Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ENVIRONMENTAL HAZARDS - INSPECT, TEST, REMEDY
ACOUSTICAL SEALANT CHOICES
AGE of a BUILDING - how to determine
AIR BYPASS LEAKS
AIR LEAK DETECTION TOOLS
AIR LEAK MINIMIZATION
AIR LEAK SEALING PROCEDURE
AIR POLLUTANTS, COMMON INDOOR
ALLERGENS in BUILDINGS, RECOGNIZING
ANIMAL ALLERGENS / PET DANDER
APPLIANCE EFFICIENCY RATINGS
ARCHITECTURE & BUILDING COMPONENT ID
ASBESTOS CEILING TILES, Asbestos-Containing
ASBESTOS CEMENT ROOFING
ASBESTOS CEMENT SIDING
ASBESTOS DUCTS, HVAC
ASBESTOS-FREE INSULATION MATERIALS
ASBESTOS IDENTIFICATION IN buildings
ASBESTOS FLOORING HAZARD REDUCTION
ASBESTOS FLOORING REMOVAL GUIDE
ASBESTOS LIST of PRODUCTS
ASBESTOS MATERIAL REGULATIONS
ASBESTOS MATERIAL REGULATIONS Update
ASBESTOS MATERIAL REGULATIONS, OSHA
ASBESTOS PHOTO GUIDE to Materials
ASBESTOS REMOVAL, Amateur, Incomplete
Asbestos Removal, Certification
ASBESTOS REMOVAL, Wetting Guidelines
ASBESTOS RISK ASSESSMENT
Asbestos Under the Microscope
ATTIC LEAKS, CONDENSATION & MOLD
BASEMENT HEAT LOSS
BUCKLED FOUNDATIONS due to INSULATION?
BUILDING NOISE DIAGNOSIS & CURE
CATHEDRAL CEILING INSULATION
CEILING FINISHES INTERIOR
CEILINGS, DROP or SUSPENDED PANEL
CEILINGS, PLASTER TYPES
CERAMIC TILE FLOOR, WALL
CERAMIC TILE, ASBESTOS in?
CHIMNEY INSPECTION DIAGNOSIS & REPAIR
CHINESE DRYWALL HAZARDS
DEW POINT CALCULATION for WALLS
EFFLORESCENCE, Salts & White / Brown Deposits
FIBERGLASS INSULATION MOLD
FLOOR TILE HISTORY & INGREDIENTS
FLOOR TILES ASBESTOS
FLOOR TYPES & DEFECTS
HEAT LOSS in BUILDINGS
HOUSE DOCTOR, how-to be
HUMIDITY LEVEL TARGET
ICE DAM PREVENTION
INDOOR AIR QUALITY IMPROVEMENT GUIDE
INSULATION FACT SHEET- DOE
INSULATION IDENTIFICATION GUIDE
INSULATION R-Values & Properties
METAL LATH, PLASTER & STUCCO
METHANE GAS SOURCES
MOISTURE CONTROL in BUILDINGS
MOLD: A COMPLETE GUIDE TO MOLD
Museum Artifact Preservation
NOISE / SOUND DIAGNOSIS & CURE
ODORS & SMELLS DIAGNOSIS & CURE
PAINT FALURE, DIAGNOSIS, CURE, PREVENTION
PLASTER & BEAVERBOARD & DRYWALL
PLASTER BULGES & PILLOWS
PLASTER LATH, METAL
PLASTER, LOOSE FALL HAZARDS
PLASTER TYPE IDENTIFICATION
PLASTER VENEER Best Practices
ROOF VENTILATION SPECIFICATIONS
SAFETY HAZARDS & INSPECTIONS
SEARS KIT HOUSES
SOUND CONTROL in buildings
Splits in Structural Wood Beams
STAIN DIAGNOSIS on BUILDING EXTERIORS
STAIN DIAGNOSIS on BUILDING INTERIORS
STUCCO WALL METHODS & INSTALLATION
STRUCTURAL DAMAGE PROBING
SWEATING (CONDENSATION) on PIPES, TANKS
Thermal Expansion Cracking of Brick
THERMAL EXPANSION of MATERIALS
THERMAL IMAGING, THERMOGRAPHY
THERMAL MASS in BUILDINGS
THERMAL TRACKING Indicates Heat Loss
VAPOR BARRIERS & CONDENSATION in BUILDINGS
VENTILATION in BUILDINGS
VINYL CHLORIDE HEALTH INFO
Volatile Organic Compounds VOCs
WALL CONSTRUCTION BARRIER vs CAVITY
WATER ENTRY in buildings
WINDOWS & DOORS
WINTERIZE A BUILDING
WOOD Burning Heaters Fireplaces Stoves
World Trade Center Collapse Dust Photos
Asbestos paper HVAC duct wrap identification & handling: as a visual aid to recognizing asbestos materials in buildings, this article describes and illustrates asbestos paper duct wrap that was usually applied to the exterior of metal heating ducts in buildings prior to 1970. We describe the difference between asbestos paper wrap or duct seal, asbestos pipe insulation, and hardcast asbestos lagging or plaster used on boilers and pipe joints. We discuss the PACM designation for asbestos materials and we offer general advice for options in handling asbestos paper duct seal and wrap.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved. Author Daniel Friedman.
