Asphalt Shingle Laddering Wear & Failure Types
Types of asphalt shingle roof wear found on roofs installed using the shingle laddering method.
LADDERED SHINGLE FAILURES & WEAR - CONTENTS: identification of types of asphalt roof shingle wear or damage that can be mapped by the shingle laddering installation pattern. We explain the role of shingle laddering in diagnosing the cause and appearance of mineral granule loss, thermal splitting, and fishmouthing that are found on asphalt shingle roofs.
POST a QUESTION or READ FAQs about types of asphalt shingle roof damage caused by or explained by shingle installation in a ladder pattern up the roof slope.
InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
Asphalt shingle laddering wear & failure patterns: this article describes the wear, leak, or failure patterns seen on asphalt shingle roofs that were installed in a ladder-pattern. Some, but not all of these wear conditions can be ascribed to the ladder-pattern of installation. In other photos the ladder pattern-marked shingle wear tells us something else about why the roof is wearing early or unevenly.
This article series describes the installation of asphalt roof shingles in a ladder-approach rather than a multi-course staggered approach to nailing shingles and illustrates the effects of this method on roofs. Our page top photo shows asphalt roof shingles that were installed in the ladder pattern - made very apparent by the early wear and failure of some of areas of the roof - a wear condition that we explain in the text below.
Photo-Guide to Asphalt Shingle Laddering Wear & Failure Patterns
Shingle granule loss due to improper shingle storage or handling
At left is a closer view of the wearing shingles on the asphalt shingle roof shown at page top. The dark shingles in the photo center and lower right show granule loss - early wear or product failure whose cause we can guess.
[Click to enlarge any image]
This article series defines shingle laddering - an installation pattern, and it explains how to identify & evaluate shingles installed in this "ladder pattern". The information here describes the various sorts of roof leak, wear, and cosmetic issues caused by shingle laddering as
an example of something a bit less than the "best" roof installation workmanship. These shingle laddering defects occur on both organic-mat and fiberglass-mat
asphalt roof shingles.
Getting back to the asphalt shingle ladder pattern photo show just above, I've marked and numbered four roof areas on this slope of a roof pointed out by my daughter Michelle Friedman and found in Haddonfield, New Jersey. Here is some experienced, informed speculation about four conditions seen on this roof:
Asphalt shingles wearing well - and normally, showing little granule loss. These are the lighter colored shingles in most of the field of this roof. Take another look at the page top photo and you'll see these lighter, better-condition shingles appear in various areas of the roof surface, independent of their position on the roof, near the ridge, mid-roof, and near the roof eaves.
Asphalt shingles showing small specific area of granule loss from foot traffic - this looks to me a lot like foot traffic. Stand on this roof and turn your foot on a hot day and you'll rip off granules from the area below your feet. Someone may have been walking on the roof, or the wear could even have been caused during installation. Click to enlarge the photo and you'll see that the granule loss is on about 3 individual shingles and does not appear elsewhere in this pattern on this roof photo.
Damaged or defective asphalt roof shingles showing early granule loss - these darkest shingles have lost the most granules and are likely to wear out and leak before the rest of the roof covering, precipitating an "early" roof replacement, perhaps several years or more before the end of life of the rest of the roof covering and possibly before the end of the shingle warranty period.
Notice that these shingles appear physically together - they were picked up in a handful - or several handfuls, one for each area where they were nailed onto the roof. I suspect that all of these damaged shingles (I counted 64 of them) came from the same bundle or shingle bundle trio in a pallet of asphalt shingles that were stored outdoors, exposed to weather (in violation of the manufacturer's instructions), and I suspect that these shingle bundles were on the uppermost or weather-exposed top of the entire pallet of materials.
Exposure of uninstalled roof shingles to the weather by storing them outdoors can cause water to accumulate in the uppermost bundles of material where freeze-thaw cycles can soften and damage the product. There are other possible explanations but that's my guess and I'm sticking to it unless we can get a sample of the material for laboratory analysis that might offer an alternative explanation such as a manufacturing defect.
Worn asphalt shingles with moderate granule loss, more than item #1 above but less than #3 above. I speculate that these shingles were from the next layer down of shingle bundles on the pallet stored outdoors or that they were also exposed to weather but for less time or in less wearing conditions than their sisters in #3.
