Vacuuming Building Cavities to Screen for Hidden Mold: Guide to Good Practices
InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Guide to vacuuming building cavities to screen for particles, dust, or mold:
This article explains the advantages and shortcomings of using vacuum cassettes or spore traps to collect mold test samples (or other dust or particle samples) from building wall and ceiling cavities. In this article series discuss the validity of nearly all of the popular mold testing methods currently in use, pointing out the strengths and weakness of each approach to mold sampling in the indoor environment, beginning with air sampling for airborne mold levels indoors.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
Validity/Accuracy of Vacuuming Building Cavities for a Hidden Mold Screen
15th Annual North Carolina/South Carolina
Environmental Information Association Technical Conference
Myrtle Beach, SC
Daniel Friedman 23 September 2005, Updated 4/14/2009
Vacuuming building cavities is a popular screening practice to look for mold
reservoirs. The investigator is trying to explore wall cavities while doing
minimal or no visible damage.
A wall-check™ system has been marketed for this
purpose and several manufacturers have coped the basic idea: a receiving
Air-o-Cel™ or MCE filter cassette is attached at its inlet side to a tube which
is inserted as a probe into a wall cavity, permitting creation of only a small
hole. The outlet or pump side of the test device is connected to a pump and
operated, typically at 15 lpm. Where we have tested this method we have
experimented with both passive collection (what most investigators use) or
aggressive collection (banging on the wall/ceiling at various points to attempt
to dislodge and stir particles).
Short duration samples, 1-2 minutes using an Air-o-Cell ™ permit a
comparatively large number of samples to be collected in a reasonably short
interval. Long duration samples, perhaps for up to two hours, are collected
using an MCE filter cassette.
Wall Cavity Vacuuming - Found Ineffective
Working with Louis Relle, a Louisiana mold remediation expert on a New
Orleans Building which was to be demolished we collected wall-check samples from every suspect Building cavity.
building interior surfaces were demolished we then performed a visual inspection and collected bulk surface samples using tape.
See DUST / MOLD TEST KIT INSTRUCTIONS
The wall check samples were
completely unable to detect large and significant mold contamination in the cavities of this building.
We postulate that
even with mechanical agitation (banging on the wall during wall check sampling) the flow rate of the sampling method does
not move enough air to reliably pick up surface contamination unless the mold genera/species happens to be at a
particularly high state of active sporulation. The tool remains in the professional's arsenal, to be used with
Shortcomings of vacuuming building cavities through a tube but our testing
strongly suggests that this method is very unreliable for characterizing wall
contents. We do not believe that enough air movement is created in the wall
cavity (sucking any lpm flow through a small diameter tube) to reliably collect
what could be a severe mold reservoir that happens not to be right next to the
probe. Further if the cavity is insulated there will be virtually no air or
particle movement except from very close to the probe.
What should we make of wall vacuum test results done without
other inspection and testing?
cavity vacuum tests, depending on how and when they are performed, can be
like searching for a needle in a haystack while looking through a straw: if you
find evidence of a problem you're lucky. But if you don't find evidence, when
using a very limited-scope method, that doesn't mean that a problem is not
Our photo, left, is not showing the wall-check vacuum method that relies on vacuuming into a cassette through a hole in the wall. Instead, here we have pulled loose paneling and have inserted our spore trap cassette into the cavity.
This position combined with aggressive sampling by banging on the wall paneling with a flashlight is more likely to collect problem particles if they are present close to the point of vacuum cassette insertion into the wall. But even this approach is not a reliable characterization of mold risk in the building. And it is not looking into the wall cavity itself - rather we are looking at the two surfaces behind the paneling.
Short vacuum pump duration for microscopic examination (to avoid
sample overload, e.g. 2-=3 minutes on an Air-O-Cell) does not move enough air
to reliably find what may be in the wall
cavity. An experiment done with Louis Relle in New Orleans LA demonstrated that
wall-vac tests found less than 10% of large problem mold cavities that could
be discovered by cutting drywall openings in a building.
Our photo (left) shows a short-duration but larger surface area or wall opening vacuuming system invented and tested by the author - it did not provide useful results.
Longer vacuum pump duration samples for viable sampling (2 hours
into an MCE cassette for culturing) still may not move enough air to sample
through a cavity, particularly if the cavity is insulated. Further, two-hour
samples means that most-likely very few sample points were collected, making
the inspection scope extremely limited and thus overall confidence in the
accuracy of the picture of the building lower.
Consider that the popularly-marketed version of this wall cavity vacuuming approach
to test for hidden mold contamination in buildings relies on culture of the sample. Did you know that only about 10% of molds grow
in any culture at all? You're 90% uncertain of the accuracy of the test at the
One can't be sure that the mold that grew in the culture represents the
dominant problem mold or whether it's just a low-occurrence (in the building) spore
that liked the media (in the culture). We like cultures for further
genera/species identification of samples but we are nervous about relying on them
to tell me if the building has a problem or not.
Because mold test validity and mold test accuracy are often confused, readers should also see ACCURACY OF VARIOUS MOLD TEST METHODS.
Continue reading at VACUUM TEST INSULATION CONTAMINANTS or select a topic from the More Reading links shown below.
Or see VACUUM SAMPLING EQUIPMENT, DIY
Suggested citation for this web page
VACUUMING BUILDING CAVITIES at InspectApedia.com - online encyclopedia of building & environmental inspection, testing, diagnosis, repair, & problem prevention advice.
Green link shows where you are in this article series.
