Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
AIR CONDITIONING & HEAT PUMP SYSTEMS
A/C - HEAT PUMP CONTROLS & SWITCHES
AIR CONDITIONER BTU CHART
AIR CONDITIONER COMPONENT PARTS
AIR CONDITIONER TYPES, ENERGY SOURCES
AIR CONDITIONER NOT WORKING
AIR FILTER EFFICIENCY
AIR FILTERS, FIBERGLASS PARTICLES
AIR FILTERS for HVAC SYSTEMS
AIR FLOW MEASUREMENT CFM
AIR HANDLER / BLOWER UNITS
ADDING A/C: RETROFIT SIZING
BLOWER FAN CONTINUOUS OPERATION
BLOWER FAN OPERATION & TESTING
BLOWER LEAKS, RUST & MOLD
COOLING COIL or EVAPORATOR COIL
DIRTY A/C BLOWERS
Leaks, Rodents In Air Handlers
Mold Growth in Air Handlers
BACKUP HEAT for HEAT PUMPS
BLOWER DOORS & AIR INFILTRATION
BLOWER FAN CONTINUOUS OPERATION
BLOWER FAN OPERATION & TESTING
BOOKSTORE - Air Conditioning "How To" Books
CAPACITORS for HARD STARTING MOTORS
CLEANING & Legionella BACTERIA
CHINESE DRYWALL HAZARDS
COMBUSTION GASES & PARTICLE HAZARDS
COMPRESSOR & CONDENSING COIL, A/C
CONDENSATE HANDLING, A/C
CONTROLS & SWITCHES, A/C - HEAT PUMP
COOL OFF HEAT Thermostat Switch
COOLING CAPACITY, RATED
COOLING COIL or EVAPORATOR COIL
DATA TAGS on AIR CONDITIONERS
DEFINITION of HEATING & COOLING TERMS
DEW POINT CALCULATION for WALLS
DEW POINT TABLE - CONDENSATION POINT GUIDE
DIAGNOSTIC GUIDES A/C / HEAT PUMP
DIAGNOSE & FIX HEATING PROBLEMS-BOILER
DIAGNOSE & FIX HEATING PROBLEMS-FURNACE
DUCT SYSTEM & DUCT DEFECTS
DUCTS - Asbestos
DUCT INSULATION, Asbestos Paper
DUCT INSULATION for SOUNDPROOFING
DUCT SYSTEM & DUCT DEFECTS
DUCT SYSTEM NOISES
DUCTS, Asbestos Transite Pipe
DUST, HVAC CONTAMINATION STUDY
DUST SAMPLING PROCEDURE
EDUCATION, HVAC SCHOOLS
ELECTRIC MOTOR DIAGNOSTIC GUIDE
ELECTRIC MOTOR OVERLOAD RESET SWITCH
ELECTRICAL POWER SWITCH FOR HEAT
EVAPORATOR COIL or COOLING COIL
EVAPORATIVE COOLING SYSTEMS
EXPANSION VALVES, REFRIGERANT
FAN, AIR HANDLER BLOWER UNIT
FAN AUTO ON Thermostat Switch
FAN CONVECTOR HEATERS - HYDRONIC COILS
FAN LIMIT SWITCH
FAN NOISES, HVAC
FURNACES WARM AIR HEATING SYSTEMS
GAS EXPOSURE EFFECTS, TOXIC
GAS DETECTION INSTRUMENTS
GAUGE, REFRIGERATION PRESSURE TEST
HEAT LOSS (or GAIN) in buildings
HEAT LOSS (or GAIN) INDICATORS
HEAT LOSS R U & K VALUE CALCULATION
HEATING SMALL LOADS
HOUSEWRAP AIR & VAPOR BARRIERS
HUMIDITY LEVEL TARGET
INDOOR AIR QUALITY IMPROVEMENT GUIDE
INSPECTION CHECKLIST - OUTDOOR UNIT
INSPECTION LIMITATIONS, A/C SYSTEMS
LEED GREEN BUILDING CERTIFICATION
LIGHT, GUIDE to FORENSIC USE
LOST COOLING CAPACITY
LOW VOLTAGE TRANSFORMER TEST
MANUALS & PARTS GUIDES - HVAC
MOTOR OVERLOAD RESET SWITCH
MOLD in AIR HANDLERS & DUCT WORK
MOLD INFORMATION CENTER
NOISE AIR CONDITIONER / HEAT PUMP
NOISE / SOUND DIAGNOSIS & CURE
ODORS in AIR HANDLERS & DUCT WORK
OPERATING COST, AIR CONDITIONER
OPERATING DEFECTS, AIR CONDITIONING
OPERATING TEMPERATURES, AIR CONDITIONER
PORTABLE ROOM AIR CONDITIONERS
PRESSURE READINGS, REFRIGERANT
REPAIR GUIDES A/C / HEAT PUMP
REPAIR & DIAGNOSTIC FAQs for A/C
REFRIGERANTS & PIPING
RETROFIT SIZING for A/C or HEAT PUMPS
SEER RATINGS & OTHER DEFINITIONS
SPLIT SYSTEM AIR CONDITIONERS & HEAT PUMPS
THERMOSTATS, HEATING / COOLING
THERMOSTATIC EXPANSION VALVES
WATER COOLED AIR CONDITIONERS
WINDOW / WALL AIR CONDITIONERS
WINDOW / WALL A/C SUPPORTS
Tests for mold in HVAC air ducts: this article explains how to assess the level of mold contamination in heating or cooling air ducts, and the aggressiveness of mold testing (do we agitate the ducts) that can form sources of error when testing HVAC systems for mold contamination.
This document is a brief tutorial which provides information about the accuracy of and sources of errors in tests for the level of allergenic and toxic mold in residential buildings:Are spore counts valid? Are cultures and swab tests valid?
