Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SEPTIC CARE INSTRUCTIONS
SEPTIC D-BOX INSTALL REPAIR
SEPTIC DRAINFIELD FAILURE DIAGNOSIS
SEPTIC DYE TEST PROCEDURE
SEPTIC FAILURE SIGNS
SEPTIC INSPECTION & TEST GUIDE
SEPTIC LIFE EXPECTANCY
SEPTIC SUPPLIES & PARTS
SEPTIC SYSTEM DESIGN ALTERNATIVES
SEPTIC SYSTEM DESIGN BASICS
SEPTIC SYSTEMS, HOME BUYERS GUIDE to
SEPTIC SYSTEM SAFETY WARNINGS
SEPTIC TREATMENTS & CHEMICALS
SEWAGE BACKUP PREVENTION
SEWAGE EJECTOR / GRINDER PUMPS
SEWER GAS ODORS
SEWER LINE REPLACEMENT
SINKHOLES, WARNING SIGNS
SOAKAWAY BED FAILURE DIAGNOSIS
SULPHUR & SEWER GAS SMELL SOURCES
TOILETS, INSPECT, INSTALL, REPAIR
TRAPS on PLUMBING FIXTURES
TREATMENTS & CHEMICALS, SEPTIC
VIDEO GUIDES: Septic Videos
WATER CONSERVATION MEASURES
WATER SOFTENERS & CONDITIONERS
WATER SUPPLY & DRAIN PIPING
WATER, WELLS, WATER TANKS: TESTING GUIDE
WASHING MACHINES & SEPTIC SYSTEMS
WASTEWATER TREATMENT BASICS
WINTERIZE A BUILDING
Use sand around buried pipes: This article describes the use of sand around a sewer pipe during backfill when a sewer pipe or "drain line" is replaced.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Use of sand to bed the new drain piping: why & how - specifications for bedding sewer piping in sand in trenches
What is the Proper Material for Bedding Buried Sewer or Water Pipes?
Sewer lines in sand, possibly in pea gravel: Our contractor for the sewer line replacement project documented in this article used clean sand for bedding the new sewer piping. Sand was specified by our local building department. Some local codes permit and some contractors like to use pea gravel for plastic sewer line protection, asserting that pea gravel settles less than sand in the pipe trench.
However water supply piping must be bedded in clean sand. Where copper water supply pipes have been buried in gravel contractors find that over time the gravel, perhaps moving by frost or water passage through the soil, actually works against the metal water piping to create multiple holes and leaks in the water main.
One of our consultants, George from Jeneral Sewer Service reported that on excavating a water supply line with poor water pressure, he found that the entire length of the copper water pipe had multiple perforations - "When we dug it up and turned on water pressure at the curb box the water line looked like a sprinkler hose!" he said.
Where plastic water supply piping is used the risk of gravel perforation from the backfill material is little or none unless the excavator permits a large or sharp stone to become buried close to the piping. .
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Check the FAQs just above, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.