For shingles suffering early granule loss due to improper storage or handling, the failure has nothing to do with their installation in a laddering pattern. Rather, the ladder-installation pattern tells us useful information about the sequence of and selection of individual asphalt shingles as they were being nailed to the roof surface.
Shingle Cracking or Thermal Splitting at Roof Locations Determined by Shingle Installation Pattern
At left you can see long vertical lines of black roofing mastic or sealant that was applied to try to seal cracks or tears in these asphalt roof shingles observed by looking down from the Poughkeepsie NY railroad bridge.
There we explain that thermal splitting occurs in asphalt roof shingles made without adequate tear resistance, especially when combined with very effective self-sealing shingle tabs (intended to protect against wind-blow-off) and combined again with thermal movement that is more pronounced in areas subject to both freezing winters and hot summers.
Some inspectors opined that the crack pattern on this roof maps 8-foot lengths of roof plywood. Balderdash! You can see thermal splitting occurring in vertical patterns that range in width from one shingle to several individual shingle widths on the roof.
On the roof roof shown above the installation of shingles in a ladder pattern did not cause the thermal splitting problem, but it explains why the thermal splits occur in long vertical lines in the pattern seen in the photograph.
[Click to enlarge any image].
Shown for comparison, at left I include a photograph of thermal splitting occurring along a diagonal on a different roof. These shingles were installed in a standard half-tab offset staggered pattern up the roof rather than in a ladder pattern.
The result is that butt joints march on a diagonal up the roof, and so does thermal splitting in the tabs placed over those butt joints.
While thermal splitting can indeed run vertically up any asphalt shingle roof, why are these shingles splitting along these particular and parallel and long vertical lines? Probably because the ladder pattern creates a vertical line of shingle butt joints that run straight up the roof on alternating shingle courses.
As the self sealing tabs of a single course of shingles glue that tab across the butt joint of a pair of shingles in the course below, that sealed tab is just where the split is most-likely to occur when temperatures cause shrinking or cooling of the entire roof surface. The shingles separated by a butt joint move apart, but the tab glued atop them tears.
Shingle Fishmouthing Occurring in Patterns Mapped to Shingle Ladder Pattern Installation
At below left you can see shingle fishmouthing, a characteristic upwards curved "mouth" occurring roughly in parallel vertical runs up the roof. Click to enlarge the image and you'll see even more interesting evidence. Alternating courses of shingles are producing a fishmouth that is almost exactly 1/2 shingle tab offset from the fishmouthing occurring in shingle courses just above and below.
This pattern of occurrence of fishmouthing is almost certainly mapping the butt joints (below each raised fish mouth) of shingles installed in a shingle ladder installation pattern - shingles installed lapped 1/2 tab to the left, then right, as the roofer worked straight up the roof slope.
Just to illustrate and prove the shingle laddering-fishmouth claim for the roof at above left, in my photo at above right we illustrate fishmouthing occurring on long diagonals on another 3-tab asphalt shingle roof. These shingles were nailed in the more conventional roof shingle nailing pattern in which shingle courses were offset by 1/2 tab working to the roofer's left or right for six shingle courses at a time.
This increased staggering shows up as follows: choose any fishmouth on the roof and count up-slope until you find another one directly above it. You'll get to six - the number of shingle courses that were nailed in a staggered offset before any shingle butt joint appears over a shingle course below.
Why six? Each of these shingles is comprised of 3 individual tabs separated by slots. The roofer offsets each successive shingle course 1/2 of a tab (about 6 inches) to the left (or right if she is working to her right) as courses are nailed onto the roof. Do the math - you'll see that offsetting 1/2 a tab at each course will run 6 courses before the pattern repeats.
Shingle laddering does not cause shingle fishmouthing (some mistakenly call this CUPPING ASPHALT SHINGLES, it's not). But it does help confirm an explanation of why shingle fishmouthing occurs by mapping the location of fishmouths in the roof to the location of shingle butt joints.
