Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
WATER PUMPS, TANKS, TESTS, WELLS, REPAIRS
WATER CONTAMINANT LEVELS
WATER HAMMER NOISE DIAGNOSE & CURE
WATER ODORS, CAUSE CURE
WATER PUMP REPAIR GUIDE
WATER PRESSURE LOSS DIAGNOSIS & REPAIR
WATER PUMP SHORT CYCLING
WATER SOFTENERS & CONDITIONERS
WATER TANK REPAIR PROCEDURES
WATER TANK: USES, TROUBLESHOOTING
WATER TESTS, CONTAMINANTS, TREATMENT
WATER TREATMENT EQUIPMENT CHOICES
WELLS CISTERNS & SPRINGS
WELL FLOW RATE
WELL WATER PRESSURE DIAGNOSIS
WELL YIELD IMPROVEMENT
WINTERIZE A BUILDING
Hard water or high mineral content water supply: how to recognize that you need a water softener by simple visual inspection of fixtures in the building . Here is a description of what to look for and where to find it in diagnosing hard water conditions.
Green links show where you are. © Copyright 2013 InspectAPedia.com, All Rights Reserved.
Hard water is not just an aesthetic concern in the shower. Very hard water can clog pipes [photo of scale build-up in a water pipe] and water heating equipment (especially tankless coils such as the ones we show here) leading to costly repairs.
Hard water is not normally health concern people although the treatment of hard water using a conventional ion-exchange (salt) water softener can, especially if improperly adjusted, place salt (NaCl) into the water supply at a level which people on low-salt or no-salt diets may wish to avoid.
We discuss this point further at HOW SOFTENERS WORK.
Separately at WATER TESTING GUIDE we describe easy tests you can make to actually measure the hardness of the building water supply.
Here are some visual clues that the water supply at a building is hard
There is a water softener installed - look for the water softener treatment tank and salt tank, usually installed close to where water enters the building or close to the water pressure tank and pump controls if a private well is in use.
Hot water pressure is noticeably less than cold water pressure in the building.
Since minerals precipitate out of hard water faster when the water is heated, we expect hot water piping to clog with minerals faster than cold water piping.
Signs of tankless coil clogging from hard water: When a tankless coil is installed, since that's where our water is the hottest, often the tankless coil clogs before other plumbing materials.
Our photo at left looks up into the mouth of a bathroom faucet spout, showing minerals deposited by three years of exposure to hard well water.
Stained plumbing fixtures such as the bath tub shown in this photo often tell a lot about the history of a building as well as the condition of its water supply.
Hard Water Lime Deposits in Other Problem Locations
White lime deposits have been reported on roofs where leaky swamp coolers were installed - WHITE STAINS on ROOFS
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about visual clues indicating that a building water supply is high in mineral content - has "hard water"
Ask a Question or Enter Search Terms in the InspectApedia search box just below.
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.
Design Manuals for Septic Systems
Onsite Wastewater Disposal Books