InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Bath vent fan slope: this article describes the recommended slope direction on bath exhaust fan ducts to avoid icing and related building leaks.
This article series explains how to install bathroom exhaust fans or vents, the vent ducting, the vent termination at the wall, soffit or roof, vent fan wiring, bath vent duct insulation, bath vent lengths, clearances, routing, and we answer just about any other bathroom ventilation design or installation question you may have.
Bath vent fan duct slope: Bath fan vent ducting in most installations is sloped gently back towards the bathroom. Especially where flex-duct is used, it is important to to avoid a low spot that collects condensation moisture in the attic.
Not only does such accumulation risk leaks into the ceilings (mold hazards) but in freezing climates water accumulating in duct work can freeze, accumulate further, block the duct, and when temperatures rise, cause extensive leakage back into the building.
We like to slope the bath fan vent duct downwards towards its building exit in non-freezing climates or where insulation protects against freezing. This will avoid condensation accumulating inside the ductwork and dripping back into the building ceilings or insulation. We illustrate a down-sloped bath vent duct installation in this article.
Question: ice accumulation around the bath vent cover on the outside wall
I have a brand new house that was built last summer. I noticed that the bathroom vents right below the roof line on the wall. The problem is there's an ice accumulation around the vent cover on the outside wall.
This does not seem normal to me, or is it? I should specify that I haven't even started using this washroom yet, since my shower has not yet been installed. I went up in the attic and they used a flexible vent and there's insulation on top of it. Is heat loss normal when the fan is not operating? Could this be the cause of the ice buildup outside at the vent cover? - Marc
Marc, it sounds as if warm moist air is exiting at the vent and you're seeing ice accumulation as a result. I agree that we don't want house air venting itself through the bath vent duct when the bath vent fan is not even running = that's an unnecessary heat loss.
But if the ductwork is routed all sloping "up" from the vent fan location this might happen, in particular if the bath vent fan system does not include an automatic closing mechanism indoors or outside at the wall. Take a look at the vent on the exterior wall (if you can safely do so in this weather and at that height) - see if there is a closing mechanism?
Question: moisture condensation on & in the bath vent connector tube that terminates outside. Why?
(Apr 15, 2014) Bill said:
I vented my bathroom fan to the side of the house. Condensation is building on the inside and outside of the connector tube that terminates outside. Why?
Bill I've thought about this for a while without dreaming up a magically clever response. Condensation means temperature differences and the presence of moisture. Warmer, moisture laden air gives up moisture that is deposited on the cooler surface.
So if by "why" you don't ask for theory but for a diagnosis we'd need to look at the home to see where moisture is present, and where temperatures differ. Perhaps also look for missing insulation.
You can handle condensation on the fan duct surfaces by these approaches:
Reduce indoor moisture levels - which is nonsense if we're talking about a bath vent fan that is specifically intended to exhaust moisture to outside of the building
Watch out: Keep in mind that moisture forming on the outside of the bath exhaust fan duct must be coming from moisture-laden air in the area where the duct is routed. If you are seeing lots of moisture on the exterior of a bath exhaust fan duct I'd be worried that shower moisture is entering the ceiling or other building cavity when it should not. Look for leaks at light fixtures, around the fan fixture, at electrical receptacles, etc. Then look for other moisture sources (such as roof leaks).
Insulate the exhaust fan duct - Insulation on the exterior of a bath exhaust fan duct prevents moisture from forming on the duct exterior, as you are preventing the temperature of the exterior from reaching the dew point.
Proper exhaust fan duct material & slope - moisture may form inside the fan duct because of the combination of high moisture-content air being vented to outside (say from shower steam entering the fan), along with cool duct surfaces (say from a duct running through a cool attic or wall space).
In addition to insulating the fan duct to reduce the condensation rate on both interior and exterior surfaces (insulation should be placed only on the outside of such exhaust ducts), use of smooth surfaced solid metal avoids little depressions where condensate can accumulate (and leak into the building), and sloping the duct properly (back towards the bathroom as discussed in the article above), will avoid water and ice accumulation at the exhaust duct termination.
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Eric Galow, Galow Homes, Lagrangeville, NY. Mr. Galow can be reached by email: firstname.lastname@example.org or by telephone: 914-474-6613. Mr. Galow specializes in residential construction including both new homes and repairs, renovations, and additions.
