Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SEPTIC CARE INSTRUCTIONS
SEPTIC D-BOX INSTALL REPAIR
SEPTIC DRAINFIELD FAILURE DIAGNOSIS
SEPTIC DYE TEST PROCEDURE
SEPTIC FAILURE SIGNS
SEPTIC INSPECTION & TEST GUIDE
SEPTIC LIFE EXPECTANCY
SEPTIC SUPPLIES & PARTS
SEPTIC SYSTEM DESIGN ALTERNATIVES
SEPTIC SYSTEM DESIGN BASICS
SEPTIC SYSTEMS, HOME BUYERS GUIDE to
SEPTIC SYSTEM SAFETY WARNINGS
SEPTIC TREATMENTS & CHEMICALS
SEWAGE BACKUP PREVENTION
SEWAGE EJECTOR / GRINDER PUMPS
SEWER GAS ODORS
SEWER LINE REPLACEMENT
SINKHOLES, WARNING SIGNS
SOAKAWAY BED FAILURE DIAGNOSIS
SULPHUR & SEWER GAS SMELL SOURCES
TOILETS, INSPECT, INSTALL, REPAIR
TRAPS on PLUMBING FIXTURES
TREATMENTS & CHEMICALS, SEPTIC
VIDEO GUIDES: Septic Videos
WATER CONSERVATION MEASURES
WATER SOFTENERS & CONDITIONERS
WATER SUPPLY & DRAIN PIPING
WATER, WELLS, WATER TANKS: TESTING GUIDE
WASHING MACHINES & SEPTIC SYSTEMS
WASTEWATER TREATMENT BASICS
WINTERIZE A BUILDING
Septic dye testing guide: this article provides the detailed procedure explaining just how to inspect and test a septic system. We give details of the Septic Loading and Dye Test procedure for testing the function of septic systems, focused on condition of the effluent disposal section, also known as a leach field, seepage pits, drainfield or drainage field.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Septic System Loading and Dye Tests often requested by certain lenders, involve flushing a special dye down a toilet or other drain combined with a known quantity of water sufficient to put a working load on the absorption system.
If waste water leaks to the ground surface (an unsanitary condition indicating serious septic failure) one may find dye in that water provided the septic system is flowing at common rates.
Dyed effluent usually appears in 20-30 minutes on a failed system but can take up to five days to show up. If at a building inspection suspect wet areas are observed I recommend a dye test even if one was not previously requested. When wet areas are not found (or created by running water into the septic system) on the property being inspected, dye tests may still be performed to meet requirements of some lenders.
Although this test can often find a costly failure it does not find all possible problems. So by itself a dye test is not indicative of complete condition of the system. On the other hand, I've found so many failed systems with this procedure that it's well worth performing.
Watch out: Anyone inspecting septic systems MUST be familiar with the hazards and safety concerns discussed at SEPTIC SYSTEM SAFETY WARNINGS
Septic dye tests involve flushing a special florescent dye down a toilet or other drain. The dye itself does not make anything happen. It is simply a colored indicator that can identify water found outside as having come from the fixture where the dye was introduced.
It's the volume of water introduced into the system that forms the actual "test". If waste water is coming to the surface (an unsanitary condition indicating serious septic failure) one may see dye in that water, provided the septic system is flowing at common rates.
When suspect wet areas are observed, if the system has no maintenance history, if the area is known to have problem soils, or if other historic or site conditions raise question about the condition of the system we recommend that the inspector perform a dye test.
A septic loading and dye test will by no means find every septic failure, but this methods finds many failures that otherwise are unnoticed by a home buyer until shortly after moving-in. Septic loading and dye tests are complimentary to and should precede any further inspection steps taken such as pumping the septic tank.
After a loading and dye test (which primarily tests the absorption system, leach field, or drain field), unless the septic tank has been pumped very recently, we recommend that this additional step be taken.
Before completing the purchase of a property with a septic tank and absorption system, limited but important additional information regarding the condition of the system tank and also the leach field may be obtained by having a septic contractor open, clean, and inspect the septic tank itself.
Particularly in the case of older systems that have not been serviced, if the property owner will permit this step we recommend it. When the tank is pumped, ask the pumping contractor to describe the size, type, and condition of the tank and its components, and also to tell you if s/he saw any indications that the system needs repair or that the tank or leach system are at or near the end of their life.
Do not permit the septic tank to be pumped before the septic loading and dye test - that will prevent a valid test of the system and in particular, prevents loading of the drainfield. More details about the problem of septic tank pumpouts as a cover-up of a septic problem or failure are at Don't Pump Before Testing Septic Systems: warnings for home buyers about septic tank pumping.
The links given below describe the details of how to perform a septic loading and dye test, procedures, observations, water quantity, and septic dye quantity.
Also see The Septic Information Website - and see Septic Systems Inspection, Testing, & Maintenance online book on inspecting and maintaining septic systems, of which the document is a chapter. Technical review by industry experts has been performed and is ongoing - reviewers are listed at "References." Comments and suggestions for content are welcome.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about septic testing procedures: how to perform a loading and dye test on the septic system
Check the FAQs just above, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.
Design Manuals for Septic Systems
Onsite Wastewater Disposal Books