Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SEPTIC CARE INSTRUCTIONS
SEPTIC D-BOX INSTALL REPAIR
SEPTIC DRAINFIELD FAILURE DIAGNOSIS
SEPTIC DYE TEST PROCEDURE
SEPTIC FAILURE SIGNS
SEPTIC INSPECTION & TEST GUIDE
SEPTIC LIFE EXPECTANCY
SEPTIC SUPPLIES & PARTS
SEPTIC SYSTEM DESIGN ALTERNATIVES
SEPTIC SYSTEM DESIGN BASICS
SEPTIC SYSTEMS, HOME BUYERS GUIDE to
SEPTIC SYSTEM SAFETY WARNINGS
SEPTIC TREATMENTS & CHEMICALS
SEWAGE & SEPTIC CONTAMINANTS
SEWAGE BACKUP, WHAT TO DO
SEWAGE BACKUP TEST & CLEANUP
SEWAGE BACKUP PREVENTION
SEWAGE CONTAMINATION in buildings
SEWAGE CONTAMINANTS in FRUIT / VEGETABLES
SEWAGE EJECTOR / GRINDER PUMPS
SEWAGE LEVELS in SEPTIC TANKS
SEWAGE NITROGEN CONTAMINANTS
SEWAGE PATHOGENS in SEPTIC SLUDGE
SEWER GAS ODORS
SEWER LINE REPLACEMENT
SINKHOLES, WARNING SIGNS
SMELL PATCH TEST to Track Down Odors
SOAKAWAY BED FAILURE DIAGNOSIS
SULPHUR & SEWER GAS SMELL SOURCES
TOILETS, INSPECT, INSTALL, REPAIR
ALTERNATIVE & WATERLESS TOILETS
TOILETS, DON'T FLUSH LIST
TRAPS on PLUMBING FIXTURES
TREATMENTS & CHEMICALS, SEPTIC
VIDEO GUIDES: Septic Videos
WATER CONSERVATION MEASURES
WATER SOFTENERS & CONDITIONERS
WATER SUPPLY & DRAIN PIPING
WATER, WELLS, WATER TANKS: TESTING GUIDE
WASHING MACHINES & SEPTIC SYSTEMS
WASTEWATER TREATMENT BASICS
WINTERIZE A BUILDING
Septic system D box inspection & problem diagnosis: procedures for inspecting or diagnosing problems at the the septic drainfield distribution box, or the "D-box" or "drop box". If the D-box is leaking, smells, or is tipped, clogged, or otherwise not working this article describes how to diagnose & fix the trouble.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
The distribution box (more than one may be in use) connects a single effluent line from the septic tank to a network of absorption system components such as drainfield leach lines or to a network of seepage pits or galleys.
The photo (left) shows the adjustable weir outlets that permit balancing flow among drainfield lines. (Source EPA who used photo from Ayres Associates.) More sketches of D-box layouts and configurations are shown in this EPA drawing.
Inspection Points at the Septic Drop Box
Regulating effluent distribution: In good system design the outlet openings from the distribution box to each drainfield line can be adjusted to regulate the flow among the various absorption lines.
Elegantly simple, a plug with an eccentric hole is inserted into the end of each leach line fed from the D-box. By turning the plug in the end of the leach line pipe one can place the eccentric hole higher or lower with respect to the bottom of the distribution box, thus compensating for a slightly tipped box, differences in leach line length, or differences in leach line condition.
Uneven effluent distribution: If a distribution box becomes tipped (or clogged) effluent may be routed to only a portion of the absorption system, thus overloading it and leading to a "breakout" of effluent at the surface or to clogging and system backup.
An examination of the septic system distribution box interior may show flood lines in the box if the drain field has been clogged or saturated in the past even if at the time of inspection the box is not flooded.
If the septic drainfields have been flooded you should be pessimistic about the remaining life of the absorption system.
If the septic drainfield distribution box is tipped and/or septic system effluent arriving from the septic tank has not been uniformly distributed among the drainfield lines (assuming they are of equal length and in equally good soils), only a simple adjustment of the outflow may be needed.
Round plugs with eccentric openings may be present or can be inserted in the D-box outlet openings to regulate flow among the individual absorption lines. (C)Trap Daniel Friedman Copyright Protected text. Also see ALTERNATING BED SEPTIC SYSTEMS.
Tipped or flooded distribution boxes, resulting in uneven loading of soil absorption system lines. This condition can flood one or two lines leading to early field failure.
Continue reading at SEPTIC D-BOX PIPING or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References