Water Softener Installation Procedures
How to hook up plumbing, wiring, drains for a water conditioner
INSTALLATION of WATER SOFTENERS - CONTENTS: How Water Softeners Are Hooked Up to Building Plumbing Pipes & Electrical Wiring. How to Connect Water Softener Water Piping Input & Output Water Lines & how to route & connect water conditioner regeneration cycle drain, salt tank, controls.
POST a QUESTION or READ FAQs about how water softeners are installed: location, plumbing, wiring connections, drain connections & where to obtain installation & operation manuals
InspectAPedia tolerates no conflicts of interest. We have no relationship with advertisers, products, or services discussed at this website.
How to install or "hook up" a water softener:
How to connect a water softener to building water piping, drain piping, & electrical power; where to locate the water softener. This article explains how to hook up a water softener or water conditioner.
We describe the piping connections for water in and out of the water softener, water softener bypass valves for maintenance, and water softener drain hookups.
This article series explains how water softeners and similar water conditioners work, types of water softeners, and the basics of what water softener controls are present and what they do, how water softeners should be installed, maintained, cleaned, and adjusted.
How Water Softeners or Water Conditioners are Hooked Up to Building Plumbing
It is conceptually simple to install and connect-up a water conditioner or water softener.
You need to find physical space where the resin or treatment tank and controls will fit, and where the salt or brine tank will fit. Usually these two pieces are separate (except in some older manually operated water softeners), but they are installed side-by-side.
Our photo of a water conditioner installation at left shows a Kinetico Mach Series water conditioner system installed in a Dutchess County New York home.
Where space is really tight, we sometimes see the larger brine tank installed somewhere else not right next to the water softener, but of course connected to it by its flexible plastic tubing.
Guide to Connecting A Water Softener Water Piping or Input and Output Water Lines
Since it's usually preferable to treat all of the building water supply with a water conditioner (this helps protect pipes from mineral-clogging by hard water), the water conditioner is usually placed as close as possible to where water enters the building.
Most installers place the water softener near other water equipment in the building such as close to an indoor pump and water pressure tank, or where municipal water is supplied, close to where the water supply enters the building.
[Click to enlarge any image or table]
The water softener hookup layout sketch shown at left is from a 1989 Culligan System 19 or 23 Water Conditioner installation manual. Be sure to consult the specific manual for your own water softener brand and model for correct hookup details for your own equipment.
The water softener is piped "in line" on the main cold water pipe entering the structure so that incoming water is treated before passing on to the building water heater, and to hot and cold water distribution piping.
If other water treatment or water sterilizing or potability system is installed (such as a chlorinator or UV light), that equipment is best placed ahead of or before the water softener to help avoid the chances of unwanted bacterial growth in the water conditioner.
If a water filter is installed, we like that to also be ahead of all other water treatment in the building to help avoid debris clogging that interferes with proper operation of other water treatment equipment. For example, dirt or silt in a water supply can quickly coat the bulb in a UV light bacterial treatment device on a private water supply system.
Incoming water is connected to the "input" side of the water softener/water conditioner, and the conditioner's output side is connected to the building water supply piping feeding the building's plumbing fixtures.
For watering gardens and lawns the installer may provide a direct connection to that building water piping taken off before the water softener so that we don't waste water softener salt treating water being used to wash a car or water the lawn.
How & Where to Connect the Water Softener Drain Line
Periodically, depending on the water hardness and the amount of water used, the water softener or water conditioner needs to clean itself of minerals accumulated as they were removed from the water supply, and to recharge the salt used in the softener's resin chamber where water is treated.
[Click to enlarge any image or table]
On an automatic water softener the regeneration and cleaning cycle for the water softener is controlled by a simple timer or clock, or on more sophisticated systems a computer chip may monitor the amount of water used and even the hardness of water leaving the system, deciding based on that data when a backwash-regeneration cycle is needed.
Shown at left is a chart indicating the water softener drain line length limitations in feet based on an installation in which the brine tank and water softener are installed together on the same building level. This specific chart is from a Culligan System 19/23 Water Conditioner installation manual. Be sure to check your own equipment's installation manual.