Asbestos paper insulation used to Seal or Insulate Heating Ducts or Air Conditioning Ductwork Exterior Surfaces, Bends, Connections
This document assists building buyers, owners or inspectors who need to identify asbestos materials (or probable-asbestos) in buildings by simple visual inspection. We provide photographs and descriptive text of asbestos insulation and other asbestos-containing products to permit identification of definite, probable, or possible asbestos materials in buildings.
While an expert lab test using polarized light microscopy may be needed to identify the specific type of asbestos fiber, or to identify the presence of asbestos in air or dust samples, many asbestos-containing building products not only are obvious and easy to recognize, but since there were not other look-alike products that were not asbestos, a visual identification of this material can be virtually a certainty in many cases.
Also see ASBESTOS DUCTS, HVAC a field identification guide to visual detection of asbestos in and on heating and cooling system ducts and flue vents.
Examples of Asbestos Suspect Material Commonly Found on Heating and Air Conditioning Systems in buildings
We often see what may be asbestos containing insulating material on the heating system, including the following:
General advice about asbestos suspect paper wrap material on heating or cooling duct work: You should obtain proper technical information and health and safety guidelines before attempting to do anything with this material. It is the breathing of fibers when this material is disturbed, not it's mere presence, which is considered a health risk. When the material is not found in living areas in poor condition treatment is not usually an emergency and you have time to become informed, obtain estimates, and select an appropriate course of action.
If asbestos materials are inside the duct work, such as used for lining of a stud or floor joist bay which serves as an air duct, or perhaps where used as the vibration damper material connecting an air handler to the supply plenum of a system, because of the possible release of fibers continuously and directly into the path of moving air in the building, this material should be removed.
If asbestos materials have been disturbed inside a building without proper containment and cleanup, additional evaluation of the level of asbestos particles in building may need to be evaluated as additional expert cleaning might be needed.
Frequently Asked Questions (FAQs) About Asbestos Paper Duct Wraps & Seals or Insulation
Question: Unknown wrap on ductwork, I think it's asbestos hardcast wrap
I discovered this ductwork covered with this unknown wrap.
I know that the only way to know for certain is to have it tested, but there was nothing in the home inspection about it - assuming the inspector wasn't lazy and didn't lift the tiles - and there was nothing in the home seller disclosure about asbestos, so my gut tells me it's probably just hardcast wrap.
I would like to defer to more experienced eyes, however for a more informed opinion... Many thanks, M.B.
