Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SEPTIC CARE INSTRUCTIONS
SEPTIC D-BOX INSPECTION
SEPTIC DRAINFIELD FAILURE DIAGNOSIS
SEPTIC DYE TEST PROCEDURE
SEPTIC FAILURE SIGNS
SEPTIC INSPECTION & TEST GUIDE
SEPTIC LIFE EXPECTANCY
SEPTIC SUPPLIES & PARTS
SEPTIC SYSTEM DESIGN ALTERNATIVES
SEPTIC SYSTEM DESIGN BASICS
SEPTIC SYSTEMS, HOME BUYERS GUIDE to
SEPTIC SYSTEM SAFETY WARNINGS
SEPTIC TREATMENTS & CHEMICALS
SEWAGE BACKUP PREVENTION
SEWAGE EJECTOR / GRINDER PUMPS
SEWER GAS ODORS
SEWER LINE REPLACEMENT
SINKHOLES, WARNING SIGNS
SOAKAWAY BED FAILURE DIAGNOSIS
SULPHUR & SEWER GAS SMELL SOURCES
TOILETS, INSPECT, INSTALL, REPAIR
TRAPS on PLUMBING FIXTURES
TREATMENTS & CHEMICALS, SEPTIC
VIDEO GUIDES: Septic Videos
WASHING MACHINES & SEPTIC SYSTEMS
WATER SOFTENERS & CONDITIONERS
WATER SUPPLY & DRAIN PIPING
WASTEWATER TREATMENT BASICS
WATER, WELLS, WATER TANKS: TESTING GUIDE
WINTERIZE A BUILDING
This article describes we determined that a sewer pipe or "drain line" had to be replaced. The line which was replaced in this sewer drain line article runs from the building exterior to a septic tank located downhill from the home. Sketch courtesy of Carson Dunlop Associates (above) shows common defects found in clay sewer piping: tree root invasion, silt infiltration where pipe hugs open due to settlement and pipe shifting, or broken, collapsed pipe sections. Our clay sewer pipe article (below) diagnosed a broken sewer line that was crushed from above. The pipe was shallow, not protected from damage, and was broken when a heavy lawn mower drove over the line.
We present an actual sewer line replacement case study, illustrated with photos of each step in the diagnosis and replacement of a blocked sewer line. Technical reviewers are welcome and are listed at "References." This is a chapter of Inspecting, Testing, & Maintaining Residential Septic Systems an online book on septic systems. Also see Backups and Clogged Drains diagnosing septic backups and septic system failures versus clogged drains.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved.
Using a wrecking bar and shovel we flipped over the section of sidewalk to expose, no surprise, a wet area below the sidewalk, showing that not only was our sewer line blocked, worse, it was broken. This was not a big surprise.
We were working on a 1920's home which still, as far as we knew, had its original clay piping between house and septic tank. The second photo is a close up showing the sewage leak where the drain line was not only blocked, but broken below the sidewalk.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the search box below to ask a question or to search the InspectApedia.com website.
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.
Onsite Wastewater Disposal Books