- MOLD CONTAMINATION IN BUILDINGS - home
- AIR CLEANER PURIFIER TYPES
- AIR CONDITIONING SYSTEM ODORS
- AIR POLLUTANTS, COMMON INDOOR
- AIR QUALITY on COMMERCIAL AIRCRAFT
- AIRBORNE PARTICLE ANALYSIS METHODS
- ALLERGEN TESTS for BUILDINGS
- ALLERGENS in BUILDINGS, RECOGNIZING
- ALLERGY & MOLD IAQ PRODUCTS
- BIBLIOGAPHY for ENVIRONMENTAL HEALTH, MOLD, IAQ
- BIOLOGICAL POLLUTANTS
- BOOKSTORE - ENVIRONMENTAL
- CACTUS FUNGI / MOLD
- CAR MOLD CONTAMINATION
- CARPET DUST IDENTIFICATION
- CHAIN OF CUSTODY FORM for ENVIRONMENTAL SAMPLES
- DIRECTORY of MOLD / ENVIRONMENTAL EXPERTS
- DISASTERS: BUILDING INSPECTION & REPAIR - home
- DUST SAMPLING PROCEDURE
- DUST ANALYSIS for FIBERGLASS
- EMERGENCY RESPONSE, IAQ, GAS, MOLD
- FORENSIC & IAQ FIELD IAQ EQUIPMENT SOP - home
- HOUSE DUST ANALYSIS
- HUMIDITY CONTROL & TARGETS INDOORS
- INDOOR AIR QUALITY IMPROVEMENT GUIDE - home
- ITCHY FABRICS
- MILDEW in BUILDINGS ?
- MOISTURE CONTROL in BUILDINGS
- MOLD CONTAMINATION IN BUILDINGS - home
- MOLD: A COMPLETE GUIDE - home
- MOLD / ENVIRONMENTAL EXPERT, HIRE ?
- MOLD TEST PROCEDURES
- MORGELLONS SYNDROME
- MSDS MATERIAL SAFETY DATA SHEETS
- MVOCs & MOLDY MUSTY ODORS
- ODORS GASES SMELLS, DIAGNOSIS & CURE
- OZONE MOLD / ODOR TREATMENT WARNINGS
- PARTICLE & MOLD LEVELS in DUCTWORK
- PARTICLE SIZES & IAQ
- STAIN DIAGNOSIS on BUILDING INTERIORS
- STAINS on INDOOR SURFACES, PHOTO GUIDE
- TECHNICAL & LAB PROCEDURES
- TEST KITS for DUST, MOLD, PARTICLE TESTS
- VAPOR BARRIERS & CONDENSATION
- VENTILATION in BUILDINGS
- VOCs VOLATILE ORGANIC COMPOUNDS
- WATER ENTRY in BUILDINGS
- WORLD TRADE CENTER 9-11 DUST PHOTOS
- FAQs below discusses field reports of problems & solutions for this topic
Frequently Asked Questions (FAQs)
Click to Show or Hide FAQs
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
Technical Reviewers & References
Publisher's Google+ Page by Daniel Friedman
Click to Show or Hide Citations & References
- Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. (416) 964-9415 1-800-268-7070 email@example.com. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides:
- Commercial Building Inspection Courses - protocol ASTM Standard E 2018-08 for Property Condition Assessments
- Home Inspection Education Courses including home study & live classes at eleven colleges & universities.
- Home Inspection Education Home Study Courses - ASHI@Home Training 10-course program.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
- The Home Reference Book, a reference & inspection report product for building owners & inspectors.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
- The Home Reference eBook, an electronic version for PCs, the iPad, iPhone, & Android smart phones.
Special Offer: For a 5% discount on any number of copies of the Home Reference eBook purchased as a single order. Enter inspectaehrb in the order payment page "Promo/Redemption" space.
- The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors.
Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
- The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones.
- Eric Galow, Galow Homes, Lagrangeville, NY. Mr. Galow can be reached by email: firstname.lastname@example.org or by telephone: 914-474-6613. Mr. Galow specializes in residential construction including both new homes and repairs, renovations, and additions.
- Mark Cramer Inspection Services Mark Cramer, Tampa Florida, Mr. Cramer is a past president of ASHI, the American Society of Home Inspectors and is a Florida home inspector and home inspection educator. Contact Mark Cramer at: 727-595-4211 mark@BestTampaInspector.com 11/06
- Roger Hankey is principal of Hankey and Brown home inspectors, Eden Prairie, MN. Mr. Hankey is a past chairman of the ASHI Standards Committee. Mr. Hankey has served in other ASHI professional and leadership roles. Contact Roger Hankey at: 952 829-0044 - email@example.com. Mr. Hankey is a frequent contributor to InspectAPedia.com.
- Arlene Puentes, an ASHI member and a licensed home inspector in Kingston, NY, and has served on ASHI national committees as well as HVASHI Chapter President. Ms. Puentes can be contacted at firstname.lastname@example.org
- Wikipedia provided background information about some topics discussed at this website provided this citation is also found in the same article along with a " retrieved on" date. NOTE: because Wikipedia entries are fluid and can be amended in real time, we cite the retrieval date of Wikipedia citations and we do not assert that the information found there is necessarily authoritative.
Books & Articles on Building & Environmental Inspection, Testing, Diagnosis, & Repair
- The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume. Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Or choose the The Home Reference eBook for PCs, Macs, Kindle, iPad, iPhone, or Android Smart Phones. Special Offer: For a 5% discount on any number of copies of the Home Reference eBook purchased as a single order. Enter INSPECTAEHRB in the order payment page "Promo/Redemption" space.