"Panasonic® Ventilating Fan Installation Instructions, FV-05VQ3, FV-08VQ3, FV11VQ3, FV-15VQ3", X120-4-8189Panasonic Consumer Electronics Co., Div. of Panasonic Corp. of North America, One Panasonic Way, Seacaucus NJ 07094 & Panasonic Canada, Inc., 5770 Ambler Dr., Imssissauga, ON L4W 2T3, Website: www.panasonic.com, retrieved 4/7/14
"Brink Renovent HR Installation and Operation Manual", Brink Climate Systems, P.O. box 11
NL-7950 AA Staphorst
+31 522 46 99 44
www.brinkclimatesystems.nl retrieved 4/7/14 This is the installation guide for medium & large Brink Renovent HR systems.
"Installation Instruction, Heat Recovery Unit, Renovent Small", Brink Climate Systems, P.O. box 11
NL-7950 AA Staphorst
+31 522 46 99 44
www.brinkclimatesystems.nl retrieved 4/7/14 This is the installation guide for the small Brink Renovent HR system. [copy on file]
"About the House - Bathroom Vents", Henri deMarne, New England Builder, November 1985
"Bathroom Vent Fan Beats Open Window", James Dulley, Poughkeepsie Journal, 11/4/1987 p. 12D.
References for Bathroom Vent Fan Installation
Fantech Installation, Operation, and Maintenance Manual, PB Series Premium Bath Fans. These fan models use a remote fan motor and
are available in 4" duct and 6" duct models. Web search 7/26/11 - original source http://fantech.net/docs-resi/412889-pb-install.pdf
Fantech in the United States
10048 Industrial Blvd.,
Lenexa, KS 66215
Phone: 800.747.1762; 913.752.6000
Fax: 800.487.9915; 913.752.6466
Fantech in Canada
50 Kanalflakt Way,
Bouctouche, NB E4S 3M5
Phone: 800.565.3548; 506.743.9500
Fax: 877.747.8116; 506.743.9600
Nutone Bathroom Exhaust Fan/Light Combination Installation Instructions, Model 8663RP, 8673RP, 8664RP suitable for use
in shower or tub enclosure when used with GFCI protected branch circuit. Suitable for use in insulated ceilings.
Nutone, 4820 Red Bank Road, Cincinnati, Ohio 45227, web search 07/27/2011, original source:
"Energy Savers: Whole-House Supply Ventilation Systems [copy on file as /interiors/Energy_Savers_Whole-House_Supply_Vent.pdf ] - ", U.S. Department of Energy energysavers.gov/your_home/insulation_airsealing/index.cfm/mytopic=11880?print
"Energy Savers: Whole-House Exhaust Ventilation Systems [copy on file as /interiors/Energy_Savers_Whole-House_Exhaust.pdf ] - ", U.S. Department of Energy energysavers.gov/your_home/insulation_airsealing/index.cfm/mytopic=11870
"Energy Savers: Ventilation [copy on file as /interiors/Energy_Savers_Ventilation.pdf ] - ", U.S. Department of Energy
"Energy Savers: Natural Ventilation [copy on file as /interiors/Energy_Savers_Natural_Ventilation.pdf ] - ", U.S. Department of Energy
"Energy Savers: Energy Recovery Ventilation Systems [copy on file as /interiors/Energy_Savers_Energy_Recovery_Venting.pdf ] - ", U.S. Department of Energy energysavers.gov/your_home/insulation_airsealing/index.cfm/mytopic=11900
"Energy Savers: Detecting Air Leaks [copy on file as /interiors/Energy_Savers_Detect_Air_Leaks.pdf ] - ", U.S. Department of Energy
"Energy Savers: Air Sealing [copy on file as /interiors/Energy_Savers_Air_Sealing_1.pdf ] - ", U.S. Department of Energy
Fiberglass: Indoor Air Quality Investigations: Health Concerns About Airborne Fiberglass: Fiberglass in Indoor Air from HVAC ducts, and Building Insulation
Humidity: What indoor humidity should we maintain in order to avoid a mold problem?
Re-Bath, tub lining products is a bath tub relining manufacturer and distributor located in Tempe, Arizona - see rebath.com
Books & Articles on Building & Environmental Inspection, Testing, Diagnosis, & Repair
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: email@example.com. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones
Support InspectApedia.com & See Fewer Advertisements
From Google's Contributor website: Contribute a few dollars each month. See fewer ads. The money you contribute helps fund the sites you visit.