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Question: After dealing with a moldy washing machine and even a mold remediation we are focusing on our ductwork: what is the best way to test for mold in the heating/AC system
Thanks for your website - it is truly a public service. My husband and I are both very ill - my husband has recently been diagnosed with metastasizing melanoma in his eye, which has spread to his liver and spine - his prognosis is not good.
[Click to enlarge any image]
I have been sick with sinusitis for over a year now and am known to have severe allergies to mold (causing recurrent bronchitis and sinusitis). After many scans and tests, my doctors feel the most likely reason not responding to treatment (many courses of antibiotics and sinus irrigations) is because of an environmental allergy.
Because of my known allergy, and because of a small area of what looked like black mold (and smelled unbelievably vile) discovered during the renovation, we had two different mold remediation companies as well as an air quality testing company come in.
They felt the black mold was removed completely (under negative pressure and other precautions) and then they did a fair amount of preventive work - since there were a few tiny areas of green mold in the basement and attic. Air quality testing afterwards supposedly showed no mold anywhere.
We recently discovered our front-loading washing machine is one of the brands known to have major mold problems and there are now several class action suits against them. We had several puzzling episodes of moldy sheets, which weren't recognized until our son came home to visit (my sense of smell has been wiped out by the sinusitis and my husband never had a good sense of smell).
We couldn't figure out how this was happening since we are very careful not to leave wet clothes/linens lying around or in the washer. According to our son, the mold smell permeated the master bedroom. We then moved to the other bedroom and the same thing happened again, discovered when our son was visiting again, and again the smell permeated the room. The washer is in the master bath.
I first got sick in our old house (which was a house that, up until then, had been a very healthy environment for me) after we bought the washing machine. We had a couple of episodes of moldy-smells in our wash in the old house, but I was still able to smell and threw things out right away, but was puzzled as to why they were occurring.
We have replaced the washer, aired out the rooms, bought air filters, have an HEPA filter on the return heating duct, but I am not feeling better (after having rewashed all our clothes and bedding.
We're concerned that mold could be in the heating/AC duct system.
We've thrown out all our linens twice now (after our son discovered the mold) but before we learned about the washer. We're also wondering if we need to throw out everything again.
My basic question is what is the best way to test for mold in the heating/AC system and is there a company/person you could recommend to do this work?
Thanks for your time and any advice you can give us. - K.J., New Jersey
Reply: A combination of Steps can Help Assess Mold Contamination in an HVAC System
We have sometimes found that thick absorbent furnishings such as carpets, upholstered couches and chairs, and mattresses that suffer prolonged exposure to a moldy environment may be smelly from MVOCs even if there was no observable actual mold spore or mold growth contamination on those items.
I'd like to know more about the clothes washer you had trouble with and what authoritative references you have on that matter.
