Diagnosing and Curing Sewer Gas Smells and Septic Tank Odors Caused by Site Problems
SITE, WEATHER, NEIGHBORS SEWER ODORS - CONTENTS: How building site conditions, wind, weather, or a neighbor's septic system can produce sewer or septic odors in or around buildings. How to find and cure ground water flooding the septic tank or drainfield. Sewer gas smell diagnosis - plumbing checklist. Septic gas smell diagnosis - septic system checklist
InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
This article describes how to diagnose, find, and cure odors in buildings including septic or sewage or sewer gas smells or "gas odors" in buildings
with a focus on homes with a private onsite septic tank but including tips for owners whose home is connected to a sewer system as well. What makes the smell in sewer gas? Sewer gases are more than an obnoxious odor.
Site Conditions, Weather Conditions, or Failing Neighboring Septic Systems or Plumbing Can Produce Local Sewer Gas Odors
Watch out: Because sewer gas contains
methane gas (CH4) there is a risk of an explosion hazard or even fatal asphyxiation. (METHANE GAS SOURCES)
[Click to enlarge any image]
Sewer gases also will typically contain HYDROGEN SULFIDE GAS (H2S). In addition some writers opine that there are possible
health hazards from sewer gas exposure, such as a bacterial infection of the sinuses (which can occur due to any sinus irritation).
Depending on the sewer gas source and other factors such as humidity and building
and weather conditions, mold spores may also be present in sewer gases.
Check for sources of ground water or surface water that are flooding your septic tank or drainfield. Runoff from roof drainage or surface or subsurface water can easily enter and flood a septic tank and drainfield, including at surprising locations such as an opening at the septic tank top, a crack in the septic tank, or an opening in a drain line entering or leaving the septic tank. Our photo (above left) shows Wappingers Creek in flood conditions (Dutchess County, New York) - nearby septic drainfields are also flooded and saturated.
Excavate and the soil around the drainfield: a few test holes, combined with a septic loading and dye test can tell us if the water flooding a septic field is coming from the building's septic tank and wastewater or from invading surface runoff.
Septic loading and dye test procedures are given in detail at this website. See Dye Tests: how to perform a Septic Loading and Dye Test - the complete procedure for septic loading & dye testing, a septic function test.
Use an intercept drain: Probably the most common problem, however, is ground water or surface water flooding the leach field, causing it to fail or back up. It may be possible to install intercept drainage around the septic field to salvage the system.
Check neighboring properties and drains: before digging up your yard and septic tank, walk around the neighborhood. Is the smell getting stronger as you walk away from your property? Perhaps a neighbor has a failing septic system or is having work performed on their septic system.
Check nearby storm drains for odor sources.
Check for unusual site and wind conditions: I've encountered buildings where all of the plumbing vent installations appear to be to code and complete, but where unusual terrain shape (house at the bottom of a large hill) and prevailing winds conspired (in some weather conditions) to blow septic gases back down from above the roof to a bedroom window or even to ground level.
Depending on the building roof shape, orientation, and prevailing or even uncommon wind direction, wind blowing at the building can cause downdrafts around a plumbing vent stack, sending normal sewer gases and odors back closer to the ground or even into the building.
If your sewer gas odors seem to correlate to windy conditions I'd check this out further. Extending the plumbing vents higher or installing a wind block at the vent top might help.
Weather: how rain and flooding can cause sewage odors at a building or site:
Rain or stormwater flooding a local sewer/storm drain system: can cause sewer gases to back up through a building's drain/waste/vent piping and into the building.
Flooding the private septic system drainfield causes sewage effluent to reach the surface
Failing septic drainfields: Even a septic drainfield that is not flooded may be smelly if it is improperly constructed or has lost its ability to treat septic effluent, but these conditions may be expected to be worse in wet weather
Flooding the septic tank, by invasive ground water, surface runoff, or from actual flood conditions is likely to also leave the system not functional and possibly releasing septic gases See SEPTIC SYSTEM FLOOD DAMAGE REPAIR
Other Sources of Smells that are less like "sewer gas" odors (in my opinion) include the odor of burning electrical components. If you trace odors to an appliance or fixture or switch, shut off electricity to that device (or un-plug it if it's an appliance) and have the system or appliance checked by a licensed electrician. Burning electrical components and insulation, and overheating florescent light ballasts can make quite an odor but that's the just a warning sign of an unsafe condition that needs prompt attention.
