Question? Just ask us!
Free Encyclopedia of Building & Environmental Inspection, Testing, Diagnosis, Repair
InspectAPedia ® Home
AGE of WATER HEATERS
AIRBOUND HEAT SYSTEM REPAIR by WATER FEED VALVE
ALTERNATIVE HOT WATER SOURCES
ANODES & DIP TUBES on WATER HEATERS
ANTIFREEZE for BOILERS
ANTI SCALD VALVES
APPLIANCE DIAGNOSIS & REPAIR
APPLIANCE EFFICIENCY RATINGS
AQUASTAT CONTROL Functions
BACKDRAFTING HEATING EQUIPMENT
BACKFLOW PREVENTER, HEATER WATER FEEDER
CARBON MONOXIDE - CO
CHECK VALVES, WATER SUPPLY
CHEMICAL CONTAMINANTS in WATER
CHIMNEY INSPECTION DIAGNOSIS REPAIR
CLOGGED SUPPLY PIPING
DEBRIS in WATER SUPPLY, Water Heater
DRAIN a WATER HEATER TANK
ELECTRIC WATER HEATERS
FLOODED HEATING EQUIPMENT REPAIR
FLOODED WATER HEATER REPAIR
GALVANIC SCALE & METAL CORROSION
GAS BURNER Flame & Noise Defects
GAS FIRED WATER HEATERS
GAS PIPING, VALVES, CONTROLS
HOT WATER SUPPLY
INDIRECT FIRED WATER HEATERS
MANUALS & PARTS GUIDES - HVAC
MIXING / ANTI-SCALD VALVES
NO HEAT - NO HOT WATER: HEATER DIAGNOSIS
NOISE / SOUND DIAGNOSIS & CURE
NOISE CONTROL for HEATING SYSTEMS
NOISE, PLUMBING CHECKLIST
NOISE, WATER HEATER
ODORS GASES SMELLS, DIAGNOSIS & CURE
ODORS IN WATER
PIPING IN buildings, Clogs Leaks Types
PLASTIC Plexvent / Ultravent RECALL
PLUMBING FIXTURES, KITCHEN, BATH
RELIEF VALVE LEAKS
RELIEF VALVES - Water Heaters
SCALE REMOVAL, WATER HEATERS
SEWER GAS ODORS
SOLAR HOT WATER HEATERS
SOOT on OIL FIRED HEATING EQUIPMENT
SPILL SWITCHES - Flue Gas Detection
TANKLESS WATER HEATERS
Temperature Pressure Relief Valves - Water Heaters
THERMOSTATS, WATER HEATER
TIMERS for ELECTRIC WATER HEATERS
WATER CONSERVATION MEASURES
WATER CONTAMINANT LEVELS
WATER HAMMER NOISE DIAGNOSE & CURE
WATER ODORS, CAUSE CURE
WATER PIPES, Clogs Leaks Types
WATER PRESSURE & FLOW MEASUREMENT
WATER PRESSURE LOSS DIAGNOSIS & REPAIR
WATER QUANTITY IMPROVEMENT
WATER SOFTENERS & CONDITIONERS
WINTERIZE A BUILDING
This article describes in complete detail the steps in the procedure to remove scale or lime from a hot water heater tank - hot water heater de-scaling or de-liming procedural steps.
Green links show where you are. © Copyright 2014 InspectApedia.com, All Rights Reserved.
Lime or scale in plumbing systems is caused by hard water as well as silicates, sulfates, and similar materials form water scale that coats the bottom of a hot water tank or the surface of the electrodes in an electric water heater, interfering with proper water heater operation, causing water heater noises, reduction in hot water quantity, increased water heater operating costs, and a shorter water heater life.
Silt and soil debris can also collect in a water heater tank where it can cause similar problems even if the water supply is not hard.
Silt and debris can be easily removed from a hot water tank by periodic flushing. In fact if your water heater is quite noisy, it will probably be easier to remove un-wanted mineral deposits from the water tank than it will be later if you wait until the heater is no longer making much noise (because the mineral layer has solidified).
Install a sediment filter on the incoming water supply to avoid this problem in the first place.
But lime or water scale are more difficult to remove from a water heater: manually scraping the tank bottom through the drain opening or use of a de-limer chemical will be needed. Below we describe these procedures.
Readers should also see our discussion of mineral clogging of water piping, water heaters, and tankless coils, organized at HOT WATER IMPROVEMENTS. Other gas fired water heater noises are discussed at GAS FLAME & NOISE DEFECTS.
The articles at this website will answer most questions about diagnosing and curing noisy domestic water heaters and about the procedure to remove mineral deposits, lime, water scale, silicates, sulfates, aluminates, or silt and sand from a water heater tank.
If your hot water source is from a tankless coil, or if you suspect that the clogging problem in your building is in the piping itself, see CLOGGED PIPING & Hot Water Flow.
Why do we need to remove lime or scale from a water heater?
At WATER HEATER NOISES we explain how scale in a water heater can reduce the quantity of hot water, reduce water heater life, and cause water heater noises. We explain why it is important to remove the scale from a hot water heater.