At MOLD & ENVIRONMENTAL INSPECTORS we list some inspectors/testers specializing in mold and indoor contaminants. But there may be other well qualified people in your area. Talk with anyone you are considering hiring. Don't tell them the "right answer" (besides they are likely to have other good ideas). But name your concerns and ask how they will approach the job - stay away from superficial experts who dash in, collect a mold sample, charge you, and leave. [InspectAPedia.com has no financial nor business relationship with products or services discussed at our website
How much variation in airborne mold or dust level do we see inside heating and air conditioning ducts and air handlers?: The left hand photograph shows a one liter airborne particle trace collected inside of a heating furnace return air plenum using a Burkard Personal Air Sampler.
The right hand photograph shows a second particle trace collected in the same location, with the same volume of air, with one difference: we tapped lightly on the side of the air plenum during the sampling process.
Even before counting the number airborne particles of any type per liter of air it is obvious that even modestly aggressive sampling (rapping on the plenum to stir up local dust) can make a large difference in the level of particles seen in the sample result.
We conducted this test during a post mold remediation clearance inspection of a previously mold-contaminated air conditioning system. The remediation contractor vehemently disagreed with the procedure of tapping on the ductwork during testing, informing us that "... his hygienist never did such a thing".
We agree that consistency in test methods is important in order to be able to compare one mold test with another. However if we're looking for the presence or absence of a significant mold or allergenic dust reservoir that should have been removed, a little aggressiveness in sampling can be useful and in fact more accurate as well.
In sum, do not rely on the accuracy of airborne particle counts alone: Since air samples do not capture a representative picture of the indoor environment an indoor air quality investigator should not rely simply on conventional airborne particle quantitative analysis (particle counts per cubic meter).
Readers concerned with mold contamination in heating and air conditioning air handlers and ductwork should see BLOWER LEAKS, RUST & MOLD and PARTICLE & MOLD LEVELS in DUCTWORK where we describe how to test HVAC systems and ductwork for mold.
Mold in HVAC ductwork is also discussed at WHY DOES MOLD GROW in INSULATION?. See SLAB DUCTWORK for the role of in-slab placement of air ducts in the formation of mold contamination in HVAC systems. These critical mold testing accuracy questions are discussed in this paper.
Readers should also see MOLD LEVEL IN AIR, VALIDITY, and for a more in-depth critique of popular mold testing methods than this tutorial see MOLD TESTING METHOD VALIDITY or select a topic from the More Reading links shown below.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
Question: how can I arrange a test to identify the mold in the flex duct on my HVAC system?
Recently, I discovered mold in the air ducts of my house.
I am hoping you can tell me how to get it tested as I am very concerned.
I will forward pictures as well.
Thanks in advance for your time and help. - A.B. 11/16/2012
Reply: focus on removing the mold (replace the flex duct) and fixing the cause of its growth
A competent onsite inspection by an expert usually finds additional clues that help accurately diagnose a problem - in this case, why the flex duct in your photos is moldy, how much moldy material is present, and thus not just how to correct the problem but how to prevent its recurrence. That said, here are some things to consider:
Testing your HVAC duct mold is easy following the procedure we describe using clear adhesive tape - see MOLD TEST KITS for DIY MOLD TESTS and use any qualified mold test lab or look into the list of labs and experts we provider at InspectApedia.
BUT I'm not sure I would bother in this case. There are sometimes reasons to test mold or dust samples, (see MOLD TEST REASONS ) but in this case you'd be best off spending your money on replacing the moldy ductwork and fixing the cause of its growth in the first place.
Replace the moldy flex duct, inspect the whole system for cleanliness, clean components that can be cleaned (air handler blowers, metal ductwork interiors), and fix the cause of mold growth.
See MOLD EXPERT, WHEN TO HIRE for help in deciding if it's appropriate to bring in an expert.
Question: can you determine by viewing photos of a dark substance on the [outside] of an air handlers' ductwork that there is mold contamination? Can I assume the mold is also inside the ductwork?
