Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SEPTIC CARE INSTRUCTIONS
SEPTIC D-BOX INSTALL REPAIR
SEPTIC DRAINFIELD FAILURE DIAGNOSIS
SEPTIC DYE TEST PROCEDURE
SEPTIC FAILURE SIGNS
SEPTIC INSPECTION & TEST GUIDE
SEPTIC LIFE EXPECTANCY
SEPTIC SUPPLIES & PARTS
SEPTIC SYSTEM DESIGN ALTERNATIVES
SEPTIC SYSTEM DESIGN BASICS
SEPTIC SYSTEMS, HOME BUYERS GUIDE to
SEPTIC SYSTEM SAFETY WARNINGS
SEPTIC TREATMENTS & CHEMICALS
SEWAGE & SEPTIC CONTAMINANTS
SEWAGE BACKUP, WHAT TO DO
SEWAGE BACKUP TEST & CLEANUP
SEWAGE BACKUP PREVENTION
SEWAGE CONTAMINATION in BUILDINGS
SEWAGE CONTAMINANTS in FRUIT / VEGETABLES
SEWAGE EJECTOR / GRINDER PUMPS
SEWAGE LEVELS in SEPTIC TANKS
SEWAGE NITROGEN CONTAMINANTS
SEWAGE PATHOGENS in SEPTIC SLUDGE
SEWER GAS ODORS
SEWER LINE REPLACEMENT
SINKHOLES, WARNING SIGNS
SMELL PATCH TEST to FIND ODOR SOURCE
SOAKAWAY BED FAILURE DIAGNOSIS
SULPHUR & SEWER GAS SMELL SOURCES
TOILETS, INSPECT, INSTALL, REPAIR
ALTERNATIVE & WATERLESS TOILETS
TOILETS, DON'T FLUSH LIST
TRAPS on PLUMBING FIXTURES
TREATMENTS & CHEMICALS, SEPTIC
VIDEO GUIDES: Septic Videos
WATER CONSERVATION MEASURES
WATER SOFTENERS & CONDITIONERS
WATER SUPPLY & DRAIN PIPING
WATER, WELLS, WATER TANKS: TESTING GUIDE
WASHING MACHINES & SEPTIC SYSTEMS
WASTEWATER TREATMENT BASICS
WINTERIZE A BUILDING
Diagnose problems at the septic system drop box: procedures for troubleshooting leaks, smells, or backups & flooding in the septic system D-box.
Septic system D box installation, specifications, inspection, diagnosis, and repair: in this article series about septic system drop boxes we describe the best procedures for locating and inspecting, repairing or replacing the septic drainfield distribution box, or the "D-box" or "Splitter box". If the D-box is leaking, smells, or is tipped, clogged, or otherwise not working this article describes how to diagnose & fix the trouble.
Green links show where you are. © Copyright 2015 InspectApedia.com, All Rights Reserved.
Reader Question: Tipped septic effluent distribution box, standing water at end of one leach line
I have been told that the way that fitting is angled down low and how it comes in angled is bad. It is making me worried. I am essentially being old that it should be redone.
We have Type III soils, very sandy with 2 - 75' long infiltrators.
Three years ago during the wet season I noticed some standing water at the end of one of the laterals.
It was the lateral that receives all the effluent when no levelers are in place. - Nicholas Day
With thanks to clarifications from reader Doug (March 2013), we recap the effluent distribution piping connections to this D-box as follows:
Without the elbow, effluent flows more forcibly across the box and into the opposing outlet, but very little effluent will make the 90-degree turn into the perpendicular outlet. This is a very common installation practice
If you knew for example that one of your lines was much longer than the other, you'd send more effluent to the longer line - presuming they are both working ok.
As you report that one of the laterals showed a sign of failure during wet weather several years ago, you might want to try to re-balance the effluent flow sending more (or perhaps temporarily, most) of the effluent into the other drainfield line. But to have an accurate idea of the condition of the drainfield sections or leach lines before adjusting the effluent flow in your D-Box, the best step would be to carefully excavate near the end of each of the two leach lines (presuming you don't already have inspection ports installed). Look at the condition of the soils there, particularly, look for standing water or effluent.
Because the D-box is a small thing and not deep, it shouldn't be a big job nor too costly to dig it out, install a larger one, make sure the D-box is not tipped, and that effluent is flowing as desired into both of the drainfield lines.
But you should also check the septic tank condition, especially the outlet baffle, and the scum/sludge levels, to be sure the tank is pumped on schedule (SEPTIC TANK PUMPING SCHEDULE) and that the baffles are in place and working. (SEPTIC TANK BAFFLES).
Another problem that could send sludge into the D-box would be a septic tank that floods from groundwater leaking into it, so you will want to check that too. At also see SEPTIC TANK INSPECTION PROCEDURE, and SEPTIC TANK INSPECTION PROCEDURE, and finally, see Septic Tank Leaks.
Question: during a septic test the trenches "took on water" - they think the D box is kiltered. What does that mean and how do I fix it?
I had a Hydraulic Load test done and the trenches were taking on water...they think the D box is kiltered. Can you explain this and what are the recommendations to have it fixed? - Reen
Reply: a tipped d-box does not distribute effluent evenly among the drainfield lines and can cause flooded drainfields
Sure Reen: someone is making things sound like rocket science instead of simple ditch-digging.
Question: The d-box is not distributing effluent evenly among my three drywells. Is it likely to be a tipped d box or a clog?
I have an old 3-drywell system fed from a d-box in the center of the 3 drywells (laid out on 3 points of an equilateral triangle). The system has had minimal use but one drywell is full and the other 2 are bone dry. Should they all be being fed in parallel or in series (one fills before the next)? Is there likely a tip or a clog? - Jeff O
Reply: Drywells are often installed and fed in series; if yours are in parallel, set the D box to send effluent to all of them.
Often drywells were installed in series - not in parallel. If that's how yours were piped, then if you can confirm that the full drywell has an outlet pipe that drains into the next (dry) one in the series you should be OK. If that connection is missing I'd add it.
Continue reading at SEPTIC D-BOX FLOODING or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References