.S. Consumer Product Safety Commission staff completed a test program
to evaluate residential electric clothes dryers under various test conditions. The test
program included measurements of temperature and airflow characteristics for different
electric clothes dryer designs under normal operating conditions and conditions of
partially-blocked and fully-blocked exhaust ducting. The ignition characteristics of lint in
relation to electric clothes dryer operation were also evaluated. The test program
produced data on different dryer operating and design characteristics that can be used
to help reduce the risk of lint ignition in a clothes dryer and help prevent fires.
The experiments described in this research report were undertaken to support future
advances in clothes dryer safety. This report should not be used to suggest that current
clothes dryers are unsafe or defective....
CPSC staff tested clothes dryers to evaluate the effects of lint accumulation and abovenormal
operating temperatures and determine whether such conditions may result in lint ignition
and/or dryer fires. The data was used to help determine if dryer fires result from a single event
or a combination of events....
The results of the CPSC staff tests showed that lint that accumulates inside the dryer
can ignite if the lint contacts certain areas of the heater housing, if the lint is in proximity to the
heater, or if the lint is ingested by the heater box.
Wijayasinghe, Mahendra. "Fire losses in Canada: Year 2007 and selected years." (2011).
Wright, Frank Lloyd. "Environmental Barriers." New York Times (1953).
Questions & Answers on bathroom vent fan and fan ducting installation procedures, codes, standards.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
 "Overheated Clothes Dryers Can Cause Fires, CPSC Document # 5022 Updated June 2003", U.S. Consumer Product Safety Commission, www.cpsc.gov., websearch 11/25/2011, original source: cpsc.gov/cpscpub/pubs/5022.html
 "Electric and Gas Clothes Dryers, Staff Evaluation and Contractor Report", US CPSC Memorandum, 25 Feb 2000
"Report on Electric and Gas Clothes Dryers", U.S. CPSC Memorandum, 25 Feb 1999, the Clothes Dryer Project, March 1999
 UL Standard 2158, voluntary standard for electric clothes dryers
 ANSI Z21.5 1 (CGA 7.1) voluntary safety standard for gas powered clothes dryers
 "Healthy Indoor Air for America's Homes, Indoor Air Hazards Every Homeowner Should Know About - room by room assessment", U.S. Government Publications, web search, 11/30/2011, original source: http://publications.usa.gov/epublications/indoorair-hazards/assessment.htm More about this information source, quoting the US Government website: ... Federal Citizen Information Center (FCIC) has been a trusted one-stop source for answers to questions about consumer problems and government services. FCIC, part of the General Services Administration's Office of Citizen Services and Innovative Technologies, has traditionally provided publications to consumers via the publications distribution center in Pueblo, Colorado. The Pueblo.GSA.gov website was where consumers could go to find information and order publications on a variety of topics from the federal government. Publications.USA.gov replaces the former Pueblo.GSA.gov.
 "The Facts About Clothes Dryer Exhaust Systems", John Cranor, the ASHI Reporter, April 2005,American Society of Home Inspectors,® Inc., 932 Lee Street, Suite 101, Des Plaines, Illinois, 60016, Tel: 847-759-2820, website: ashi.org, original source: ashireporter.org/articles/articles.aspx?id=161
 Tjernlund Residential Capacity Dryer Duct Booster®, "Dryer Duct Booster Fan Model LB1, Installation Instructions" [PDF], Tjernlund Products, 1601 9th Street
White Bear Lake, MN 55110-6794 , (800) 255-4208, web search 01/06/2012, original source: tjernlund.com/dryer_booster.htm Quoting:
The Dryer Duct Booster®, Model LB1, has been specifically designed to boost residential capacity clothes dryer duct exhaust velocities
where dryer duct runs exceed 25 equivalent feet. Proper exhaust velocities will reduce drying times, save energy and prevent lint
buildup in the dryer duct. The LB1 is controlled by an electronic Pressure Response Control (PRC) for automatic operation. The LB1
utilizes galvanized steel construction, a reverse inclined, particulate handling impeller that is guaranteed not to clog with lint and
an externally mounted PSC motor for trouble-free operation.
"About the House - Bathroom Vents", Henri deMarne, New England Builder, November 1985
"Bathroom Vent Fan Beats Open Window", James Dulley, Poughkeepsie Journal, 11/4/1987 p. 12D.
Mark Cramer Inspection Services Mark Cramer, Tampa Florida, Mr. Cramer is a past president of ASHI, the American Society of Home Inspectors and is a Florida home inspector and home inspection educator. Mr. Cramer serves on the ASHI Home Inspection Standards. Contact Mark Cramer at: 727-595-4211 mark@BestTampaInspector.com
John Cranor is an ASHI member and a home inspector (The House Whisperer) is located in Glen Allen, VA 23060. He is also a contributor to InspectApedia.com in several technical areas such as plumbing and appliances (dryer vents). Contact Mr. Cranor at 804-747-7747 or by Email: firstname.lastname@example.org
Eric Galow, Galow Homes, Lagrangeville, NY. Mr. Galow can be reached by email: email@example.com or by telephone: 914-474-6613. Mr. Galow specializes in residential construction including both new homes and repairs, renovations, and additions.
References for Bathroom Vent Fan Installation:
Fantech Installation, Operation, and Maintenance Manual, PB Series Premium Bath Fans. These fan models use a remote fan motor and
are available in 4" duct and 6" duct models. Web search 7/26/11 - original source http://fantech.net/docs-resi/412889-pb-install.pdf
Fantech in the United States
10048 Industrial Blvd.,
Lenexa, KS 66215
Phone: 800.747.1762; 913.752.6000
Fax: 800.487.9915; 913.752.6466
Fantech in Canada
50 Kanalflakt Way,
Bouctouche, NB E4S 3M5
Phone: 800.565.3548; 506.743.9500
Fax: 877.747.8116; 506.743.9600
Nutone Bathroom Exhaust Fan/Light Combination Installation Instructions, Model 8663RP, 8673RP, 8664RP suitable for use
in shower or tub enclosure when used with GFCI protected branch circuit. Suitable for use in insulated ceilings.
Nutone, 4820 Red Bank Road, Cincinnati, Ohio 45227, web search 07/27/2011, original source:
Books & Articles on Building & Environmental Inspection, Testing, Diagnosis, & Repair
The Home Reference Book - the Encyclopedia of Homes, Carson, Dunlop & Associates Ltd., Toronto, Ontario, 2010, $69.00 U.S., is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. InspectAPedia.com ® author/editor Daniel Friedman is a contributing author. Field inspection work
sheets are included at the back of the volume.
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: firstname.lastname@example.org. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones
Support InspectApedia.com & See Fewer Advertisements
From Google's Contributor website: Contribute a few dollars each month. See fewer ads. The money you contribute helps fund the sites you visit.