Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SEPTIC CARE INSTRUCTIONS
SEPTIC D-BOX INSTALL REPAIR
SEPTIC DRAINFIELD FAILURE DIAGNOSIS
SEPTIC DYE TEST PROCEDURE
SEPTIC FAILURE SIGNS
SEPTIC INSPECTION & TEST GUIDE
SEPTIC LIFE EXPECTANCY
SEPTIC SUPPLIES & PARTS
SEPTIC SYSTEM DESIGN ALTERNATIVES
SEPTIC SYSTEM DESIGN BASICS
SEPTIC SYSTEMS, HOME BUYERS GUIDE to
SEPTIC SYSTEM SAFETY WARNINGS
SEPTIC TREATMENTS & CHEMICALS
SEWAGE BACKUP PREVENTION
SEWAGE EJECTOR / GRINDER PUMPS
SEWER GAS ODORS
SEWER LINE REPLACEMENT
SINKHOLES, WARNING SIGNS
SOAKAWAY BED FAILURE DIAGNOSIS
SULPHUR & SEWER GAS SMELL SOURCES
TOILETS, INSPECT, INSTALL, REPAIR
TRAPS on PLUMBING FIXTURES
TREATMENTS & CHEMICALS, SEPTIC
VIDEO GUIDES: Septic Videos
WATER CONSERVATION MEASURES
WATER SOFTENERS & CONDITIONERS
WATER SUPPLY & DRAIN PIPING
WATER, WELLS, WATER TANKS: TESTING GUIDE
WASHING MACHINES & SEPTIC SYSTEMS
WASTEWATER TREATMENT BASICS
WINTERIZE A BUILDING
Septic tank or field clearance distances to swim pools: this document, which discusses distances that should be observed between a swimming pool installation and septic fields or septic tanks is a supplement to our chapter SEPTIC CLEARANCES which provides typical septic tank and field clearances. In this file a detailed septic distances table describes distance requirements between septic components (septic tank, leach field, cesspools, drywells) and other site features such as wells, water supply piping, streams, trees, property boundaries, lakes, etc.
Also see Well Clearances for required distances between wells and septic systems and other site features. In general, septic effluent must be disposed of on the property from which it originates. However more strict clearances and distances than this are required between various onsite wastewater treatment system components and buildings, property boundaries, lakes, streams, wells, and so on, as detailed in the table below. Contact us with corrections or additions to this data.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Few septic authorities or codes specifically address the distance that should be maintained between a swimming pool and septic system components like septic tanks, drainfields, or septic mound systems. But we have observed some serious problems when swimming pools were installed near or on top of septic system components.
Problems caused by a swimming pool on top of or too close to a septic field include damage to the drainfield, reduced ability of the drainfield to absorb effluent, redirecting water onto and thus flooding the drainfield, and even causing drainfield effluent to leak out to the ground surface around the swimming pool. This article discusses some of things you should consider when installing a swimming pool near a septic system.
Other than a fifteen foot clearance specified between a swimming pool and septic components for the state of Missouri, and a 100 ft. clearance specified between a swimming pool and a septic lagoon (an entirely different situation), we don't have much guidance in locating swimming pools near septic components. I don-t know an official answer to this question, but here are some considerations when planning to add a swimming pool to a property with a septic system:
After also addressing the above considerations, locate a pool 25- or more from the nearest portion of the mound. That should give good working distance for installation and if surface drainage corrections are needed between pool and mound there should be ample room to install such.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Design Manuals for Septic Systems