Would you be able to determine by viewing the photo DSC 0199 if the dark black substance which appears in two areas of the air handler’s adjoining ductwork is a mold which has formed from condensation? If this is a mold can it be assumed to exist inside the duct where air flow would be exposed to the mold? All of the filters were found to have excessive dust and dirt build up which would lend itself to introducing particles into the ductwork which could harbor mold spores. - J.B. 12/31/2013
A competent onsite inspection by an expert usually finds additional clues that would permit a more accurate, complete, and authoritative answer than we can give by email alone, and for the case you describe I'm certain that an onsite expert would be more useful. You will find additional depth and detail in articles on ductwork mold contamination and leaks into ductwork at our website. That said I offer these comments:
I see in your photos what looks like leaks into and out of a section of ductwork - a condition that indeed invites mold growth. I also see thick debris in the other photos - but from just the photos, no honest competent investigator could conclude the extent of mold contamination nor hazard.
The minimum steps that make sense to me are to investigate further to
- find and fix the cause of leaks into the ductwork or air handler or both
- look in the areas of leakage for visible mold growth
- change the filters regularly
- if filters clog quickly, look for an unusually high level source of airborne particulate debris
No you cannot assume that because you see mold on the outside of an air handler, plenum, or HVAC duct that mold is growing inside the ductwork, nor could you assume, even if mold were inside the ducts that it is the same genera/species, as the interior materials and debris that might support mold growth may be different and thus may tend to grow different molds.
More to the point, in tracing mold contaminatin in buildings one needs to follow the water. If the leak that made stains on the outside of HVAC equipment and ducts also sent water inside the same system then yes, one might want to look at the extent of cleaning needed inside the duct system. But if the leak did not send water inside of the ducts then it would be unfounded to assume that the same mold contamination was present therein.
Reader follow-up: if it's dark it's mold, right?
I do realize it takes a hands on approach and not just a view of a photo taken to establish any extent of mold intrusion. I assume from your response below we cannot even say with any certainty that the dark substance is mold? It could be just a discoloration that occurred after the fact from years of operation, however, I cannot imagine what else would cause the discoloration other than mold.
The dark gray stuff I could make out in the photos could be just house dust.
Keep in mind that of the approximately 1.5 million mold genera/species, only a small subset are "dark" or black, and of those, a smaller still subset are particularly likely to grow in or on building materials, and a smaller subset of those that are particularly harmful. I agree that a dark discoloration, when viewed closely, may contain or even be mold, but dirt, house dust, and other debris are also dark.
Generally for detecting mold growth on a surface one first looks closely at the suspect area for the characteristic mold growth patterns - enabling one to assert that mold is present even without knowing its genera and species. Often this is enough, since the cleanup procedure does not depend on the mold genera/species.
However in some cases, particularly where mold-related illness is involved, the physician may want to know what molds are in the patient's environment. And in other cases where large, costly mold remediation projects are required, knowing what mold genera/species were being removed combined with pre-testing of various building areas outside the remediation area can head off problems with poor cleaning or inadequate work area dust containment that may arise later.
Reader follow-up: my concern is if the mold I see is entering the HVAC air flow
Yes, i agree, the filter debris appears to be only dust buildup but after Auto correcting the air handler photo it improves clarity and if you zoom in close it appears to be mold for sure. My concern next is to determine if it is inside the ductwork and allowing the spores to communicate with the air flow.
Reply: agreed - take a look inside the ductwork for evidence of water leakage and mold growth
Agreed; I may not have emphasized it adequately before but to me the red flag was what looked like water leak stains running down the exterior surface of the duct, suggesting the chances of leaks into the duct system as well. If you find mold there and if the duct interior is an insulating mat rather than simple sheet metal, it may be cheapest to simply remove and replace that duct section.
Reader follow-up: I found a website that says ductwork is the most likely place to find building mold
I found another site which appears to mirror the same issue i am having. I would venture to say that the inside of the duct itself has to have some deposits as well. The website states "This is the #1 place that mold is found in your home, outside of roof leaks. This condition is caused by air handler unit that was not maintained properly."
Reply: the quotation is mistaken
The website you quote is interesting but not without conflict of interest and not fully nor accurately informed. While some of the photos are almost certainly show some mold contamination, one cannot always nor necessarily easily distinguish between debris deposits on a fiberglass duct liner and mold contamination. Further, some of these molds are very common (Cladosporium cladosporoioides), sticky, not easily airborne, not found at notable levels in an in-duct air sample, and at worst allergenic, and in small areas not actionable. Other molds less likely to be found but that can appear can be more of a concern (Aspergillus sp./niger for example) as they are easily airborne, small, toxic or pathogenic, inhaled deeply into the lung, may be light colored and difficult to see.