Reply: Definition of Hardcast Asbestos Insulation vs. Asbestos Paper Ductwrap, Definition of PACM, Modern Substitutes
That said, your photo looks very much like a metal HVAC duct that has been wrapped using an asbestos paper wrap. A few more photos of such material, information about the age of your home and its heating system design and history could increase our confidence in that conclusion, or of course you could test a small piece of the material.
At left we include another photograph of asbestos paper used on an old metal heating duct where the duct makes a 90-degreen turn to direct warm air up through the floor and into a room that is on the other side of the gypsum board partition wall shown in our photo.
I don't use the term "hardcast" asbestos for the material in your photo - I use the term asbestos paper ductwrap or seam wrap because the material is a thin (perhaps 1/8" or less) asbestos paper product, typically applied wet or dampened to allow installation around bends and to adhere to the metal duct surface.
I use the term "hardcast" asbestos to refer to an asbestos paste or "plaster" that was typically applied in a layer of about 1" or greater, used to completely or partially coat old hot water or steam boilers and used on heat distribution piping at elbows or valves. On heating and other piping installations a similarly thick corrugated asbestos paper wrap was used on the straight sections and sometimes on the boiler exterior and on occasion even in the interior of some warm air furnaces. See ASBESTOS PIPE INSULATION for more images of asbestos on piping.
Hardcast asbestos, when it needs to be removed, is usually handled following a number of asbestos remediation safety procedures (area signage, isolation, dust control, protective gear, etc) and with a "glove and bag method along with wetting, cleaning the exposed metal surfaces and sealing the cleaned surface as well.
Option 1: leave asbestos paper ductwrap in place, possibly covered or spray-sealed:
Best practice is to leave the material you show alone unless other building conditions or very poor condition require its professional removal. Some asbestos contractors use an encapsulant spray or paint where the paper wrap is to be left in place. As long as the asbestos paper is on the outside of supply ducts (ducts that are normally under neutral or positive air pressure) the chances that asbestos from the paper is entering the duct system and building air are very low. In my OPIION, should we find asbestos materials of any sort inside the duct system or air handler, that is a different (and more serious) concern.
Option 2: remove asbestos paper ductwarap, consider complete duct R&R:
If asbestos-paper wrapped duct seal/insulation does need to be removed for other reasons (building renovations, reconstruction, or materials in damaged, exposed, friable conditions), the removal is handled using asbestos remediation precautions, but more often it is much less expensive and an easier asbestos abatement job to remove the duct entirely, intact, from the building than it would be to try to remove just the paper wrap followed by duct cleaning. In sum, in most cases it will be easier and less costly to remove old asbestos-wrapped ducts and replace them with new ducts in the same area (if the ducts are still needed) than to try to clean and re-use the old ductwork.
Treat the Material as PACM - presumed asbestos containing material
This material is reasonably treated as "Presumed Asbestos Containing Material" or "PACM". Asbestos "hardcast" asbestos paper and paper tape were used as an air leak seal and slight insulating covering on metal heating ducts usually dating from before 1965 but may have been used up to around 1981.
Contemporary fireproof substitute products for asbestos cloth or paper used on HVAC ducts
A contemporary substitute for asbestos cloth and perhaps as a substitute for fireproof asbestos paper duct-wrap - that is if an application requires fireproof duct sealing material - and for asbestos paper tape (duct joint seal) used in high temperature operations is Silicone Hi-T, a waterproof and chemically waterproof and airtight and non-combustible (and ozone-resistant) flex-duct-connector tape available from Carlisle Coatings & Waterproofing, INc., 900 Hensley Lane, Wylie TX 75098, Tel: 800-527-7092, Website: www.hardcast.com [copy on file in our records as Hardcast-Hardware-Catalog-Final-25.pdf ] Carlisle C&W, under the brand name Hardcast(R) distributes a wide range of tapes and seam sealers.
Questions & answers or comments about how to identify asbestos paper sealant,coating, or insulation on heating ductwork.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.