Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SEPTIC CARE INSTRUCTIONS
SEPTIC D-BOX INSTALL REPAIR
SEPTIC DRAINFIELD FAILURE DIAGNOSIS
SEPTIC DYE TEST PROCEDURE
SEPTIC FAILURE SIGNS
SEPTIC INSPECTION & TEST GUIDE
SEPTIC LIFE EXPECTANCY
SEPTIC SUPPLIES & PARTS
SEPTIC SYSTEM DESIGN ALTERNATIVES
SEPTIC SYSTEM DESIGN BASICS
SEPTIC SYSTEMS, HOME BUYERS GUIDE to
SEPTIC SYSTEM SAFETY WARNINGS
SEPTIC TREATMENTS & CHEMICALS
SEWAGE BACKUP PREVENTION
SEWAGE EJECTOR / GRINDER PUMPS
SEWER GAS ODORS
SEWER LINE REPLACEMENT
SINKHOLES, WARNING SIGNS
SOAKAWAY BED FAILURE DIAGNOSIS
SULPHUR & SEWER GAS SMELL SOURCES
TOILETS, INSPECT, INSTALL, REPAIR
TRAPS on PLUMBING FIXTURES
TREATMENTS & CHEMICALS, SEPTIC
VIDEO GUIDES: Septic Videos
WATER CONSERVATION MEASURES
WATER SOFTENERS & CONDITIONERS
WATER SUPPLY & DRAIN PIPING
WATER, WELLS, WATER TANKS: TESTING GUIDE
WASHING MACHINES & SEPTIC SYSTEMS
WASTEWATER TREATMENT BASICS
WINTERIZE A BUILDING
This article discusses soil percolation rate specifications - what are the required soil perc rates when testing for septic system absorption system or drainfield design or repair.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
PERC TEST STANDARDS - What are the soil percolation rate standards and other soil requirements for septic systems?
The Massachusetts Title 5 Septic Inspection criteria does a great job of defining a (at least possibly) what is required to assure a functional septic drainfield. The text explains the role of the biomass below the absorption bed, sets soil depth requirements, and recognizes the importance of keeping the bottom of the working biomass area in well drained soil sufficiently above the seasonal high water table.
Here is an example of soil requirements for a functional drainfield. This version is particularly clearly written and is for residents of Ohio but the principles apply anywhere. Readers should also see our example of state-regulated soil percolation tests at the New York State Septic System Design Regulations 75-A.4 - Soil and site evaluation for septic system design page.
In Ohio, soil absorption systems can be used in areas where the percolation rate of the soil is between 3 and 60 minutes per inch (soil permeability between 1 and 20 inches per hour).
At least 4 feet of suitable soil is required under the soil absorption system to provide adequate treatment of the septic tank effluent. To accommodate the construction of the system and provide adequate soil cover to grade, a minimum of 5 1/2 to 6 1/2 feet of suitable soil is needed above the limiting layer.
A limiting layer may be bedrock, an impervious soil layer (hardpan, fragipan) or a seasonally high water table (gray soil or mottles). The soil absorption system must be at least 8 feet from any drain line on the lot, 50 feet from a water supply, and 10 feet from the property line, right-of-ways and the house. Septic systems cannot be placed on the flood plain and are limited to areas with less than a 15 percent slope. Reference: ohioline.osu.edu/aex-fact/0743.html Ohio State University Fact Sheet Septic Tank - Soil Absorption Systems
Our separate article by Lockwood includes a description of the calculations to answer the question: How Big Should the Leach Field Be? and includes a practical example using sample calculations as well as a table of soil percolation rate vs. the necessary leach field size.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References