When the water softener goes through a regeneration cycle it will bypass the building water supply, often automatically, so that water stops passing through the equipment's treatment system pump water into the separate brine tank (salt tank) where it dissolves salt pump new salty water backwards through the resin tank or treatment tank where the process removes other minerals from the treatment tank, sending this product out through a (usually plastic) drain tube to a building drain.
Other water conditioner manufacturers such as Autotrol specify other drain line connection details
The ideal water conditioner location is above (higher than) and not more than 20 feet from the drain. Use 1/2-inch plastic tubing between the water conditioner drain hookup on the equipment and the drain. The ideal location for a water conditioner (or softener) is also in an area protected from freezing, protected from mechanical damage (don't run into it when pulling a car into the garage), and at a location convenient for connection to building water supply piping and electrical hookups. Usually we locate the water conditioner as close as possible to the point of water entry into the building so that we protect as much of the building plumbing system as possible from mineral clogging.
Increase the water softener drain line diameter from 1/2-inch to 3/4-inch diameter for runs of more than 20 feet in length and less than 40 feet.
For elevated water conditioner drain lines, provided that incoming water pressure is at least 40 psi, you can elevate the drain up to six feet as long as the total drain line length is less than fifteen feet. You can elevate the water conditioner drain line another two feet for every 10 psi increase in water pressure. For example if your water pressure is always 50 psi or higher, the drain line for the water softener can be eight feet above the unit.
Watch out: Use a Siphon Trap: for elevated water conditioner drain lines emptying into a drain below the level of the control valve (that's where the drain line connects to the water softener), make a 7-inch loop in the plastic drain line such that the bottom of the drain line loop is level with the drain line connection point (at the water softener). The loop should provide an adequate anti-siphon trap. Without this detail, after a water softener regen cycle when the drain line is filled, the drain can continue to siphon-drain water out of the water softener.
Warnings: Avoid These Water Conditioner Drain Connection Mistakes
Connect your water conditioner drain line to a building drain or to a separate graywater drain feeding drywell, but do not simply spill water conditioner drainage onto the ground surface such as is shown in our photo shown above - a water softener drain hose simply spurts out through the building exterior wall and onto the ground surface.
Doing so violates plumbing and sanitary code in most jurisdictions (and invites basement or crawl space leakage too).
Watch out: be sure that the water softener drain connection is made following the manufacturer's instructions [usually including an air-gap rather than an air-tight/water-tight connection at the drain standpipe] so that you avoid a possibly unsanitary CROSS CONNECTIONS, PLUMBING.
Our photo of a cross connection (left) shows a water conditioner drain line (using a garden hose) connected to a sewer pipe - inviting sewage and bacteria to enter the building's water supply.
Also, where the softener is emptying its drain product into an onsite private septic system and drainfield, the salts in the wastewater may shorten the drainfield life, so take a look at REDUCE IMPACT of SOFTENER on SEPTIC.
Watch out also for crimped water softener drain line tubing. If you are using soft flexible tubing to connect your water conditioner to a drain line it's easy to crimp the line at a sharp bend or where it is stapled to a building support.
A crimped water conditioner drain will interfere with proper backwash/regeneration cycling of your equipment.
Watch out: Use an air gap: for elevated water conditioner drain lines that empty into an overhead sewer pipe or waste pipe you should use a sink-type trap for the connection (that is provide an air gap to avoid back-contamination of the equipment).
Watch out: Never connect the water softener drain line directly to a sewer drain (that is by an air-tight connection such as shown at left).
Doing so invites sewage and bacterial back-contamination into the building water supply system, especially if a sewer line backup occurs. See CROSS CONNECTIONS, PLUMBING.
Setting up the Water Softener & Setting Its Controls
You'll need to set the water conditioner's clock to the proper time (and day on some models) and you may need to set the water softener controls that determine the frequency of regeneration and the salt dose. See SOFTENER ADJUSTMENT & CONTROLS.
Steps in Starting Up A New or Newly-Installed Water Softener
The following advice is adapted from water softener installation manuals from Culligan and other water conditioner manufacturers.