Submissions are invited: Contact Us if you have other examples of tracking down septic or sewer gas smells to their source. Credit and link-exchanges given.
Green link shows where you are in this article series.
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Thanks to Slade Franklin
for the reminder that a leaky wax ring at a toilet can lead to septic odors in bathrooms. 11/2007
Thanks to J.V. (privacy protected) for the reminder to make a detailed inspection of the plumbing vent system when sewer gas odors are present. 07/2008
Thanks to Roger Hankey & Cheryll Brown, www.hankeyandbrown.com, ASHI home inspectors in Minnesota, for the deteriorated transite pipe gas flue vent photograph and comments. Mr. Hankey is a past chairman of the ASHI Technical Committee, serves as co-chairman of ASHI legislative committee, and has served in other ASHI professional and leadership roles. 7/2007.
Drain Noises: may indicate defective or clogged plumbing: how to diagnose and cure drain sounds
Septic Tank/Soil-Absorption Systems: How to Operate & Maintain [ copy on file as /septic/Septic_Operation_USDA.pdf ] - , Equipment Tips, U.S. Department of Agriculture, 8271 1302, 7100 Engineering, 2300 Recreation, September 1982, web search 08/28/2010, original source: http://www.fs.fed.us/t-d/pubs/pdfimage/82711302.pdf.
Pennsylvania State Fact Sheets relating to domestic wastewater treatment systems include
Pennsylvania State Wastewater Treatment Fact Sheet SW-161, Septic System Failure: Diagnosis and Treatment
Pennsylvania State Wastewater Treatment Fact Sheet SW-162, The Soil Media and the Percolation Test
Pennsylvania State Wastewater Treatment Fact Sheet SW-l64, Mound Systems for Wastewater Treatment
Pennsylvania State Wastewater Treatment Fact Sheet SW-165, Septic Tank-Soil Absorption Systems
Document Sources used for this web page include but are not limited to: Agricultural Fact Sheet #SW-161 "Septic Tank Pumping," by Paul D. Robillard and
Kelli S. Martin. Penn State College of Agriculture - Cooperative Extension, edited and annotated by
Dan Friedman (Thanks: to Bob Mackey for proofreading the original source material.)
Books & Articles on Building & Environmental Inspection, Testing, Diagnosis, & Repair
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume. Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Or choose the The Home Reference eBook for PCs, Macs, Kindle, iPad, iPhone, or Android Smart Phones. Special Offer: For a 5% discount on any number of copies of the Home Reference eBook purchased as a single order. Enter INSPECTAEHRB in the order payment page "Promo/Redemption" space.
Builder's Guide to Wells and Septic Systems, Woodson, R. Dodge: $ 24.95; MCGRAW HILL B; TP;
Quoting from Amazon's description: For the homebuilder, one mistake in estimating or installing wells and septic systems can cost thousands of dollars. This comprehensive guide filled with case studies can prevent that. Master plumber R. Dodge Woodson packs this reader-friendly guide with guidance and information, including details on new techniques and materials that can economize and expedite jobs and advice on how to avoid mistakes in both estimating and construction. Chapters cover virtually every aspect of wells and septic systems, including on-site evaluations; site limitations; bidding; soil studies, septic designs, and code-related issues; drilled and dug wells, gravel and pipe, chamber-type, and gravity septic systems; pump stations; common problems with well installation; and remedies for poor septic situations. Woodson also discusses ways to increase profits by avoiding cost overruns.
Country Plumbing: Living with a Septic System, Hartigan, Gerry: $ 9.95; ALAN C HOOD & TP;
Quoting an Amazon reviewer's comment, with which we agree--DF:This book is informative as far as it goes and might be most useful for someone with an older system. But it was written in the early 1980s. A lot has changed since then. In particular, the book doesn't cover any of the newer systems that are used more and more nowadays in some parts of the country -- sand mounds, aeration systems, lagoons, etc.