Fishmouthing is most likely caused by a greater concentration of moisture entering the under-side of an asphalt shingle from below, perhaps from a damp attic or one with excessive moisture condensation. Where shingle butt joints occur the tab overlying the butt joint will receive more moisture (up through the butt joint gap) than neighboring shingle tabs that are not placed over a shingle butt joint.
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Ask a Question or Search InspectApedia
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
 Dave Flickinger, "Offset Patterns for Asphalt Shingles", Professional Roofing, National Roofing Contractor's Association (NRCA), May 2000. Professional Roofing Magazine, 10255 W. Higgins Rd., Suite 600, Rosemont IL 60018, Tel: 847-299-1183.
Carl Gerosa, Target Inspection Consultants, Inc., New Rochelle, NY 10804, Tel: 914-833-2900 / 914-834-7494, New York Home Inspectors License Number: NY 1600005625/CT 20 is a certified ASHI inspector and a member of CAHI, the Connecticut Association of Home Inspectors. Mr. Gerosa provides home inspections of Single Family Homes, Radon Testing, Wood Destroying Organisms. Email: firstname.lastname@example.org
Hankey and Brown home inspectors, Eden Prairie, MN, technical review by Roger Hankey, prior chairman, Standards Committee, American Society of Home Inspectors - ASHI. 952 829-0044 - hankeyandbrown.com
Arlene Puentes, a licensed home inspector, educator, and building failures researcher in Kingston, NY
Thanks to James A. Skees, PE, President and Sr. Forensic Engineer, OnTheRock Engineering, LLC, 604 W. Jefferson Street, LaGrange, KY 40031
502-225-6203 FAX 225-6204, for commenting on the roof cellophane strip problem, on wind damage to roof shingles, shingle blow off, improper shingle nailing, and roof shingle laddering underlying defects, August 2010. Mr. Skees is a forensic engineer who works for insurance companies. Mr. Skees can also be reached by email at email@example.com
The company has published online a sample Tornado Report
"Residential Wind Damage Evaluation", Wind Damage Sample, found at http://www.ontherockeng.com/Sample%20Tornado%20Report.pdf
Home Inspection Education Home Study Courses - ASHI@Home Training 10-course program. Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Home Reference Book, a reference & inspection report product for building owners & inspectors. Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Home Reference eBook, an electronic version for PCs, the iPad, iPhone, & Android smart phones. Special Offer: For a 5% discount on any number of copies of the Home Reference eBook purchased as a single order. Enter inspectaehrb in the order payment page "Promo/Redemption" space.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones
Wikipedia provided background information about some topics discussed at this website provided this citation is also found in the same article along with a " retrieved on" date. NOTE: because Wikipedia entries are fluid and can be amended in real time, we cite the retrieval date of Wikipedia citations and we do not assert that the information found there is necessarily authoritative.
Books & Articles on Building & Environmental Inspection, Testing, Diagnosis, & Repair
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume. Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Or choose the The Home Reference eBook for PCs, Macs, Kindle, iPad, iPhone, or Android Smart Phones. Special Offer: For a 5% discount on any number of copies of the Home Reference eBook purchased as a single order. Enter INSPECTAEHRB in the order payment page "Promo/Redemption" space.
Green Roof Plants: A Resource and Planting Guide, Edmund C. Snodgrass, Lucie L. Snodgrass, Timber Press, Incorporated, 2006, ISBN-10: 0881927872, ISBN-13: 978-0881927870. The text covers moisture needs, heat tolerance, hardiness, bloom color, foliage characteristics, and height of 350 species and cultivars.
Green Roof Construction and Maintenance, Kelley Luckett, McGraw-Hill Professional, 2009, ISBN-10: 007160880X, ISBN-13: 978-0071608800, quoting: Key questions to ask at each stage of the green building process Tested tips and techniques for successful structural design
Construction methods for new and existing buildings
Information on insulation, drainage, detailing, irrigation, and plant selection
Details on optimal soil formulation
Illustrations featuring various stages of construction
Best practices for green roof maintenance
A survey of environmental benefits, including evapo-transpiration, storm-water management, habitat restoration, and improvement of air quality
Tips on the LEED design and certification process
Considerations for assessing return on investment
Color photographs of successfully installed green roofs
Useful checklists, tables, and charts