Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
ENVIRONMENTAL HAZARDS - INSPECT, TEST, REMEDY
ACOUSTICAL SEALANT CHOICES
AGE of a BUILDING - how to determine
AIR BYPASS LEAKS
AIR LEAK DETECTION TOOLS
AIR LEAK MINIMIZATION
AIR LEAK SEALING PROCEDURE
AIR POLLUTANTS, COMMON INDOOR
ALLERGENS in BUILDINGS, RECOGNIZING
ANIMAL ALLERGENS / PET DANDER
APPLIANCE EFFICIENCY RATINGS
ARCHITECTURE & BUILDING COMPONENT ID
ASBESTOS CEILING TILES, Asbestos-Containing
ASBESTOS CEMENT ROOFING
ASBESTOS ROOFING / SIDING POWER WASHING
ASBESTOS ROOFING / SIDING DUST
ASBESTOS CEMENT SIDING
ASBESTOS DUCTS, HVAC
ASBESTOS-FREE INSULATION MATERIALS
ASBESTOS IDENTIFICATION IN buildings
ASBESTOS FLOORING HAZARD REDUCTION
ASBESTOS FLOOR TILE IDENTIFICATION
ASBESTOS FLOORING REMOVAL GUIDE
ASBESTOS LIST of PRODUCTS
ASBESTOS MATERIAL REGULATIONS
ASBESTOS MATERIAL REGULATIONS Update
ASBESTOS MATERIAL REGULATIONS, OSHA
ASBESTOS PHOTO GUIDE to Materials
ASBESTOS REMOVAL, Amateur, Incomplete
ASBESTOS REMOVAL CERTIFICATIONS
ASBESTOS REMOVAL, Wetting Guidelines
ASBESTOS RISK ASSESSMENT
ASBESTOS TESTING LAB LIST
ASBESTOS UNDER the MICROSCOPE
ROOF ICE DAM LEAKS
BASEMENT HEAT LOSS
BUCKLED FOUNDATIONS due to INSULATION?
BUILDING NOISE DIAGNOSIS & CURE
CATHEDRAL CEILING INSULATION
CEILING FINISHES INTERIOR
CEILINGS, DROP or SUSPENDED PANEL
CEILINGS & WALLS, PLASTER TYPES
CERAMIC TILE FLOOR, WALL
CERAMIC TILE, ASBESTOS in?
CHIMNEY INSPECTION DIAGNOSIS & REPAIR
CHINESE DRYWALL HAZARDS
DEW POINT CALCULATION for WALLS
EFFLORESCENCE, Salts & White / Brown Deposits
FIBERGLASS INSULATION MOLD
FLOOR TILE HISTORY & INGREDIENTS
FLOOR TILES ASBESTOS
FLOOR TYPES & DEFECTS
HEAT LOSS in BUILDINGS
HOUSE DOCTOR, how-to be
HUMIDITY LEVEL TARGET
ROOF ICE DAM LEAKS
INDOOR AIR QUALITY IMPROVEMENT GUIDE
INSULATION FACT SHEET- DOE
INSULATION IDENTIFICATION GUIDE
INSULATION R-Values & Properties
METAL LATH, PLASTER & STUCCO
METHANE GAS SOURCES
MOISTURE CONTROL in BUILDINGS
MOLD: A COMPLETE GUIDE TO MOLD
Museum Artifact Preservation
NOISE / SOUND DIAGNOSIS & CURE
ODORS GASES SMELLS, DIAGNOSIS & CURE
PAINT FALURE, DIAGNOSIS, CURE, PREVENTION
PLASTER & BEAVERBOARD & DRYWALL
PLASTER BULGES & PILLOWS
PLASTER LATH, METAL
PLASTER, LOOSE FALL HAZARDS
PLASTER TYPE IDENTIFICATION
PLASTER VENEER Best Practices
ROOF VENTILATION SPECIFICATIONS
ROOFING INSPECTION & REPAIR
SAFETY HAZARDS & INSPECTIONS
SEARS KIT HOUSES
SOUND CONTROL in buildings
SPLITS & CRACKS in STRUCTURAL WOOD BEAMS
STAIN DIAGNOSIS on BUILDING EXTERIORS
STAIN DIAGNOSIS on BUILDING INTERIORS
STUCCO WALL METHODS & INSTALLATION
STRUCTURAL DAMAGE PROBING
SWEATING (CONDENSATION) on PIPES, TANKS
Thermal Expansion Cracking of Brick
THERMAL EXPANSION of MATERIALS
THERMAL IMAGING, THERMOGRAPHY
THERMAL MASS in BUILDINGS
THERMAL TRACKING Indicates Heat Loss
VAPOR BARRIERS & CONDENSATION in BUILDINGS
VENTILATION in BUILDINGS
VINYL CHLORIDE HEALTH INFO
VOCs VOLATILE ORGANIC COMPOUNDS
WALL CONSTRUCTION BARRIER vs CAVITY
WATER ENTRY in buildings
WINDOWS & DOORS
WINTERIZE A BUILDING
WOOD Burning Heaters Fireplaces Stoves
WORLD TRADE CENTER 9-11 DUST PHOTOS
Asbestos cement roof damaged by washing: this article warns about un-supervised or un-trained environmental cleanup companies or work crews handling asbestos, lead, mold, and similar indoor contaminants, including identification of amateur or improper asbestos "abatement" projects that failed to properly remove materials or that left abandoned asbestos materials in place. These warnings about using a power washer on an asbestos-cement roof also pertain to asbestos cement siding as well.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Question: Is power-washed asbestos-cement roof runoff an environmental hazard?
