Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
PLUMBING SYSTEM INSPECT DIAGNOSE REPAIR
AGE of PLUMBING MATERIALS & FIXTURES
AIR DISCHARGE at FAUCETS, FIXTURES
ANTI SCALD VALVES
ANODES & DIP TUBES on WATER HEATERS
BACKUP PREVENTION, SEPTIC
BACKUP PREVENTION, SEWER LINE
BACKWATER VALVES, SEWER LINE
BATH & KITCHEN DESIGN GUIDE
CHEMICAL CONTAMINANTS in WATER
CHLORINE IN DRINKING WATER
DEBRIS in WATER SUPPLY, Water Heater
DEPTH of SEPTIC TANK
DRAIN & SEWER PIPING
FAUCETS & CONTROLS, KITCHEN & BATH
FAUCETS, OUTDOOR HOSE BIBBS
FLOOD DAMAGE ASSESSMENT, SAFETY & CLEANUP
FLOOR DRAIN / TRAP ODORS
FLUSHOMETER VALVES for TOILETS URINALS
GAS PIPING, VALVES, CONTROLS
GALVANIC SCALE & METAL CORROSION
HARD WATER - SOFTENERS
HEAT TAPES, Heat, Insulation prevent Freeze-Up
LEAD POISONING HAZARDS GUIDE
LEAD IN DRINKING WATER, HOW to REDUCE
METHANE GAS SOURCES
MIXING / ANTI-SCALD VALVES
MUNICIPAL WATER PRESSURE IMPROVEMENTS
NOISE / SOUND DIAGNOSIS & CURE
ODORS GASES SMELLS, DIAGNOSIS & CURE
ODORS IN WATER
ODORS, SEPTIC or SEWER
ODORS SEWER GAS in COLD WEATHER
ODORS, SULPHUR SMELL SOURCES
ANIMAL or URINE ODOR SOURCE DETECTION
PIPING IN BUILDINGS, Clogs Leaks Types
PLUMBING FIXTURES, KITCHEN, BATH
PLUMBING NOISE CONTROL
PLUMBING VENT DEFINITIONS & CODES
PLUMBING VENT DEFECTS & NOISES
PUMPS, WATER REPAIR
RELIEF VALVE LEAKS
RELIEF VALVES - TP Valves on Boilers
RELIEF VALVES - STEAM TP VALVES
RELIEF VALVES - Water Heaters
RELIEF VALVES - Water Tanks
REPAIR BURST LEAKY PIPES
SEPTIC METHANE GAS
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SHUTOFF VALVE LOCATION, USE
SULPHUR & SEWER GAS SMELL SOURCES
SWEATING (CONDENSATION) on PIPES, TANKS
TOILETS, INSPECT, INSTALL, REPAIR
WATER, WELLS, WATER TANKS: TESTING GUIDE
WATER PRESSURE LOSS DIAGNOSIS & REPAIR
WATER PUMPS & TANKS
WATER SOFTENERS & CONDITIONERS
WATER SOURCE ALTERNATIVES
WATER SUPPLY & DRAIN PIPING
WATER SHUTOFF VALVE LOCATION, USE
WATER SHUTOFF VALVE, WELL PUMP
WATER TESTS, CONTAMINANTS, TREATMENT
WELLS CISTERNS & SPRINGS
WINTERIZE A BUILDING
This RV and chemical toilet article describes acceptable ways to empty a chemical toilet, porta-potty, or RV waste holding tank, and answers the question of when these can be emptied into a residential septic tank. Chemical toilets with larger waste reservoirs are used in RV's and campers as well as for full-sized portable toilets or Porta-Johns used at construction sites and at outdoor festivals. Other common portable toilets include models from Sears, the Coleman, and Reliance toilets who provide a hassock model portable chemical toilet. Our page top photo shows a chemical toilet set atop a septic tank service riser. The chemical toilet's holding tank has been removed so that the toilet empties directly into the septic tank - a perfectly functional emergency toilet setup, but unstable and of course lacking in privacy.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved.
We would not hesitate to occasionally dump a portajohn or small, portable, chemical toilet into a home septic tank - the volumes are so low, typically two gallons or so total, that the deodorants or disinfectants in that small container would be so dilute as not to harm the tank bacteria.
But not only in view of the typical state standard on dumping chemical toilets into the environment, but further and more serious, an RV is a different matter as the holding tank is much bigger. It depends on what chemicals you're using in your RV holding tank. I'd contact the manufacturer and ask for their literature on this point - if you get something from the manufacturer of your product, pass it on to me.
Here's one example of one manufacturer's comment about dumping RV chemicals into a septic:: "Yes [you can empty your RV holding tank into your septic system], as long as your septic system is fully functioning, adequately sized and properly maintained. If you do, it's important to use only the recommended amount of deodorant in your holding tank and only empty when the tank is full.
Also, because holding tank waste is very concentrated and breakdown takes longer, we recommend you dump only one RV holding tank in a home septic system per week." --Copyright © 2010 Thetford Corporation.
How Much Holding Tank Deodorant Chemical to Use
Biodegradable RV Toilet & Holding Tank Fluids?
Calculations and Data to Evaluate the Effect of Dumping RV Holding Tanks Into a Septic Tank
Comment-DF: What's missing from this is a more scholarly explanation that includes real data such as:
What are the problems if we empty an RV or other waste holding tank into the septic system?
The concern with dumping RV disinfectants or any chemical into a septic system is that high concentrations of a disinfectant may not only harm the natural bacterial and other actions that occur in the septic tank, worse, it could harm the biomat which forms under and is essential for proper functioning of the drainfield. With some chemicals there is also the risk that the chemical itself is an environmental contaminant. You can understand why New York State and perhaps other states have taken the position quoted just above.
Considering that the chemical manufacturer says they are confident that their chemical won't harm the system if we follow their instructions, then if you want to develop some real test data, after checking with your local health department to discuss doing a mini-study of this kind:
Go ahead and empty your RV tank into the septic system, Once only, making a note of the volume dumped and the other information listed above. If you don't already have one, install a riser port at the septic tank pumping opening so that you can use the same riser port as a dumping station. You'll just pull the cap off of the riser pipe and connect your RV dumping hose to it.
What else should we do to avoid Damaging the Septic System with our RV?
NOW: since you're putting sewage along with deodorant (which probably retards sewage breakdown) into the septic tank, and since we don't have any quantitative data from the manufacturer about how many RV gallons can go how often into a septic tank of any given size (I doubt they know), I would respond by moving up my septic tank pumping schedule to an earlier date.
A Proposed Septic Tank Pumping Schedules if We Empty an Recreational Vehicle Holding Tank into the Septic Tank
The below is ARBITRARY to use as a starting point -
RV gallons put into Next septic tank Move your tank tank in one year pumpout was due up sooner by 250 gals 1 year 2 months 500 gals 1 year 4 months 250 gals 2 years 0 months 500 gals 2 years 2 months 250 gals 3 years 0 months 500 gals 3 years 0 months 1000 gals 3 years 4 months
FOLLOWUP: IF, when you pump the septic tank+RV-waste and your pumper says that there was no unusually thick floating scum or settled sludge or suspended solid waste, you can begin to push the septic tank pumping schedule back out to the frequency given in my table.
If I can get some more accurate data I will amend this current table (which is completely made-up and speculative) and post it online.
Products - for Alternative Septic System Designs aerobic system pumps, media filters, gravelless systems, other advanced wastewater treatment products including waterless, low water, chemical, and incinerating toilets.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about problems with the operation of aerobic septic systems
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.
Design Manuals for Septic Systems
Onsite Wastewater Disposal Books