FLOODED SEPTIC SYSTEMS, REPAIR - CONTENTS: How to evaluate & repair or return to service a flooded septic tank & septic fields. Safety advice for flooded septic systems & how to get a flooded septic system working again, when to pump the septic tank, what to look for. Flood damage septic systems. Septic system flooding research.
POST a QUESTION or READ FAQs about flooded septic tanks and flooded drainfields or soakaway beds - what to do to restore the septic system to safe functional operation
InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Flooded septic tanks and drainfields - advice:
If your septic system has been exposed to flooding, this document gives immediate safety and health advice and includes
other advice from the U.S. EPA and other septic system experts. We set priorities: safety, health, maintenance, and repair
for septic systems after flooding.
Yin et als (2011) point out that problems associated with flooded septic systems will increase significantly as sea levels and tide levels continue to rise around the world. In addition to describing steps to return a septic system to operation after flooding, this article includes recommendations and research on the construction of flood-damage-resistant decentralized or onsite septic systems.
The photo at page top shows storm-flooding of Wappingers Creek in Dutchess County, New York. Homes built along this creek have septic soakbeds or drainfields located not only in a flood zone but too close to this waterway.
Citation of this article by reference to this website and brief quotation for the sole purpose of review are permitted
The following text is not part of the original US EPA document but has been added by this website author.
Emergency Response: Septic System Safety in Flooded Areas
Immediate Serious Safety Hazards: Property owners whose septic system has been flooded should be concerned first for immediate safety hazards
such as the increased risk of a dangerous collapse of a site-built septic tank, drywell, or cesspool. A site-built system, such as
a cesspool made of dry-laid stone or concrete blocks, may have been weakened by floodwaters.
Rope off and prevent access to the area
where such systems are installed until you have made certain that there is no danger of collapse. Someone walking over a weakened
septic tank cover or cesspool or drywell could fall in - a possible fatal event. Never leave the cover off of a septic tank,
cesspool, or manhole. Someone can fall-in.
Electrical Hazards: if your septic system includes electrical components such as pumps, be sure that electrical power
has been turned off before attempting to examine the equipment.
Health Hazards: the EPA advice on this topic (below) refers to the high risk of sewage backup into homes during flooding. Sewage backup
into a home leaves a variety of pathogens and creates a serious risk of hidden mold in buildings.
Both of these can
create health hazards, particularly for people who are at extra risk: infants, the elderly, people who are immune-impaired,
people with asthma, etc.
Further investigation, testing,
and cleaning are likely to be in order. A simple "pumpout" of a flooded basement, for example, may leave wet building materials and insulation
if the basement walls were finished with drywall or paneling. In these cases the wet materials should be removed promptly, the area dried,
cleaned if needed, and inspected for evidence of contamination before rebuilding.
Major Structural or System Damage: do not enter a flooded structure if there is evidence that the building may be unstable
or in danger of collapse. A building which has shifted off of its foundations, evidence of subsidence (depressions in the soil) over or near a septic system (or anywhere else),
or buckled foundation walls are examples of dangerous conditions that merit professional inspection and advice.
Manholes and Tank Covers may have shifted or may even have been lost during flooding. Falling into an open septic tank or sewer
is likely to be fatal. Watch for open, shifted, damaged, or otherwise unsafe covers or openings to these systems.
Property owners whose septic systems have been flooded should read the following articles as well as the advice offered
from the U.S. Environmental Protection Agency and re-printed below.
SEWAGE CONTAMINATION TEST how to test buildings for bacterial contamination from Sewage and Septic backup, remediation, & references
SEPTIC TANK SAFETY Septic System, Septic Tank, & Cesspool Safety Warnings for Septic Inspectors, Septic Pumpers, and Homeowners
The information below is provided by the U.S. EPA. Additional comments or suggestions, where provided by the web author, will
be flagged as added text (such as the paragraphs preceding this section. I have re-ordered some of the original EPA text to put the
obvious and most important information first. [DJF]
What do I do with my septic system after the flood?
Once floodwaters have receded, there are several things homeowners should remember:
Be sure the septic tank's manhole cover is secure and that inspection ports have not been blocked or damaged. Otherwise someone could fall into the septic tank - a fatal hazard.
Do not use the sewage system until the water level in the soil absorption field is lower than the water level around the house.
Have your septic tank professionally inspected and serviced if you suspect damage. Signs of damage include settling or an inability to accept water.
Most septic tanks are not damaged by flooding since they are below ground and completely covered. However, septic tanks and pump chambers can fill with silt and debris, and must be professionally cleaned.
If the soil absorption field is clogged with silt, a new system may have to be installed. [DF: check the area of the drain field for piping which has become exposed (soil loss) or piping which has become clogged with mud and silt.]
Only trained specialists should clean or repair septic tanks because tanks may contain dangerous gases. Contact your health department for a list of septic system contractors who work in your area.