I live in Brantford Ontario and a building in my neighbourhood has was I think is a corrugated asbestos roof. Last weekend some workmen power washed it. The run off, when dried, looked like grey powder and lifted from the pavement in "sheets" almost like parchment paper. I've attached a couple of photos. Does this present any danger or give cause for health concerns? - D.F., Brantford ONT
Reply: Asbestos hazards are probably present, asbestos regulation violations may have occurred, and further steps are needed
Most likely the debris that was washed off of the roof contains road and other environmental dust that had settled on the roof surface over time, and possibly algae, mold, or lichens that were staining the surface (as in our file photo of corrugated asbestos roofing - left) leading to the desire to wash the roof in the first place. But because power washing is a strong approach to cleaning a surface it is likely to also have dislodged asbestos and cement particles from the asbestos-cement corrugated roof itself.
While wetting the material, something that would naturally occur during the power-washing of the cement-asbestos roof surface, would be expected to reduce the airborne level of asbestos during the actual washing process, although when properly peformed, wetting to control asbestos particle release includes the addition of a wetting agent to the spray before it is applied.
Power-washing a cement asbestos roof would leave substantial materials on the ground after the clening procedure. As the on-ground material dries asbestos fiber and particle risks are likely to be present.
So it would be no surprise if the debris on the ground around the building in your photos contains a high level of asbestos fibers and particles. The material therefore may form an airborne asbestos hazard in the neighborhood, or as it washes into local storm drains, it may constitute an illegal and improper disposal of asbestos dust and debris.
If the added cost to properly clean up this mess is going to be high (which we would guess is the case), it would be appropriate and inexpensive to collect a debris sample for testing by a local, certified asbestos testing lab to confirm that the contents are indeed contaminated at a level requiring professional cleaning.
In addition, power-washing the roof surface risks increasing the friable nature of the material that remains on the building, as the cementious binding has been removed from the uppermost roof surface, first by normal weathering and second, and much more aggressively, by the power washing process.
The building owners should address these questions immediately in order to reduce the spread and thus possible costs of a proper asbestos dust cleanup.
Asbestos regulations for Ontario are published under the Occupational Health and Safety Act and are in Ontario Regulation 278/05 and provide a clearly-written and comprehensive guide to cleaning up and disposing of asbestos containing materials in or on buildings. Discussing [Type 1] asbestos operations that regulation states:
Watch out: in 2010 The New York Times reported that
Details are at ASBESTOS REMOVAL CERTIFICATIONS.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.