For new water conditioners: The water conditioner start-up procedure here is appropriate when you are installing a new water conditioner system or a new water conditioner media tank.
Watch out: as Culligan's manuals point out about new water conditioners,
A sanitizing agent has been added to the conditioner tank [the media tank or resin tank] at the factory. This sanitizing agent must be flushed out before the unit is placed into service, by initiating a recharge cycle using the steps outlined below.
Plug in the power cord: Check that the water conditioner timer or control is in the "service" position, then plug in the water conditioner's power cord to an electrical outlet.
You should use a grounded outlet that will accept a grounded electrical cord plug (a three-prong plug). If necessary you can use a three-prong to two-prong adapter to connect to a two-prong electrical receptacle, but be sure that that receptacle is itself grounded. In general, a three-prong to two-prong electrical outlet adapter includes a green metal tab with a hole in it that is used to make a proper connection to the electrical grounding system.
The screw in the center of the cover plate for the electrical receptacle is removed and reinserted through the green tab so that the adapter is secured in place and a ground connection is made. We recommend that you ask your electrician to install a grounded, three-prong electrical receptacle in that location as soon as convenient.
Set the water conditioner controls: set the timer to the correct time of day, time of recharge, recharge frequency, and set the "salt dose" or refill regulator to the proper number. See SOFTENER ADJUSTMENT & CONTROLS for details.
Open the bypass valve: with the controls set for normal service, slowly open the water inlet valve or slowly open the bypass valve if it was in the closed or "bypass" position. On a Culligan water softener this means push slowly on the blue knob on the bypass valve to put the unit into service.
Allow water to fill the resin tank.
Perform a water softener regeneration cycle. On a typical Culligan model this may mean rotating the cam that carries the "salt dosage" dial 1/3 turn, or pushing a red "regen" button on the water conditioner timer.
Note: more detailed instructions in your water conditioner installation or user's manual may explain the need to move the salt dosage cam to start a regen cycle or to return the cam to a normal between-cycle position.
Drain and refill the hot water tank? If hard, untreated water entered the building's hot water tank while the water softener was on bypass or turned off, then you should drain and refill the hot water tank.
Be sure that the water heater is turned off before and during drainage and refill.
List of Free Water Softener & Water Conditioner Installation Manuals
Watch out: because water softener and other water conditioner equipment models vary in features and functions, they also vary in their exact installation requirements. You should have or obtain the installation, operation, and maintenance manual for your own brand and model of water softener.
Most water softener owners manuals include detailed installation instructions and also a table of recommended settings. If you don't have an owner's manual call the manufacturer's tech service and give them the model number and ask for a manual as well as their setting advice.
"Commercial Water Softener Installation and Operating Instructions", IBC Filtration & Water Treatment Products (Australia) for commercial, industrial and residential application www.ibcwater.com.au (07) 3219 2233
Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Where to obtain WTF 480 or WTF 15ANX water softener manuals
Do you have any manuals on WTF 480 or WTF 15ANX water softeners? - Laura Tapp 6/12/11
Laura, the WTF series are produced and distributed by Water Tender, 6201 South Hanover Rd., Elkridge MD 21075-5651, Tel: 410-796-7700; also Water Tender, 23204 Airpark Dr., Petersburg VA 23803, Tel: 804-732-7000. You can contact them for installation and service manuals.
Also if you scroll down to the references at the bottom of this article, at "Water Tender" you'll see a link to free online information describing various Water Tender equipment models.
Question: Autotrol 255 valve/ 400 series control water conditioner - water keeps flowing out of the hose
I have a Autotrol 255 valve/ 400 series control water conditioner, water flows out of hose non stop. We have tried regeneration several time but this doesn't shut off water. - Deloras 2/8/12
Questions & answers or comments about problems with the operation of aerobic septic systems
Use the "Click to Show or Hide FAQs" link just above to see recently-posted questions, comments, replies, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
 "Commercial Water Softener Installation and Operating Instructions", IBC Filtration & Water Treatment Products (Australia) for commercial, industrial and residential application www.ibcwater.com.au (07) 3219 2233
 Culligan Mark 10 Automatic Water Conditioner (Water Softener Models from 1995) Installation and Operating Instructions (covering models manufactured after 1995) (1-96) 01881948.pdf available from www.culligan.com (covering models manufactured after 1995)
 Culligan Mark 100 Water Softener Owner's Guide, 1994-1998, 8/96, web search 01/31/2011, original source Culligan International Co., http://www.culligan.com/uploadedFiles/Service_and_Maintenance
 "Non electric water softener,
Installation and Operating Instructions", IBC Filtration & Water Treatment Products (Australia), op.cit.
