Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
SEPTIC SYSTEM INSPECT DIAGNOSE REPAIR
SEPTIC CARE INSTRUCTIONS
SEPTIC D-BOX INSTALL REPAIR
SEPTIC DRAINFIELD FAILURE DIAGNOSIS
SEPTIC DYE TEST PROCEDURE
SEPTIC FAILURE SIGNS
SEPTIC INSPECTION & TEST GUIDE
SEPTIC LIFE EXPECTANCY
SEPTIC SUPPLIES & PARTS
SEPTIC SYSTEM DESIGN ALTERNATIVES
SEPTIC SYSTEM DESIGN BASICS
SEPTIC SYSTEMS, HOME BUYERS GUIDE to
SEPTIC SYSTEM SAFETY WARNINGS
SEPTIC TREATMENTS & CHEMICALS
SEWAGE BACKUP PREVENTION
SEWAGE EJECTOR / GRINDER PUMPS
SEWER GAS ODORS
SEWER LINE REPLACEMENT
SINKHOLES, WARNING SIGNS
SOAKAWAY BED FAILURE DIAGNOSIS
SULPHUR & SEWER GAS SMELL SOURCES
TOILETS, INSPECT, INSTALL, REPAIR
TRAPS on PLUMBING FIXTURES
TREATMENTS & CHEMICALS, SEPTIC
VIDEO GUIDES: Septic Videos
WATER CONSERVATION MEASURES
WATER SOFTENERS & CONDITIONERS
WATER SUPPLY & DRAIN PIPING
WATER, WELLS, WATER TANKS: TESTING GUIDE
WASHING MACHINES & SEPTIC SYSTEMS
WASTEWATER TREATMENT BASICS
WINTERIZE A BUILDING
Sewage or wastewater flow rate assumptions & specifications for septic designers: these model septic design regulations discuss sewage flow rates to be used in designing onsite wastewater treatment facilities for individual households.
This document uses the New York State wastewater treatment standard for individual household septic systems (Appendix 75-A) to provide an example of state regulated design and installation of both conventional tank and leach field septic systems and alternative septic system designs, including raised septic systems, septic mound systems, intermittent sand filter septic systems, and evaportion-transpiration septic systems.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Model source: New York State Septic Regulation Appendix 75-A.3 - Sewage flows - Effective Date: 12/01/90 or later and cited in detail at REFERENCES. The page top photo of campers at Camp Virginia (1950's) appears in our detailed discussion of OUTHOUSES & LATRINES.
Definition of daily design flow of wastewater
The daily design flow is the volume of wastewater that should be assumed when determining the volume of wastewater that the sewage system (septic system or soakbed or drainfield or other treatment system) must be capable of handling. "Handling" means both adequate treatment and disposal without discharge of wastewater to the surface, to nearby waterways or to other unacceptable locations.
The following table gives septic system design flow rates that shall be assumed by septic system designers, giving flows in gallons of wastewater per day per bedroom in the home served by a private onsite wastewater disposal system, that is, a private septic system. Different septic design flow rates are assumed depending on the modernity and efficiency or water usage rate of the plumbing fixtures in the home. --DF
Continue reading at SEPTIC DRAINFIELD SIZE where we provide wastewater application rates and a detailed table of septic soakbed or leachfield or drainfield size as a function of soil percolation rate and wastewater volume flow in gallons per day, or select a topic from the More Reading links shown below.
Suggested citation for this web page
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about the septic blackwater or wastewater input flow rate assumptions that should be used by septic system and septic component designers - model septic regulations.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References