Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
VENTILATION in BUILDINGS
Bathroom exhaust fan termination fittings, locations, & clearance distances: this article describes the proper closure or termination of bathroom exhaust fans & fan ducts to prevent drafts, heat loss, leaks, or even bird or rodent pest entry to the building. We also review recommended clearance distances between the bath exhaust duct end opening and other building features such as a gas fired water heater exhaust opening.
This article series explains how to install bathroom exhaust fans or vents, the vent ducting, the vent termination at the wall, soffit or roof, vent fan wiring, bath vent duct insulation, bath vent lengths, clearances, routing, and we answer just about any other bathroom ventilation design or installation question you may have.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Our photo at left and two additional examples seen at below left show two typical bath vent fans that spills directly into each building's attic - both are improper vent fan installations.
Terminate the bath vent duct outside at gable end or eaves: horizontally through the building wall at a building gable-end wall (first choice), or if the gable end is too distant, terminate the bath vent down through a building soffit at the roof eaves.
Don't just blow the bath (or kitchen) vent exhaust into an attic, nor, even more crazy, into a ceiling or wall cavity or into a crawl space.
If you were not convinced that failure to properly spill bath vent air and moisture outside can lead to attic mold, notice our photo (below left).
Reader Question: what kind of ductwork can be used to terminate the run of piping from the fan to the soffit?
For soffit ventilation, what kind of ductwork can be used to terminate the run of piping from the fan to the soffit? Does the existing soffit mesh of a newer home need to be cut away and replaced with some other register, or will the existing mesh allow a 110cfm fan to operate efficiently? Thanks, great site! - Anonymous
When we install a vent fan out through an attic and down out of the soffit, we like to use solid metal ductwork (photo above left) to maximize air flow and minimize resistance, keeping the run as short as possible. Certainly use of flexible metal ducting and even plastic flex duct are permitted in many jurisdictions but in our opinion those are less effective choices.
In my photo at above left we had not yet trimmed the metal duct to proper length to protrude through the roof overhang or eaves at the proper distance to fit the vent opening cover )shown at above right). That device is automatically opened by pressure of the exhaust fan and snaps shut when the fan is off, avoiding possible back drafts through the bath exhaust vent fan system.
If you just drop the end of the duct into the soffit bay that is in turn covered by perforated panels, I worry that a substantial portion of moisture and vented air will just blow back into the attic.
Venting bath fans through up the roof surface?: While we agree that building exhaust ventilation is most powerful and thus effective when it is routed vertically, we prefer to avoid venting bath fans up through the roof, both to avoid an extra roof penetration (and leak risk) and to avoid condensate leaks into the bathroom ceiling.
Terminating exhaust fan duct at the ridge vent: our photo (above left) shows a typical attempt at venting a bath into or actually just below a ridge vent - this direction of vent exit may seem convenient but we don't like it much. In the photo (left) the droopy flex-duct will certainly invite bath moisture to condense and run back to the home's ceiling rather than exiting at the ridge. Snow cover on the ridge will prevent this vent from working.
Terminating exhaust fan duct on the roof surface: at above-right we show an ugly bathroom exhaust vent installation through the roof surface using a laundry dryer sidewall vent cover. Not only were the roof shingles torn up and sealed again to leave a leak-risk around the vent penetration of the roof surface, but because this roof exhaust vent was installed on a home in a snow-climate, in winter with snow cover on the roof the vent is likely to be blocked.
Venting a bath exhaust fan straight up: Our sketch shows a bath vent fan exiting up through the roof.
Considerations when venting a bathroom exhaust fan straight up are discussed at BATHROOM VENT THROUGH ROOF
A direct through-wall bath vent fan design may be preferable if the building roof shape, bath location, or other details make it difficult to exhaust a ceiling-mounted bathroom exhaust fan.
In other words, some bathroom locations and designs such as first floor baths in a multi-story home, are vented out thorough the building sidewall not up through the attic.
Do not vent bath fans into a crawl space: you're only putting more moisture into an area where it is already going to be a problem, inviting mold growth on wood surfaces and hidden mold growth in building insulation.
At DRYER VENTING we discuss the horrible crawl space shown at left. Below this home the clothes dryer, bath vent fans, and even a dishwasher drain all were dumping into a soaking wet crawl space below the building.
The mold contamination, mud, and stink were horrible.
Soaking a crawl space or attic also wets the insulation, ending its effectiveness and asking for more mold contamination (Mold in Fiberglass Insulation.)
Protect the bath fan duct outlet at the building exterior, using approved screening or a louvered fitting so that you do not invite birds or rodents into the building through the ductwork.
While we don't want a (lint collecting) screen over a clothes dryer vent termination (that's a fire hazard) we do screen bath or kitchen exhaust vent terminations to keep out birds, bats, and rodents.
Our photo (left) illustrates a self-closing bath vent termination in a soffit; when the bathroom vent fan is in operation this cover opens to exhaust moist air; the cover closes by gravity or a light-weight spring when the blower fan is not operating, thus avoiding any cold air back-drafts into the building.
See CLOTHES DRYER VENTING for examples of vent duct terminations, screens, and safety concerns.
Question: 5/15/14 Kevin said: restrictions on how close a bath vent can be to water heater sidewall vent?
Are there any restrictions on how close an exhausting bath vent may be placed to an exhausting vent for a gas water heater? Both exhaust vents will terminate outside through a side wall. Thanks.
Clearances for gas fired appliance sidewall vent terminations are given in detail at DIRECT VENTS / SIDE WALL VENTS
You will see that the required distances range from 1 foot to 7 feet depending on what's being cleared-from.
If the bath exhaust fan vent termination location respects the gas fired exhaust (chimney / flue) vent clearances you should be ok.
Question: minimum clearance from bathroom window to exhaust fan outlet
(Apr 9, 2014) Ryan said:
If I ran my bathroom exhaust fan duct outlet out of my soffit is there any minimum clearance from the bathroom window so it will not draw in the odors if someone happened to open the window. My house came with a bathroom exhaust fan that automatically turns on when the overhead shower light is turned on. Right now it vents into the attic (bad) and I want to vent it out the soffit(good)
Ryan you'd want to be 10 feet from the nearest operable window if you want to avoid odor intake; that is not a code specification it's an opinion.
Continue reading at BATHROOM VENT DUCT PROTECTION
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
References for Bathroom Vent Fan Installation