 North Dakota Standards for Water Softeners, North Dakota General Authority Law, Chapter 62-04-08, Water Softener Units http://www.legis.nd.gov/information/acdata/pdf/62-04-08.pdf. "The objective of this chapter is to provide a standard of quality, capacity,
and performance for water softener units. Water softener performance
is to be based upon referee tests procedures described in section
 Water Hardness Table used in this article series originated with but was edited and added to from http://www.bestfish.com/tips/110598.html and also from http://www.water-research.net/hardness.htm
 "Water Softener Twin Tank Installation and Operating Instructions", IBC Filtration & Water Treatment Products (Australia), op.cit.
 Water Softeners, CMHC, Canadian Mortgage and Housing Corporation, cmhc-schl.gc.ca/en/co/maho/wawa/wawa_005.cfm - October 2008. Canada Mortgage and Housing Corporation acknowledges the contribution of Health Canada to the development of this document. For further questions regarding water treatment and water quality, contact Health Canada at email@example.com or call 613-957-2991 or 1-866-225-0709.
 Water Softener with Microprocessor: Installation & Operating Instructions, IBC Filtration & Water Treatment Products (Australia), IBC Water, Ltd., 18 Dividend Street, Mansfield Qld 4122, Postal Address:
PO Box 2247, Mansfield BC, Qld 4122 Australia, Tel: Sales/Service: 1-300-166-253; Tel: (07) 3347 1600 Int. +61 7 3347 1600, Facsimile: (07) 3219 2266 Int. +61 7 3219 2266,
Email: firstname.lastname@example.org , web search 01/31/2011, original source: http://www.ibcwater.com.au/zone_files/PDF/as0922mp-cl.pdf
Onsite Wastewater Disposal, R. J. Perkins;
Quoting from Amazon: This practical book, co-published with the National Environmental Health Association,
describes the step-by-step procedures needed to avoid common pitfalls in septic system technology.
Valuable in matching the septic system to the site-specific conditions, this useful book will help you install a reliable system in
both suitable and difficult environments. Septic tank installers, planners, state and local regulators, civil and sanitary engineers,
consulting engineers, architects, homeowners, academics, and land developers will find this publication valuable.
Septic Tank/Soil-Absorption Systems: How to Operate & Maintain [ copy on file as /septic/Septic_Operation_USDA.pdf ] - , Equipment Tips, U.S. Department of Agriculture, 8271 1302, 7100 Engineering, 2300 Recreation, September 1982, web search 08/28/2010, original source: http://www.fs.fed.us/t-d/pubs/pdfimage/82711302.pdf
Septic System Owner's Manual, Lloyd Kahn, Blair Allen, Julie Jones, Shelter Publications, 2000 $14.95 U.S. - easy to understand, well illustrated, one of the best practical references around on septic design basics including some advanced systems; a little short on safety and maintenance. Both new and used (low priced copies are available, and we think the authors are working on an updated edition--DF.
Quoting from one of several Amazon reviews: The basics of septic systems, from underground systems and failures to what the owner can do to promote and maintain a healthy system, is revealed in an excellent guide essential for any who reside on a septic system. Rural residents receive a primer on not only the basics; but how to conduct period inspections and what to do when things go wrong. History also figures into the fine coverage.
Grass is Always Greener Over the Septic Tank, Bombeck, Erma: $ 5.99; FAWCETT; MM;
This septic system classic whose title helps avoid intimidating readers new to septic systems, is available new or used at very low prices.
It's more entertainment than a serious "how to" book on septic systems design, maintenance, or repair. Not recommended -- DF.