If sewage has backed up into the basement, clean the area and disinfect the floor. Use a chlorine solution of a half cup of chlorine bleach to each gallon of water to disinfect the area thoroughly.
Pump the septic system as soon as possible after the flood. Be sure to pump both the tank and lift station. This will remove silt and debris that may have washed into the system. Do not pump the tank during flooded or saturated drainfield conditions. At best, pumping the tank is only a temporary solution. Under worst conditions, pumping it out could cause the tank to try to float out of the ground and may damage the inlet and outlet pipes.
Do not compact the soil over the soil absorption field by driving or operating equipment in the area. Saturated soil is especially susceptible to compaction, which can reduce the soil absorption field's ability to treat wastewater and lead to system failure.
Examine all electrical connections for damage before restoring electricity. This includes electrical connections for pumps that may be used in your septic system: a septic grinder pump, effluent pump, or ejector pump.
Check the vegetation over your septic tank and soil absorption field. Repair erosion damage and sod or reseed areas as necessary to provide turf grass cover.
[DF: if your septic system uses special equipment such as a packaged aerobic treatment unit or other packaged wastewater treatment systems,
check with the system manufacturer. Some manufacturers will void the system warranty if sealed components are opened by the homeowner.]
Remember: Whenever the water table is high or your sewage system is threatened by flooding there is a risk that sewage
will back up into your home. The only way to prevent this backup is to relieve pressure on the system by using it less.
Where can I find information on my septic system?
Please contact your local health department for additional advice and assistance.
For more information on onsite/decentralized wastewater systems, call the National Environmental Services Center at
(800) 624-8301 or visit their website at www.nesc.wvu.edu.Exit EPA Disclaimer
How to Find The Septic Tank - (added by web author)
Septic Tank Location - How to Find the Septic Tank, how deep will the cover be, how to document its location
Do I pump my tank during flooded or saturated drainfield conditions?
No! At best, pumping the tank is only a temporary solution.
Under worst conditions, pumping it out could cause the tank to try to float out of the ground and may damage the
inlet and outlet pipes. The best solution is to plug all drains in the basement and drastically reduce water use in the house.
[DF NOTE: As the EPA says above, however, pump and inspect the septic system (including the piping)
as soon as possible after the flood, just not so
soon that there is risk of floating the septic tank.
If a septic system is not going to be used for months and wet weather or high
ground water conditions are expected to continue, I would not pump a fiberglass or plastic septic tank as there is risk
that the tank will float up out of the ground.
This is not much of a risk with concrete septic tanks.
Be sure to pump both the tank and lift station. Further inspection for safety as well as the overall
condition of the system is needed.]
When to Pump a Septic Tank - (added by web author)
What if my septic system has been used to dispose wastewater from my business (either a home-based or small business)?
In addition to raw sewage, small businesses may use their septic system to dispose of wastewater containing chemicals.
If your septic system that receives chemicals backs up into a basement or drain field take extra precautions to prevent skin,
eye and inhalation contact.
The proper clean-up depends of what chemicals are found in the wastewater.
Contact your State or EPA for specific clean-up information.
Suggestions for Homeowners with Flooded Septic Systems?
Use common sense. If possible, don't use the system if the soil is saturated and flooded. The wastewater will not be treated and will become a source of pollution. Conserve water as much as possible while the system restores itself and the water table fails.
Prevent silt from entering septic systems that have pump chambers. When the pump chambers are flooded, silt has a tendency to settle in the chambers and will clog the drainfield if it is not removed.
Do not open the septic tank for pumping while the soil is still saturated. Mud and silt may enter the tank and end up in the drainfield. Furthermore, pumping out a tank that is in saturated soil may cause it to "pop out" of the ground. (Likewise, recently installed systems may "pop out" of the ground more readily than older systems because the soil has not had enough time to settle and compact.)
Do not dig into the tank or drainfield area while the soil is still wet or flooded. Try to avoid any work on or around the disposal field with heavy machinery while the soil is still wet. These activities will ruin the soil conductivity.
Flooding of the septic tank will have lifted the floating crust of fats and grease in the septic tank. Some of this scum may have floated and/or partially plugged the outlet tee. If the septic system backs up into the house check the tank first for outlet blockage.
Clean up any floodwater in the house without dumping it into the sink or toilet and allow enough time for the water to recede. Floodwaters from the house that are passed through or pumped through the septic tank will cause higher flows through the system. This may cause solids to transfer from the septic tank to the drainfield and will cause clogging.
Locate any electrical or mechanical devices the system may have that could be flooded to avoid contact with them until they are dry and clean.
AEROBIC Septic systems, septic plants, upflow filters, trickling filters, and other media filters have a tendency to clog due to mud and sediment. These systems will need to be washed and raked.