The first step in curing water heater noises or poor hot water quantity is to turn off and flush out the water heater.
See Water Heater Flush Procedure for the full article on the detailed procedure for draining and flushing out water heaters to remove scale, dirt, or debris - a first step in cleaning a water heater to increase hot water quantity, temperature, and water heater life, and to stop water heater noises.
Watch out: Safety Warnings: don't tackle this water heater cleanout project on a Sunday night when you can't call a plumber or buy a replacement part. Water heaters, their heating source (oil or gas burner or electricity or solar hot water), and particularly their relief valves include critical safety components.
Do not modify or remove relief valves, chimney connections, draft hoods, etc. as you may create dangerous conditions. Turn off all electrical and or gas power to the water heater and let it cool.
Additional tips on draining a water heater tank can be found at ELECTRIC WATER HEATERS
Draining and flushing the water heater without taking more steps to loosen and remove scale from the water heater bottom may be only marginally effective at stopping water heater noise and removing debris.
If there are thick, hard mineral deposits in the bottom of the hot water tank it may be necessary to take a more aggressive approach:
Safety Warning: never turn on a water heater's heat source before the hot water tank has been re-filled. Otherwise you may damage the heater or create a dangerous condition.
Be sure the water heater pressure and temperature relief valve is properly installed and is the proper type. See RELIEF VALVES - TP VALVES.
How to Use Scale Removers to Clean a Hot Water Tank or to Clean Scale from the Electric Water Heater Electrodes: Chemical Methods
Currently there are products such as UN-Lime® (a professional non-muriatic food-grade phosphoric acid based chemical de-limer intended for removing scale from water heaters, recommended by A.O. Smith, available in 1 gal. or 5 gal. containers) or possibly other acid-based products that can dissolve mineral or lime deposits in a hot water tank.
We suggest suggest dislodging as much water heater tank bottom crud as possible, but also taking a gentle approach so as to avoid even the slightest possibility of damage to the tank.
If you elect to use a deliming chemical in your hot water tank be sure to follow the manufacturer's instructions, including these general steps:
Delimer disposal note: if the delimer is draining into a sump pit be sure to run enough water to cycle the sump pump several times to flush that component out as well - leaving acid and debris from the hot water cleanout in the sump pump could damage it.
Don't Over-Do Acid or Scale Removing Chemicals
In Krappe's 1940 experiments muriatic acid (HCL) and hexametaphosphate solution were discussed for non-mechanical efforts to reduce or dissolve scale in piping, tankless coils, side-arm heaters, water heaters. The author reported that when the zinc coating is removed by acid (older galvanized steel water heating equipment and tanks), rusty water problems were likely.
For this reason, in the 1940's mechanical scale removal was preferred. Modern water heater tanks may be glass lined and less vulnerable to these problems.
Muriatic acid is much less harmful to copper-nickel or copper-silicone surfaces than it is to iron and steel, provided it is not left in metal contact longer than necessary to remove the scale. The message: don't over-do it: more and longer is not necessarily "better".
Krappe described using an acid-resistant pump and tubing connected to fittings to circulate an acid-wash through scale-clogged copper piping back in 1940. Plumbers still use this method today. The apparatus must be designed to let the scale particles and gases escape. Plumbers may simply use an acid-proof pony pump and fittings to cycle the acid wash using a plastic bucket as the receiving sump.
Watch out: this is a dangerous procedure risking acid burns or other hazards. Don't try this procedure if you are not trained and equipped to do so. See Lime Out / Lime Out Extra, lime remover MSDS, a Summit Brands product.
But we have been informed by some plumbers that using acids to clean a tankless coil leave the coil internal surfaces etched and that the result can be faster scale formation than previously.
A detailed procedure for cleaning lime and scale clogged tankless coils, also suitable for some other piping and coil type water heaters is found at Clogged Tankless Coil & Hot Water Flow.
Electric water heaters use one or two electrodes inserted into the bottom and top of the hot water tank. Controlled by a thermostat that senses water temperature inside the hot water tank, the electrodes are turned on to heat water inside the water tank.
On some electric water heater models (Rheem for example) the top heating unit is called the "Booster" and operates only during periods of high demand for hot water. Wiring and controls on the water heater may on some models ensure that only one of the heating elements operates at a time.
Our photo (left) shows a small electric water heater with two heating electrodes - one is located behind each of the dark access panels on the front of the heater.
This water heater maintenance article series continues at Step 3: Water Heater Scale Prevention.
Green link shows where you are in this article series.
Frequently Asked Questions (FAQs)
No FAQs have been posted for this page. Try the search box below or CONTACT US by email if you cannot find the answer you need at InspectApedia.
Questions & answers or comments about scale and lime formation in water heaters.
Check the FAQs just above, try the search box just below, or if you prefer, post a question or comment in the Comments box below and we will respond promptly.
Search the InspectApedia website
HTML Comment Box is loading comments...
Technical Reviewers & References
Related Topics, found near the top of this page suggest articles closely related to this one.