Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SEPTIC CARE INSTRUCTIONS
SEPTIC D-BOX INSTALL REPAIR
SEPTIC DRAINFIELD FAILURE DIAGNOSIS
SEPTIC DYE TEST PROCEDURE
SEPTIC FAILURE SIGNS
SEPTIC INSPECTION & TEST GUIDE
SEPTIC LIFE EXPECTANCY
SEPTIC SUPPLIES & PARTS
SEPTIC SYSTEM DESIGN ALTERNATIVES
SEPTIC SYSTEM DESIGN BASICS
SEPTIC SYSTEMS, HOME BUYERS GUIDE to
SEPTIC SYSTEM SAFETY WARNINGS
SEPTIC TREATMENTS & CHEMICALS
SEWAGE BACKUP PREVENTION
SEWAGE EJECTOR / GRINDER PUMPS
SEWER GAS ODORS
SEWER LINE REPLACEMENT
SINKHOLES, WARNING SIGNS
SOAKAWAY BED FAILURE DIAGNOSIS
SULPHUR & SEWER GAS SMELL SOURCES
TOILETS, INSPECT, INSTALL, REPAIR
TRAPS on PLUMBING FIXTURES
TREATMENTS & CHEMICALS, SEPTIC
VIDEO GUIDES: Septic Videos
WATER CONSERVATION MEASURES
WATER SOFTENERS & CONDITIONERS
WATER SUPPLY & DRAIN PIPING
WATER, WELLS, WATER TANKS: TESTING GUIDE
WASHING MACHINES & SEPTIC SYSTEMS
WASTEWATER TREATMENT BASICS
WINTERIZE A BUILDING
Septic test report: this article provides details of how to report the results of a Septic Loading and Dye Test. If waste water leaks to the ground surface (an unsanitary condition indicating serious septic failure) one may find dye in that water provided the septic system is flowing at common rates.
But even without that result, the septic inspection and its report will contain critical findings and information for the property owner or for a prospective buyer.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
HOW TO REPORT SEPTIC TEST RESULTS - & Test Conditions - What is the Minimum That A a Septic Test Report Include
A septic loading and dye test does not guarantee detection of all failing conditions. However it can make a meaningful reduction in the risk of an imminent costly septic failure, if the test is performed and documented properly. For a test to be meaningful, it is critical that reasonable test procedures be followed, such as described above, and that the procedures are documented.
A professional inspector is expected to provide sufficient documentation of the procedure followed and results obtained that an experienced third party could review that information and agree that the test provided was acceptable, regardless of the outcome. Finally, proper documentation at the site and during the test makes writing the septic report much easier.
The meaning and reliability of any test procedure is obscure unless the consultant records the test parameters and conditions. For example, a "dye test" was performed by an inspector who placed a single dye tablet into a washing machine drain line, followed by running 50 gallons of water at an upstairs plumbing fixture.
The lack of aggressiveness of the test, inadequate dye amount, minimal volume of water run, and failure to confirm that the fixture operated actually placed water into the septic tank all would have been more obvious to both the inspector and the client had this date been reported. Instead, the inspector wrote that he had "performed a septic dye test" and that there was "no evidence of a problem."
In an often-occurring anecdote, the morning after the new building owner moved into the home, sewage effluent had flooded the yard behind the home. When the septic contractor opened the tank it was evident that the tank was totally packed with solids. Litigation followed. This sounds like an extreme example, but it's all too common.
Septic Inspection & Test Report Contents
Authorities from various U.S. states all suggest that a septic inspection report should answer the following basic questions about the septic system:
We recommend that for clarity, responsibility, and usefulness, anyone inspecting a septic system for a home buyer or home owner should add to these basic septic inspection report findings the information we list below. These details not only make the septic inspection report more valuable to to the client, they reduce the chances for a future and costly surprise for any of the parties involved.
Essential documentation of septic loading and dye test procedure and conditions includes at least the following
Septic System Inspection Data Recording Worksheets & Checklists
An example field data recording sheet that documents details about the septic system and includes a section on Dye Test Procedure Used (fixtures operated, total volume run, confirmation of flow into septic) and pre and post-test Observations such as and evidence of dye breakout is provided at Level 0 - Basic Septic Inspection Worksheet
These pages are part of our SEPTIC DYE TEST PROCEDURE for testing septic system function. Technical review by industry experts has been performed and is ongoing - reviewers are listed at References. Comments and suggestions for content are welcome.
Continue reading at SEPTIC DYE TEST WARNINGS or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References