US EPA Onsite Wastewater Treatment Systems Manual Top Reference: US EPA's Design Manual for Onsite Wastewater Treatment and Disposal, 1980, available from the US EPA, the US GPO Superintendent of Documents (Pueblo CO), and from the National Small Flows Clearinghouse. Original source http://www.epa.gov/ORD/NRMRL/Pubs/625R00008/625R00008.htm
Water Wells and Septic Systems Handbook, R. Dodge Woodson. This book is in the upper price range, but is worth the cost for serious septic installers and designers.
Quoting Amazon: Each year, thousands upon thousands of Americans install water wells and septic systems on their properties. But with a maze of codes governing their use along with a host of design requirements that ensure their functionality where can someone turn for comprehensive, one-stop guidance? Enter the Water Wells and Septic Systems Handbook from McGraw-Hill.
Written in language any property owner can understand yet detailed enough for professionals and technical students this easy-to-use volume delivers the latest techniques and code requirements for designing, building, rehabilitating, and maintaining private water wells and septic systems. Bolstered by a wealth of informative charts, tables, and illustrations, this book delivers:
* Current construction, maintenance, and repair methods
* New International Private Sewage Disposal Code
* Up-to-date standards from the American Water Works Association
Wells and Septic Systems, Alth, Max and Charlet, Rev. by S. Blackwell Duncan, $ 18.95; Tab Books 1992. We have found this text very useful for conventional well and septic systems design and maintenance --DF.
Quoting an Amazon description:Here's all the information you need to build a well or septic system yourself - and save a lot of time, money, and frustration. S. Blackwell Duncan has thoroughly revised and updated this second edition of Wells and Septic Systems to conform to current codes and requirements. He also has expanded this national bestseller to include new material on well and septic installation, water storage and distribution, water treatment, ecological considerations, and septic systems for problem building sites.
Carson, Dunlop & Associates Ltd., 120 Carlton Street Suite 407, Toronto ON M5A 4K2. Tel: (416) 964-9415 1-800-268-7070 Email: email@example.com. The firm provides professional home inspection services & home inspection education & publications. Alan Carson is a past president of ASHI, the American Society of Home Inspectors. Thanks to Alan Carson and Bob Dunlop, for permission for InspectAPedia to use text excerpts from The Home Reference Book & illustrations from The Illustrated Home. Carson Dunlop Associates' provides extensive home inspection education and report writing material.
The Illustrated Home illustrates construction details and building components, a reference for owners & inspectors. Special Offer: For a 5% discount on any number of copies of the Illustrated Home purchased as a single order Enter INSPECTAILL in the order payment page "Promo/Redemption" space.
TECHNICAL REFERENCE GUIDE to manufacturer's model and serial number information for heating and cooling equipment, useful for determining the age of heating boilers, furnaces, water heaters is provided by Carson Dunlop, Associates, Toronto - Carson Dunlop Weldon & Associates Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on any number of copies of the Technical Reference Guide purchased as a single order. Just enter INSPECTATRG in the order payment page "Promo/Redemption" space.
The Home Reference Book - the Encyclopedia of Homes, Carson Dunlop & Associates, Toronto, Ontario, 25th Ed., 2012, is a bound volume of more than 450 illustrated pages that assist home inspectors and home owners in the inspection and detection of problems on buildings. The text is intended as a reference guide to help building owners operate and maintain their home effectively. Field inspection worksheets are included at the back of the volume.
Special Offer: For a 10% discount on any number of copies of the Home Reference Book purchased as a single order. Enter INSPECTAHRB in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
Special Offer: Carson Dunlop Associates offers InspectAPedia readers in the U.S.A. a 5% discount on these courses: Enter INSPECTAHITP in the order payment page "Promo/Redemption" space. InspectAPedia.com editor Daniel Friedman is a contributing author.
The Horizon Software System manages business operations,scheduling, & inspection report writing using Carson Dunlop's knowledge base & color images. The Horizon system runs on always-available cloud-based software for office computers, laptops, tablets, iPad, Android, & other smartphones
Support InspectApedia.com & See Fewer Advertisements
From Google's Contributor website: Contribute a few dollars each month. See fewer ads. The money you contribute helps fund the sites you visit.