Reader follow-up: I still think the air handler ductwork is the most prone are for mold incubation
Your website is the most informative of any I've found to date. I do think though that he is claim about Air handler ductwork just like mine is the most prone area for mold incubation. I havent found any other ductwork at least from the outside appearance that has the same black color.
Reply: Drywall and wood and perhaps carpeting are the most mold-friendly and largest surfaces areas in buildings likely to product a wide range of mold contamination reservoirs of a wider range of mold genera/species
Regarding your observation that ". I do think though that he is claim about Air handler ductwork just like mine is the most prone area for mold incubation."
That statement is mistaken and cannot be based on building science, mycology, nor broad field observation of buildings. From education in those fields, from literature review of studies of building mold occurrence, and from direct experience in evaluating close to 5000 buildings over more than 30 years, including directy studies of every material and surface in mold-contaminated buildings to map the preference of various building molds for specific building materials and surfaces, it is readily apparent that the claim that ductwork is the most mold-prone "incubation" area in buildings is considerably off the mark.
Enjoying the freedom of un-edited website publication, that statement is an opinion, and it is wrong, and remains unsupported by authoritative citation nor research.
Even the word "incubation" suggests a lack of knowledge of mycology.
The largest mold reservoirs in buildings that have suffered water damage, leaks, or on occasion just high humidity are found on the most mold-friendly materials, particularly the paper surfaces of drywall, and secondarily on exposed wood surfaces such as framing and sheathing.
Unlike ductwork, those surfaces harbor most of the 200 common mold species (MOLD FREQUENCY in buildings ) as well as occasional occurrences of less common molds and include the more harmful mold genera species regularly found in buildings such as Aspergillus sp., Penicillium sp., Stachybotrys chartarum, Memnoniella echinata, and yeasts.
We do not find those genera / species growing in ductwork in large reservoirs if at all, though we do find them in contaminated dust entering the duct system from an infected building.
The surfaces of HVAC ductwork in buildings are typically of three materials: plastic, metal, or a coated dense fiberglass mat. While we can find mold genera/species that will grow on just about any material, none of those three comes even close to the mold-conducive friendly environment provided by drywall, wood, wallpaper, even carpeting.
Of the approximately 200 mold genera/species most frequently found in buildings, only a very few of them, particularly in the Cladosporium group, are commonly found in HVAC duct systems. I explained the comparative risk levels using two common Cladosporium findings vs. Aspergillus sp. (not commonly found in ductwork) at a gross level in my earlier comments. In short, the most harmful and most easily airborne molds are not commonly found growing inside HVAC ducts. When such molds are found inside HVAC duct systems, in general they have arrived there in air circulated into the duct system from a larger, more dangerous building mold reservoir.
Having disposed of the "bad mold is mostly in ductwork" mistake by pointing out what does and does not grow in ducts, one has but to observe further that the level of mold hazard in a building depends on both the mold genera/species that are found therein, and on the size of the mold reservoir itself.
In a simple comparison of the total indoor building area represented by drywall and wood in most buildings (in North America, Europe, Australia, New Zealand and the U.K. and parts of Asia) with the total area that might be represented by the interior surfaces of HVAC ductwork in that subset of buildings that even have ductwork present makes clear that the potential contribution to building mold contamination by ducts is small compared to the potential contribution to building mold from the significantly larger mold reservoirs of of other materials and the larger range of genera and species of mold that they support.
This is not to say that there is never mold contamination in HVAC systems. It is to emphasize that across a population of mold-contaminated buildings where professional mold cleanup is justified and appropriate, by no means is the ductwork mold reservoir the largest, by no means is it the most conducive to mold growth, and by no means are the mold genera species found growing therein the most harmful.
Questions & answers or comments about how to measure the level of mold contamination in HVAC air ducts and blower units.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Mold Contamination Testing, Cleanup, Prevention: references & products
OTHER IAQ ISSUES: How To Find and Address Other Indoor Air or Indoor Environment Contaminants Besides Mold
Mold or allergens may not be the only or even the main indoor environmental contaminant. Don't let media attention to mold cause so much enviro-scare fear that other, possibly more urgent hazards go un-addressed.