Aftias, E. "Considerations for the first application of source control measures for stormwater runoff in the Athens metropolitan area." In Advances in Urban Stormwater and Agricultural Runoff Source Controls, pp. 141-146. Springer Netherlands, 2001.
Aldwell, C. R., R. Thorn, and D. Daly. "Point source pollution in karst areas in Ireland." In Proc. 21st Congress, International Association Hydrogeologists,(Ed) Daoxian Y, Beijing, pp. 1046-52. 1988.
Brown, Clive, Joe Burkhart, Nancy Burton, Jean Cox-Ganser, Scott Damon, Henry Falk, Scott Fridkin et al. Mold prevention strategies and possible health effects in the aftermath of hurricanes and major floods. US Department of Health and Human Services, Centers for Disease Control and Prevention, 2006.
Burby, Raymond J., and Steven P. French. "Coping with floods: the land use management paradox." Journal of the American Planning Association 47, no. 3 (1981): 289-300.
Burby, Raymond J., and Steven P. French. "The US experience in managing flood plain land use." Disasters 4, no. 4 (1980): 451-457.
Ferguson, Bruce K. Introduction to stormwater: concept, purpose, design. John Wiley & Sons, 1998.
Few, Roger, G. T. Pham, and T. T. H. Bui. "Living with floods: health risks and coping strategies of the urban poor in Vietnam." Research project funded by British Academy (Committee for South East Asian studies), research report, May (2004).
Kilduff, James E. "Design and construction of leaching systems in fill based on permeability." Journal of Environmental Engineering 115, no. 1 (1989): 239-256.
Laak, Rein, Kent A. Healy, and Dan M. Hardisty. "Rational Basis for Septic Tank System Designa." Groundwater 12, no. 6 (1974): 348-351.
Odemerho, Francis O. "Flood control failures in a third world city: Benin City, Nigeria—Some environmental factors and policy issues." GeoJournal 29, no. 4 (1993): 371-376.
Pettry, D. E., and C. S. Coleman. "Two decades of urban soil interpretations in Fairfax County, Virginia." Developments in Soil Science 4 (1974): 27-34.
Salati Jr, E., Eneida Salati, and E. Salati. "Wetland projects developed in Brazil." Water science and technology 40, no. 3 (1999): 19-25.
Sharma, Vinod K., and Tanu Priya. "Development strategies for flood prone areas, case study: Patna, India." Disaster Prevention and Management 10, no. 2 (2001): 101-110.
Spaling, Harry, and Bryan Vroom. "Environmental assessment after the 2004 tsunami: a case study, lessons and prospects." Impact Assessment and Project Appraisal 25, no. 1 (2007): 43-52.
Swann, Chris. "The influence of septic systems at the watershed level." Watershed Protection Techniques 3, no. 4 (2001): 821-834.
Tucker, David L., and Nestor D. Vivado. "Design of an overland flow system." Journal (Water Pollution Control Federation) (1980): 559-567.
Waananen, Arvi O. Flood-prone areas and land-use planning: selected examples from the San Francisco Bay region, California. No. 942. US Govt. Print. Off., 1977.
Webb, Maureen, "Sewage Treatment for Flood Risk Sites", WTE Ltd., Water Technology, Ltd., UK Tel: 01759 369915, Website: http://www.wte-ltd.co.uk/, - commented here 12/10/2014" "The UK Environment Agency asked us to develop a solution for flood risk sites in the UK and have approved this method. " - retrieved 10/12/2014 original source: www.wte-ltd.co.uk/sewage_treatment_flood_risk.html
This sewage treatment method combines a lift-pumping station, an above-grund Vortex sewage treatment plant, and a raised mound effluent absorpton system a mound soakaway bed. The company cites the following [paraphrased and adapted - Ed]
Webb, Tony, and Rodger B. Tomlinson. "Design procedures for effluent discharge to estuaries during ebb tide." Journal of environmental engineering 118, no. 3 (1992): 338-362.
Yin, Jie, Zhan-E. Yin, Xiao-meng Hu, Shi-yuan Xu, Jun Wang, Zhi-hua Li, Hai-dong Zhong, and Fu-bin Gan. "Multiple scenario analyses forecasting the confounding impacts of sea level rise and tides from storm induced coastal flooding in the city of Shanghai, China." Environmental Earth Sciences 63, no. 2 (2011): 407-414.
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Questions & answers or comments about flooded septic tanks and flooded drainfields or soakaway beds - what to do to restore the septic system to safe functional operation
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Hankey and Brown home inspectors, Eden Prairie, MN, technical review by Roger Hankey, prior chairman, Standards Committee, American Society of Home Inspectors - ASHI. 952 829-0044 - hankeyandbrown.com 11/06
Arlene Puentes, a licensed home inspector, educator, and building failures researcher in Kingston, NY. 11/29/06
Books & Articles on Building & Environmental Inspection, Testing, Diagnosis, & Repair
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: firstname.lastname@example.org. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones